Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
AGE of PLUMBING MATERIALS & FIXTURES
AIR DISCHARGE at FAUCETS, FIXTURES
ANTI SCALD VALVES
ANODES & DIP TUBES on WATER HEATERS
BACKUP PREVENTION, SEPTIC
BACKUP PREVENTION, SEWER LINE
BACKWATER VALVES, SEWER LINE
BATH & KITCHEN DESIGN GUIDE
CHEMICAL CONTAMINANTS in WATER
CHLORINE IN DRINKING WATER
DEBRIS in WATER SUPPLY, Water Heater
DEPTH of SEPTIC TANK
DRAIN & SEWER PIPING
FAUCETS & CONTROLS, KITCHEN & BATH
FAUCETS, OUTDOOR HOSE BIBBS
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOOR DRAIN / TRAP ODORS
FLUSHOMETER VALVES for TOILETS URINALS
GAS PIPING, VALVES, CONTROLS
GALVANIC SCALE & METAL CORROSION
HARD WATER - SOFTENERS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
LEAD POISONING HAZARDS GUIDE
LEAD IN DRINKING WATER, HOW to REDUCE
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MUNICIPAL WATER PRESSURE IMPROVEMENTS
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
ODORS, SEPTIC or SEWER
ODORS SEWER GAS in COLD WEATHER
ODORS, SULPHUR SMELL SOURCES
ANIMAL or URINE ODOR SOURCE DETECTION
PIPING IN BUILDINGS, Clogs Leaks Types
PLUMBING FIXTURES, KITCHEN, BATH
PLUMBING NOISE CONTROL
PLUMBING VENT DEFINITIONS & CODES
PLUMBING VENT DEFECTS & NOISES
PUMPS, WATER REPAIR
RELIEF VALVE LEAKS
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
REPAIR BURST LEAKY PIPES
SEPTIC METHANE GAS
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SHUTOFF VALVE LOCATION, USE
SULPHUR & SEWER GAS SMELL SOURCES
SWEATING (CONDENSATION) on PIPES, TANKS
TOILETS, INSPECT, INSTALL, REPAIR
WATER, WELLS, WATER TANKS: TESTING GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMPS & TANKS
WATER SOFTENERS & CONDITIONERS
WATER SOURCE ALTERNATIVES
WATER SUPPLY & DRAIN PIPING
WATER SHUTOFF VALVE LOCATION, USE
WATER SHUTOFF VALVE, WELL PUMP
WATER TESTS, CONTAMINANTS, TREATMENT
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
Plastic plumbing pipes: beginning here, this article series describes the properties of all types of plastic piping and tubing used in buildings for water supply, drainage, or gas or oil fuels, including ABS, CPVC, PB, PEX, PVC. We include information about failures and problems with some generations of plastic pipes (ABS, polybutylene) and we describe good building practice installation details where plastic piping is being installed. Included is information about ABS, PB, Polybutylene, PEX, PVC polyvinyl chloride and other plastic piping materials. We discuss problems and class action claims for plastic pipe product failures including both the piping itself and its connectors or fittings for each of these materials where trouble has been found. We also discuss ongoing or previous health & safety concerns raised for some plastic piping products. The articles at this website will answer most questions about plastic building water supply and building drain piping products, failures, and claims as well as many other building plumbing system inspection or defect topics.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
PEX Tubing Connectors: Types, Tools, Requirements
Watch out: a variety of patented PEX tubing push-fit and clamp connecting fittings (at least six types) and connector crimping tools are on the market. You may not obtain a proper and secure PEX connection if you mix tubing connector fittings and crimping tools improperly. We recommend choosing a specific connector type and crimping tool and using it consistently at a given plumbing installation.
Examples & Photographs of the various types of PEX fittings and the special tools used include:
Standards, Listings and Approvals for PEX Plumbing Systems
The following standards and building codes list at least some elements of PEX plumbing systems.
