Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
AGE of PLUMBING MATERIALS & FIXTURES
AIR DISCHARGE at FAUCETS, FIXTURES
BACKUP PREVENTION, SEWER LINE
BLOCKED DRAIN REPAIR METHODS
CARBON MONOXIDE - CO
CHECK VALVES, WATER SUPPLY
CHLORINE IN SEPTIC WASTEWATER
CLEANOUTS, PLUMBING DRAIN
CLOGGED DRAIN DIAGNOSIS & REPAIR
CLOGGED SUPPLY PIPES, DIAGNOSIS
CLOGGED SUPPLY PIPES, REPAIR
CLOGGED SUPPLY PIPES, HOT WATER
CONDENSATION or SWEATING PIPES, TANKS
CROSS CONNECTIONS, PLUMBING
DEBRIS in WATER SUPPLY, Water Heater
DEPTH of DRAIN & SEWER PIPES
DEPTH of SEPTIC TANK
DRAIN & SEWER PIPING
DRAIN LINE DEPTH
DRAIN a WATER HEATER TANK
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOODED HEATING EQUIPMENT REPAIR
FLOODED SEPTIC SYSTEMS, REPAIR
FLOODED WATER HEATER REPAIR
FLOOR DRAIN / TRAP ODORS
FLUSHOMETER VALVES for TOILETS URINALS
GAS PIPING, VALVES, CONTROLS
GALVANIC SCALE & METAL CORROSION
GALVANIZED STEEL PIPING
HARD WATER - SOFTENERS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
LEAD POISONING HAZARDS GUIDE
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MUNICIPAL WATER PRESSURE IMPROVEMENTS
NOISE CONTROL for PLUMBING
NOISE, PLUMBING DRAIN DIAGNOSIS
NOISE, PLUMBING DRAIN REPAIR
NOISE, PLUMBING CHECKLIST
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
ODORS, SEPTIC or SEWER
ODORS SEWER GAS in COLD WEATHER
ODORS, SULPHUR SMELL SOURCES
OUTHOUSES & LATRINES
PIPING IN buildings, Clogs Leaks Types
PLUMBING FIXTURES, KITCHEN, BATH
PLUMBING NOISE CONTROL
PLUMBING VENT DEFINITIONS & CODES
PLUMBING VENT DEFECTS & NOISES
PUMPS, WATER REPAIR
REPAIR BURST LEAKY PIPES
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEWAGE BACKUP, WHAT TO DO
SEWAGE BACKUP TEST & CLEANUP
SEWAGE BACKUP PREVENTION
SEWAGE BACKUP TEST & CLEANUP
SEWAGE & SEPTIC CONTAMINANTS
SEWAGE CONTAMINATION in buildings
SEWAGE CONTAMINANTS in FRUIT / VEGETABLES
SEWAGE EJECTOR / GRINDER PUMPS
SEWAGE NITROGEN CONTAMINANTS
SEWAGE PATHOGENS in SEPTIC SLUDGE
SEWAGE PUMP CLOG DAMAGE
SEWER BACKUP PREVENTION
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SHUTOFF VALVE LOCATION, USE
SULPHUR & SEWER GAS SMELL SOURCES
SUMP PUMPS GUIDE
SWEATING (CONDENSATION) on PIPES, TANKS
TOILETS, INSPECT, INSTALL, REPAIR
TOILET ALTERNATIVES, WATERLESS
TOILET FLUSHOMETER VALVES
TOILET INSTALLATION PROCEDURE
TOILET OVERFLOW EMERGENCY
TOILET PLUGS, SEWER BACKUP
TOILET REPAIR GUIDE
Toilet Types, Flush Methods
TOILETS, DON'T FLUSH LIST
TRAPS on PLUMBING FIXTURES
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PIPES, Clogs Leaks Types
WATER PRESSURE & FLOW MEASUREMENT
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS\
WATER QUALITY TESTS, CONTAMINANTS, TREATMENT
WATER QUANTITY IMPROVEMENT
WATER SHUTOFF VALVE LOCATION, USE
WATER SHUTOFF VALVE, WELL PUMP
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELL PUMP PRIMING PROCEDURE
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
Building drain cleanout access ports: how to locate & use plumbing drain cleanouts: this article describes cleanouts used to access and clear clogged building drain pipes. Plumbing cleanouts are access points from which it is easiest to attempt to clear a slow or clogged drain line.
