Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
ANTIFREEZE for BOILERS
BACKUP PREVENTION, SEWER LINE
BLOCKED DRAIN REPAIR METHODS
CLEANOUTS, PLUMBING DRAIN
CLOGGED DRAIN DIAGNOSIS & REPAIR
FREEZE-PROOF A BUILDING
FROST HEAVES, FOUNDATION, SLAB
HEAT TAPE USAGE GUIDE
HOT WATER HEATERS
INSULATION INSPECTION & IMPROVEMENT
NO HEAT - BOILER
NO HEAT - FURNACE
ODORS & SMELLS DIAGNOSIS & CURE
OIL FIRED WATER HEATERS
PIPING IN buildings, Clogs Leaks Types
PLUMBING FIXTURES, KITCHEN, BATH
PUMPS, PONY PUMPS
RELIEF VALVE LEAKS
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SHUTOFF VALVE LOCATION, USE
SUMP PUMPS GUIDE
TRAPS on PLUMBING FIXTURES
WATER HEATER PROBLEM DIAGNOSIS
WATER HEATER PROPERTIES
WATER, WELLS, WATER TANKS: TESTING GUIDE
WATER SHUTOFF VALVE LOCATION, USE
WATER SHUTOFF VALVE, WELL PUMP
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
How & where do pipes burst when they freeze? This article describes the different ways in which plumbing pipes freeze & burst & about the pipe burst variations by different piping materials. We illustrate several burst pipe patterns for copper water supply piping and include photographs of the different failure modes for plastic pipes & for galvanized iron water pipes. In a second section we illustrate breakage patterns when plastic, galvanized iron, or cast iron drain piping freezes. Our page top photo illustrates that hot water heating pipes in a building can freeze and burst or separate when heat fails or is turned too low.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Our photo (left) provides a closeup showing one of several patterns in which a copper water pipe will swell and burst due to freezing.
In this common copper pipe freeze and burst pattern pressure from expanding ice in the copper line is localized to a specific point, sometimes further obstructed by a pipe elbow or valve.
Pressure from expanding ice forms a round bulge in the copper that bursts in the pattern shown in our photos.
Learning to recognize the typical locations and patterns in which building pipes from any system (water supply, drains, hot water heating system) burst can help diagnose previous troubles as well as prevent future freeze-ups, burst piping, and costly mold or water damage cleanup projects.
Our pipe-freeze damage photo at left illustrates a different way in which water supply piping can burst or leak due to freezing. In this case the force of expanding ice in the water pipe did not cause the copper pipe to swell nor crack.
Rather the ice pressure along the length of the pipe or between the solder joint and a nearby obstruction formed by an elbow or valve caused horizontal movement that separated the sweat fitting, opening the pipe ends.
Watch out: the copper pipe bulges, splits, separations and damage describe here can occur on hot water heating system piping too (see our page top photograph) if the heat is left off in a building. You can avoid frozen heating pipes in a shut-down building by draining the heating system when it is shut down (WINTERIZE - HEAT OFF PROCEDURE), or by providing a proper antifreeze mixture in the boiler and heat piping. (ANTIFREEZE for BOILERS).
At AIR BLEEDER VALVES we describe opening air bleeders to remove trapped air in heating piping; but that procedure can also assist in deliberate drain-downs of heating system piping as well.
The pipe frost damage shown in this photo illustrates another pipe damage pattern: splitting. The pressure of ice expanding in a length of piping can cause the pipe to expand and split along the length of the pipe.
Depending on how pipe was manufactured as well as on the location and distribution of expanding ice in the length of pipe, some pipes may tend to split when freezing while others will bulge and burst and still others may leak by separation at solder joints or connections.
Watch out: when turning water back on in a building that was left with heat off, regardless of whether or not pipes were drained, be alert for a surprise spray of water from a burst water supply or heating pipe that you did not see at initial inspection as part of your de-winterizing procedure. (DE-WINTERIZE a BUILDING).
Never just turn heat and water back on and leave the building. Make a complete visual inspection for obvious leaks, listen for leaks in wall, ceiling, or floor cavities, and even if no leaks are found, inspect the building again in 24-hours or less to check for small leaks that are slow to show-up.
Leaving a building wet for more than 24-48 hours risks not only costly water damage but a still more costly mold remediation clean-up job.
Galvanized iron water supply pipe can also burst from freezing, and may split at seams depending on how the pipe was manufactured.
Galvanized iron water supply (or drains) are more likely to burst by splitting or fracturing if pipe sections are corroded from an external cause such as corrosive water or by contact with materials or surfaces that increase the pipe corrosion rate.
Our photo (above-left) illustrates a galvanized iron pipe failure (and replacement) at a spa in Lourdes, Mexico.
Drain Pipe Freeze & Burst Patterns Organized by Drain Pipe Material
Cast iron drain piping freeze damage
Cast iron drain pipes damaged by freezing often fracture as our PVC example or pipes may split at cast-joints.
The cast iron drain in our photo was located beneath a basement floor - and failed by cracking as shown in the image.
Watch out: the crack in a cast iron pipe that causes the drain to leak may be on a side of the drain that you cannot see, such as its under-side along the floor, or a pipe side against a building wall.
That's why above we warned of the importance of a careful inspection when a building is being de-winterized.
Plastic ABS & PVC drain pipe freeze or frost damage
The photo at left shows remains of a PVC drain line that froze and burst in an un-heated crawl space.
This burst pattern is most typical of above-ground and some below-ground PVC drain pipe freeze burst damage - the material fractures.
ABS plastic piping also fails by cracking, discussed as a product failure independent of freezing, at PLASTIC PIPING
Watch out: burst drain piping that spills sewage in a building is going to require not just mopping up but disinfecting or sanitizing of the affected areas. Even dust from areas where there was a previously inadequately cleaned sewage spill can carry pathogens into the building air and into other building areas from that of the original sewer backup or burst pipe spill.
The most common cause of drain line freeze-bursting is the combination of
The cast iron drain (now removed at this location) split along a seam when it froze; often cast iron piping will break into fragments if the piping is filled with water and is frozen solid.
Frozen drain piping prevention, burst building drains: how to prevent freezing drain piping, watching for leaks and slow drips into drain systems are discussed at Drain Pipe Protection.
Galvanized Iron drain pipe freeze damage
Galvanized iron pipe can also burst from freezing, and may split at seams depending on how the pipe was manufactured.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Questions & answers or comments about about the different ways in which plumbing pipes freeze & burst & about the pipe burst variations by different piping materials.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.