Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
AGE of PLUMBING MATERIALS & FIXTURES
AIR DISCHARGE at FAUCETS, FIXTURES
ANTI SCALD VALVES
ANODES & DIP TUBES on WATER HEATERS
BACKUP PREVENTION, SEPTIC
BACKUP PREVENTION, SEWER LINE
BACKWATER VALVES, SEWER LINE
BATH & KITCHEN DESIGN GUIDE
CHEMICAL CONTAMINANTS in WATER
CHLORINE IN DRINKING WATER
DEBRIS in WATER SUPPLY, Water Heater
DEPTH of SEPTIC TANK
DRAIN & SEWER PIPING
FAUCETS & CONTROLS, KITCHEN & BATH
FAUCETS, OUTDOOR HOSE BIBBS
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOOR DRAIN / TRAP ODORS
FLUSHOMETER VALVES for TOILETS URINALS
GAS PIPING, VALVES, CONTROLS
GALVANIC SCALE & METAL CORROSION
HARD WATER - SOFTENERS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
LEAD POISONING HAZARDS GUIDE
LEAD IN DRINKING WATER, HOW to REDUCE
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MUNICIPAL WATER PRESSURE IMPROVEMENTS
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
ODORS, SEPTIC or SEWER
ODORS SEWER GAS in COLD WEATHER
ODORS, SULPHUR SMELL SOURCES
ANIMAL or URINE ODOR SOURCE DETECTION
PIPING IN BUILDINGS, Clogs Leaks Types
PLUMBING FIXTURES, KITCHEN, BATH
PLUMBING NOISE CONTROL
PLUMBING VENT DEFINITIONS & CODES
PLUMBING VENT DEFECTS & NOISES
PUMPS, WATER REPAIR
RELIEF VALVE LEAKS
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
REPAIR BURST LEAKY PIPES
SEPTIC METHANE GAS
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SHUTOFF VALVE LOCATION, USE
SULPHUR & SEWER GAS SMELL SOURCES
SWEATING (CONDENSATION) on PIPES, TANKS
TOILETS, INSPECT, INSTALL, REPAIR
WATER, WELLS, WATER TANKS: TESTING GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMPS & TANKS
WATER SOFTENERS & CONDITIONERS
WATER SOURCE ALTERNATIVES
WATER SUPPLY & DRAIN PIPING
WATER SHUTOFF VALVE LOCATION, USE
WATER SHUTOFF VALVE, WELL PUMP
WATER TESTS, CONTAMINANTS, TREATMENT
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
Cast iron plumbing drain piping: this article lists our in-depth articles on inspecting, testing, and repairing problems with cast iron building plumbing drain waste vent piping, piping materials, clogged or noisy pipes, and types of pipe hazards or product defects. The articles at this website will answer most questions about water supply & drain piping of all materials and types.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Making New Drain Connections to Old Cast Iron Drain Piping
Our photograph of cast iron drain piping (below left) demonstrates two methods by which connections have been made to newer copper drain lines. At upper left a black plastic hub fitting has been used to connect the 4" copper drain to the cast iron drain line.
At center-right in the left-hand photo a questionable clamp-on type fitting has been used for the same purpose, including a makeshift clamp using a block of wood to accommodate use of the wrong-sized clamp around the cast iron drain. Stains on the upper section of piping indicate that this drain system has been leaking.
Our photograph at below-right shows three clamp-on connectors joining cast iron and plastic drains to the cast iron sewer line.
Cast Iron Drain Piping Leak & Odor Locations, Causes, Diagnosis
Our photograph (below left) shows an odd double-hub connection on a vertical section of cast iron drain piping in a 1935-built home in poughkeepsie, NY. You can see by the rust stains that this cast iron pipe joint has been leaking for some time, that the concrete "repair" action was not fully effective, and that the basement is exposed to unsanitary conditions due to sewage leakage.
Our second cast iron drain leak photograph (below right) shows a different type of drain pipe leak: sewer gases. This fitting and collection of galvanized iron elbows and nipples should be removed and the opening in the vertical cast iron drain plugged to stop potentially dangerous sewer gases from entering the building. We suspect that this drain was once used to receive water from a basement dehumidifier or water softener, but it is no longer in use. The dry "trap" formed at the bottom of the piping "U" no longer serves to keep sewer gases out of the building.
Watch out: sewer gases may be both unsanitary and also risk of a very serious methane gas explosion. See SEWER GAS ODORS.
Several types of leaks occur in Cast Iron Piping:
Cast Iron Drain Pipe Leak & Repair Case - Odors Lead to Discovery of Under-Floor Drain Leaks
Often on city lots that are flat and poorly drained, builders or building owners were pressed to decide how to get rid of rainwater spilling off of building roofs and through the gutter and downspout system.
The best approach is to route these drains to a nearby city storm drain, pumping if necessary but best by gravity. This avoids overloading the city sewer system during periods of heavy rainfall. Our photograph (left) shows a New York City storm drain overflow station (officially, a: New York State Wet Weather Discharge Point) where excess drainage is dumped into the Hudson River when more water or wastewater enters the city sewer system than can be handled. The green sign atop this drain warns
If you see a discharge during dry weather, please call 311 - DEP (Department of Environmental Protection).
Overloading a city's sewer often means that raw sewage is simply overflowed or dumped into local rivers or streams.
But It was common in previous generations for builders to rout (usually cast iron) drain pipes from ground-level outside of a building into the building, under the basement floor slab, and out to the municipal sewer system. These drains were used to receive roof gutter drainage and dispose of it into the city sewers.
Our photo (left) shows an in-basement cast iron drain line that originally received outside gutter/downspout drain water. At the time of our inspection that system had been changed and downspouts were routed to above-ground drains (unfortunately still too close to the building to assure a dry basement).
A problem with the in-building, under-floor piping disposal of roof runoff, besides overloading the city sewers in wet weather, is that eventually the under-floor drain may become clogged, perhaps with leaves washing into the drain from the building's gutters. The best result of that problem is that the drain stops draining and gutters spill outdoors along the foundation, perhaps leading to basement water entry, rot, mold, and insect damage.
Still more troubling, a blocked under-floor drain in a building left with no heat sometimes led to frozen drain pipes and burst, heaved piping and floor damage in the building, followed by an in-building flood when freezing weather changed to a thaw.
If you have roof gutters connected to drains that enter the building and are routed to the sewers, (a step still permitted and even required in a few communities), reconnecting the drains from outside ground-level to a nearby storm drain may be a better approach.
Tracking Down Leaky Cast Iron Drain Pipes Under a Floor Slab that Sent Sewer Gases into Transite (Asbestos Cement) HVAC Ducts
Details of this sewer gas odor case, cast iron drain leak, and repair are at CAST IRON DRAIN LEAK, ODOR, REPAIR. Excerpts are below.
A reader (Conrad) provided us with the photographs and case history of the successful track-down of sewer gas odors in a building (SEWER GAS ODORS). The case began with a complaint of sewer gas odors in the building's heating duct work system.
Details about the case illustrated just below, including more pictures and notes on how the building owner tracked the sewer smell to the basement floor slab (and transite heating ducts in the slab) can be read at CAST IRON DRAIN LEAK, ODOR, REPAIR.
SLAB DUCTWORK - catalogs the functional and environmental problems found when HVAC air ducts are routed in or below floor slabs.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about cast iron drain pipes in buildings.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.