If you need to diagnose and fix a clogged drain pipe, see CLOGGED DRAIN DIAGNOSIS & REPAIR. Our page top photo shows a main building drain cleanout at the location where it is most commonly found: where the building drain exits the structure.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Indoor Building Drain Cleanouts
As we cited at DRAIN & SEWER PIPING, Plumbing codes define a building drain as "that part of the lowest piping of a building drainage system that receives the discharge from soil, waste, and other drainage pipes inside the walls [or upper floors] of the building and conveys it to the building sewer [or septic system] beginning two feet (0.6m) outside the building wall."
This piping and its horizontal branches are required to have cleanouts, however no cleanout is required for any pipe or piping above the first floor of the building.
Where do I Find the Plumbing Drain Cleanout for Upper Building Floors?
If you need to run a plumbing snake through drain piping through pipes above the first floor of the building you will most likely need to open a sink trap, shower drain, or remove a toilet to most easily access the larger-diameter drain piping on upper floors.
But most often plumbing drains clog at bends, elbows, tees, and in the longer horizontal runs often found on the first floor or between the building itself and the sewer line or septic system.
A Photo Guide to Plumbing Cleanouts & Cleanout Problems
Our plumbing drain cleanout photo (left) shows a sewer line cleanout under and building exit piping under construction at a New York Home. The image illustrates a new plumbing drain cleanout access port being installed in a home.
The in-building drains (not visible here) were 4-inch ABS pipe. The exterior sewer connection pipe was six-inch pipe. Photo courtesy Galow Homes.
When installing the plumbing drain cleanout the plumber continued the six-inch piping up into the building through the drain cleanout fitting, providing an easier-to-use wider drain cleanout opening.
The extra cost of continuing 6-inch piping up to this location was trivial and makes drain servicing much easier. At the left side of the photo the drain piping is adapted down to the 4-inch in-building drain size.
Because of the larger diameter cleanout TEE installed in this case, the plumber installed a 90 degree cleanout tee. In most of our other plumbing cleanout port photographs you'll see that the cleanout access is installed with an angled fitting to assist the plumber in routing a plumbing snake in the direction most likely to be needed to clear a slow or blocked plumbing drain.
Because this plumbing drain exit point was located in the home's garage, local building codes required that we enclose the plastic piping in a chase covered with fire-rated drywall.
Even before the fire barrier drywall, the inspector also required that we use fire-block foam insulation to seal the pipe penetrations in walls, ceilings, and floors.
And because the fire-block foam could not itself be left exposed, where that material was used at other penetrations through the fire-rated drywall, those penetrations were sealed with fire-caulk.
Finally, the builder (Galow Homes) provided a metal plumbing access cover so that it would still be possible to access the plumbing cleanout if necessary.
Outdoor Cleanout Port for Sewer or Septic Line Piping
Often an outdoor cleanout is provided to permit snaking and clearing the building sewer line connection (circled area in photo at left). In this home which is slab-on-grade construction, there was no indoor provision for a building drain cleanout access in this wing of the home; the builder constructed this plumbing cleanout access just outside of a bathroom wall. Photo courtesy Galow Homes.
Building Plumbing Drain Cleanout Problems & Defects
Using the building drain cleanout to add a washing machine or sump pump drain connection is an overwhelming temptation because of the convenience (photo at left) but this installation gave no thought to the future need to inspect or clear a blocked drain line.
The result will be extra trouble and cost when drain de-clogging is needed.
When the finished building wall in this basement was removed as part of a mold remediation project we discovered that a house trap was leaky - it has been replaced in this photograph.
And because the original house trap and cleanout access had been buried behind a finished wall the cleanout was not readily accessible, nor was its location even known to the current homeowner.
Our two building drain cleanout access photos (below) illustrate a surprisingly common and both dangerous and unsanitary condition: the building drain cleanout is left open, risking entry of sewage and sewer gases into the building.
At below left our photo illustrates a connection of copper drain to the cast iron building drain in a basement. You will notice that the copper drain line (circled at upper left) includes a cleanout access port.
Unfortunately the copper connection in the lower right of the photograph (arrow) is improper, unreliable, and perhaps unsanitary.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
(July 12, 2012) Chris said:
the kitchen drain pipe is blocked .ive removed and cleaned the inside pipes but the main outlet drain pipe is blocked
You need to find the main building drain cleanout and check that the drain is clear from there, or clear it.
