Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
AGE of PLUMBING MATERIALS & FIXTURES
AIR DISCHARGE at FAUCETS, FIXTURES
ANTI SCALD VALVES
ANODES & DIP TUBES on WATER HEATERS
BACKUP PREVENTION, SEPTIC
BACKUP PREVENTION, SEWER LINE
BACKWATER VALVES, SEWER LINE
BATH & KITCHEN DESIGN GUIDE
CHEMICAL CONTAMINANTS in WATER
CHLORINE IN DRINKING WATER
DEBRIS in WATER SUPPLY, Water Heater
DEPTH of SEPTIC TANK
DRAIN & SEWER PIPING
FAUCETS & CONTROLS, KITCHEN & BATH
FAUCETS, OUTDOOR HOSE BIBBS
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOOR DRAIN / TRAP ODORS
FLUSHOMETER VALVES for TOILETS URINALS
GAS PIPING, VALVES, CONTROLS
GALVANIC SCALE & METAL CORROSION
HARD WATER - SOFTENERS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
LEAD POISONING HAZARDS GUIDE
LEAD IN DRINKING WATER, HOW to REDUCE
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MUNICIPAL WATER PRESSURE IMPROVEMENTS
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
ODORS, SEPTIC or SEWER
ODORS SEWER GAS in COLD WEATHER
ODORS, SULPHUR SMELL SOURCES
ODORS, URINE REMOVAL
PIPING IN BUILDINGS, Clogs Leaks Types
PLUMBING FIXTURES, KITCHEN, BATH
PLUMBING NOISE CONTROL
PLUMBING VENT DEFINITIONS & CODES
PLUMBING VENT DEFECTS & NOISES
PUMPS, WATER REPAIR
RELIEF VALVE LEAKS
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
REPAIR BURST LEAKY PIPES
SEPTIC METHANE GAS
SHUTOFF VALVE LOCATION, USE
SULPHUR & SEWER GAS SMELL SOURCES
SWEATING (CONDENSATION) on PIPES, TANKS
TOILETS, INSPECT, INSTALL, REPAIR
WATER, WELLS, WATER TANKS: TESTING GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMPS & TANKS
WATER SOFTENERS & CONDITIONERS
WATER SOURCE ALTERNATIVES
WATER SUPPLY & DRAIN PIPING
WATER SHUTOFF VALVE LOCATION, USE
WATER SHUTOFF VALVE, WELL PUMP
WATER TESTS, CONTAMINANTS, TREATMENT
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
Water supply & drain piping: This article defines and describes different types of building supply and drain piping with an alphabetical list of piping materials and properties. For each type of building piping material, in addition to giving its description and properties and use, we include special concerns or possible defects to watch-out for.
The articles at this website will answer most questions about water supply & drain piping, wells, & water tanks as well as many other building plumbing system inspection or defect topics. We link to in-depth articles on inspecting, testing, and repairing problems with building plumbing: water supply and drain waste vent piping, plumbing traps, piping materials, clogged or noisy pipes, and types of pipe hazards or product defects. Other types of building piping systems are discussed at GAS PIPING, VALVES, CONTROLS and at OIL TANK PIPING & PIPING DEFECTS.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
See CAST IRON DRAIN PIPING for details. Excerpts are below.
Cast iron piping used for in-building drain piping as well as sewer lines is also illustrated at How to Locate the Main Building Drain, and at How to Use a Power Snake on Building Drains you can see a common splice-in of ABS plastic drain piping into an existing cast iron sewer line.
See COPPER PIPING in buildings for details. Excerpts are below.
See GALVANIZED STEEL WATER PIPING for details. Excerpts are below.
Galvanized steel is not commonly used as a service pipe, although galvanized steel fittings may be found at the point of entry into the house. Where galvanized service piping is used, it is typically at least 1 1/4-inch diameter. The word galvanized means zinc-coated. The coating helps prevent the steel from rusting.
Galvanized steel piping was common until roughly 1950. This piping typically lasts 40 to 60 years. Some lower-quality pipes do not last as long and there are some oversized pipes still in use after 60 years. Where it is found today in single-family homes, it is usually near the end of its life.
Life expectancy of galvanized steel piping: Galvanized steel supply pipes are typically 1/2-inch diameter. The connections are threaded. When the pipe corrodes, the rust accumulation inside the pipe chokes down the diameter of the pipe, resulting in poor water pressure.
Rust also attacks the pipe walls, making the walls thinner. Eventually, the pipe will rust through, usually at the joints first, resulting in leakage.
- Home Reference Book, used with permission.
See GALVANIZED STEEL WATER PIPING for details. Excerpts are below.