(Dec 29, 2012) Stevo said:
I am making a bathroom in my basement, can I hook up the toilet to the existing cleanup pipe?
Steveo. Yes if local codes permit. If the toilet is higher than the existing drain line so that it can drain to it by gravity, you drain directoy to the main line. If the main drain is above the toilet base you'd need either a powered up-flush toilet or more likely a sewage ejector pump that receives waste from the toilet and, using a small float-operated grinder pump, forces wastewater up to the main drain.
(Jan 15, 2013) salmontimsalmontim@yahoo. said:
I have a house built in the early 1950s with a dry well to handle the kitchen sink grey water. the piping is black iron and their is a large iron trap in the basement..(9" dia cylinder, 14" hight) the drain is clogged and the top to the trap can not be opened... any suggestions?
Salmon, a plumbe will either open the drain cap for you or in the worst case will cut out and remove and then replace the main trap. You need to be able to access this port for drain cleaning. Sometimes we can defer that trouble and cost by finding a nearby drain cleanout access that can be opened and used.
(Feb 26, 2014) Anonymous said:
How often should a 4in building drain pipe be rodeo
Anon I think you are asking how often a drain line should be routed out? When it's blocked is the answer. But if you find that clearing a drain does not produce a lasting repair I suspect other problems such as root invasion or improper slope, or scale and corrosion build-up.
Question: what types of plumbing cleanouts are used in homes & does greywater flow into the sewer line?
(1 days ago) Debs said:
My house is over 40 years old and we had roots growing into the sewer line. Plumber could not locate the sewer cleanout (he went under the house and around the house and we only could locate one cleanout, which was next to the kitchen.) so he installed one which of course is connected to the sewer pipe which is fine.
My neighbor stated there was no reason to do this since all grey water goes thru the sewer line. Can you explain to me what types of cleanouts are used in homes? Also, does the grey water from the kitchen flow into the sewer line as well?
Debs I cannot make sense whatsoever out of your neighbor's comment that drain cleanouts are unnecessary.
[Click to enlarge any image]
What is a plumbing drain cleanout and what's it for?
A plumbing drain is an opening in a drain line, typically a Wye, that is covered with a removable cap to permit drain cleaning or un-clogging.
Drains serving both blackwater (toilets) and graywater (laundry, dishwasher, kitchen sink) can clog. Building plumbing drain lines can clog for a variety of reasons such as poor slope, accumulation of solids, root invasion, items flushed down toilets, corrosion in galvanized iron, soap sludge and scum, and other blocking materials. Details are at CLOGGED DRAIN DIAGNOSIS & REPAIR.
The plumbing drain cleanout gives access to various drain sections to permit use of an auger or drain cleaning tool. Both hand operated and power-operated drain cleaning tools are used as well as other drain cleaning methods (compressed air, chemicals, and even drain line replacement). .
Where are plumbing drains located?
Typically there is at least one main drain cleanout where a sewer line leaves a building - the main drain cleanout.
In the photo guide above, at A Photo Guide to Plumbing Cleanouts & Cleanout Problems you can see a main cleanout installed where a building drain leaves the structure. Outdoors there may be additional drain line access covers to extend the reach of drain cleaning tools.
A thoughtful builder (or plumbing inspector) may install (or require the installation of) drain cleanouts at areas that woudl be hard to access or get past during a building drain cleaning operation from a sink or toilet.
Additional drain line cleanouts, if present, may be located in various locations based on convenience and need. For example where there is a long drain run cleanouts maybe installed at intervals - since handling a very long plumbing snake or drain auger is more difficult than using a shorter one.
Plumbing drain cleanouts are also installed at changes of direction and of course in different sections of drain lines before intersections.
Other access points may be used to try to clear a drain where there is no cleanout, such as by
Where greywater flows in a building depends on its drain design. In most buildings the greywater joins blackwater enroute to a public sewer or privat septic system. At properties where septic drainfield capacity is limited or there has been a history of failures, often graywater is routed to a separate drywell to reduce the load on the septic system.
Other reasons that grey water may be routed to a separate drain system include:
Convenience: if a kitchen or laundry are located where connecting their drain to the main building drain line is difficult or costly on occasion we see the contractor or plumber install a local drywall close to the point of use of those fixtures.
See GREYWATER SYSTEMS for more about graywater systems.
Questions & answers or comments about plumbing drain cleanouts: where are they required, how are they used to de-clog or inspect building drain systems?.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References