Our photographs (below) show galvanized drain piping in use in buildings. At below left, the cleanout in a galvanized drain line has been lost, plugged with who-knows-what, and is an odor and leak source. At below-right, the rope trying to secure the galvanized drain line to the cast iron sewer piping confirm a history of leak troubles and improper plumbing connections.
See our detailed articles about lead plumbing pipes in buildings at
Portions of the following summary are from Carson Dunlop Associates' Home Reference Book, used with permission:
Lead piping was used between the street main and the house up until the 1950s. A good deal of lead supply line is still in use, and the health authorities indicate that as long as it is used regularly, there is no difficulty with it. If the water has not been run for some time, many recommend that the water be flowed for several minutes before using it.
Our photographs show a lead water entry main or service pipe (below-left) and lead plumbing drain piping (below-right).
The life expectancy of lead water supply piping is indefinite in some soils and in more corrosive soils we have plumbers' opinions that the service life of buried lead water supply piping is 40 to 50 years. See LEAD WATER PIPES and LEAD in WATER, ACTION LEVEL & REMEDIES for details. Also see AGE of PLUMBING MATERIALS & FIXTURES.
Orangeburg pipes, named not for their color but for the town where the Fibre Conduit Company, a major pipe manufacturer was located, were used outside buildings to connect the building drain to septic systems or in some areas to sewer pipes.
Orangeburg pipes are black, and somewhat fragile bituminous-coated fiber pipes.
OPINION: think Orangeburg pipe? think "tar impregnated cardboard". Inexpensive, widely used. Orangeburg piping was used in both un-perforated form as septic distribution piping and more widely in perforated form as effluent distribution piping in septic drainfields and as buried downspout drain lines.
As we explain at AGE of PLUMBING MATERIALS & FIXTURES, Orangeburg drain & septic field piping, most widely used in drain piping and septic fields, was made of ground wood fibers bound with an adhesive mastic (coal tar), typically looking like black"tarred" piping. Orangeburg piping was first used in Boston in 1865.
Despite it's name, "Orangeburg pipe" is not orange in color and it never was, though if you want to see some orange-colored sewer piping see our description of Terra Cotta (clay) pipes below in this article. The name Orangeburg pipe comes from the main producer of this product, the Fibre Conduit Co., in Orangeburg, New York. After 1948 the company changed its name to Orangeburg Manufacturing. Black coal-tar impregnated fiber piping was widely used in North American from 1950 to 1970.
Orangeburg drain piping and sewer piping was not made just by Fiber Conduit. Other manufacturers included American Piping Co., J.M. Fiber Conduit, Bermico (Brown Manufacturing), and American Manufacturing
We still come across Orangeburg pipe when excavating old septic drainfields and on occasion when inspecting an older home, say before 1970, you may see the top of a section of Orangeburg pipe peeking up above ground as a connection for a roof gutter downspout.
In our Orangeburg pipe downspout drain photo above we were pointing out (the pen) that perforated pipe was used as a buried drain right next to the building - inviting basement water entry even if the drain is not yet clogged. And figure, if you see a buried downspout drain using a material not commonly installed for 40 years, that the drain itself may be blocked or collapsed by now. Now think "Orangeburg pipe septic drainfield??"
Terra cotta pipes are clay pipe that was used for external sewer (or septic system) connection in North America from about 1900 to 1940.
Terra cotta pipe is often deep red to orange in color, round with hubs to facilitate pipe section connections. (Photo, above left).
In smaller sizes terra cotta may be hexagonal in external shape (photo above right) though round in its interior profile. Joints in terra cotta piping were made using cement to surround the piping.
The material was both durable (it does not corrode or rot) but fragile, easily broken by heavy traffic above or by improper bedding in the trench if exposed to heavy rocks.
Clay drainfield piping or "drain tiles" is also shown in fragments in our article on sewer line replacement, at Determining Need for Replacement. We also provide this photo of another type of octagonal clay sewer and septic piping that was often used in drainfields as disjointed sections.
Frequently Asked Questions (FAQs) About building Supply or Drain Piping: installation, inspection, trouibleshooting, repair
Question: what's the right type of copper pipe to use at my urinals?
Inspector is challenging me about the type of copper pipe installed for waste pipe on my urinals. I installed d.w.v. Copper tube and he says type m is minimum. What do you say I cannot find anything in ontario plumbing code 2006. - Karac Rushton - 6/29/2012
Reply: 2007 Ontario Plumbing code permits K & L copper; M above ground; DWV above ground but not buried.
Karac, the 2007 Ontario Plumbing code is available online at opseu560[dot]org/BuildingCode-2007[dot]pdf
184.108.40.206. Conformance to Standards
Questions & answers or comments about installing, inspecting, & repairing building piping systems..
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.