In March 2012 the U.S. District Court for the District of Minnesota court-ordered homeowner notification program was scheduled to begin. People who own or previously owned a building where Plumb-PEX plumbing components were installed are notified of a proposed class action settlement involving Radiant Technology, Inc. and Uponor, Inc who sold Plumb-PEX insert fittings and stainless steel PEX tubing clamps. Those components may have leaked, or may leak, causing building damage. The defendants denied all claims of the lawsuit but have agreed to settle the case. 
Plumb-PEX Settlement Details
RTI Plumb-PEX Plumbing System fittings and components including
Plumb-PEX Settlement Provisions
The settlement reimburses for property damage caused by a qualifying leak in the Plumb-PEX installation, and it provides for possible repair or replacement of the RTI Plumb-PEX installation in structures suffering two or more "qualifying" leaks.
Watch out: If you are eligible for a claim under the Plumb-PEX settlement, you must file your claim within 18 months of the notification date of 22 March 2012
Also see PEX vs. Copper Water Supply Piping - health & other questions found below in the FAQs section of this article.
PB Pipe: Polybutylene Plumbing Plastic Pipe Use, Installation Specs, Failures, Leaks, Claims, Settlements
Complete details are at PB Polybutylene (PB) Pipes. Excerpts are below.
Thumbnail: Polybutylene (Polybutylene) Plumbing (plastic pipes): gray plastic water supply piping cracked, leaked, and resulted in a class action and settlement.
PB or Polybutylene pipe material (photo at left, center horizontal piping) is gray plastic water supply piping that racked, leaked, and its early use resulted in a class action and settlement.
In 1995 a $950 million class action settlement, Cox v. Shell Oil Company, provided relief for damage due to leaks in Polybutylene plumbing (PB Plumbing) within certain age constraints. Periodic notices were to be provided to homeowners over a 12-year period (ending ca. 2007) as follows:
Owners who purchased a house, mobile home, or other structure in the United States after August 21, 1995, provided that the structure contained polybutylene piping with plastic or metal insert fittings when they purchased it, are included in the class. These individuals may have been entitled to free replacement of their plumbing if it leaked previously or in the future.
The Polybutylene Pipe Settlement case is now closed. Homeowners whose structures still contain problematic versions of PB plumbing may nevertheless find that their building or mobile home is damaged by leaks and needs repairs. However there is no longer relief provided under the class action suit.
By 2010 it would be uncommon to find problematic plastic piping in buildings as we expect that where leaks were a problem, they have in many if not most installations, been discovered and repaired by now.
However home inspectors and home buyers as well as building maintenance staff need to be alert for discovery of older problematic or leaky plastic piping in buildings.
When we see several types (colors) of plastic piping mixed together, especially on older renovation or handyman plumbing jobs we worry that amateur work may have omitted use of the proper pipe glues and sealants.
This type of fitting was commonly used from the late 1970s until the late 1980s. Copper fittings were used in most installations from the late 1980s until the late 1990s. Failure of copper fittings is rare. Failure of the actual polybutylene piping also seems relatively uncommon.
For at least some of the extensive plastic pipe failure claims, an important factor in the PBS pipe failure mechanism included water that contained significant levels of chlorine. See Chlorine - sources in drinking water for related information.
Polybutylene Piping failures:
Recommendations (Specifications) for PB Polybutylene Water Pipe Installation
Industry associations, including the Polybutylene Product Line Committee of the Plastic Pipe & Fittings Association have made recommendations for successful installation of polybutylene piping systems, including those listed below. Frankly by 2010 we were never seeing PB installations in buildings at which all of the recommendations below were followed and OPINION it may be that industry experts no longer consider all of the 1990 recommendations necessary. [Feedback invited - CONTACT us.]
Complete details are at CPVC Chlorinated Polyvinyl Chloride Pipe. Excerpts are elow.
Chlorinated polyvinyl chloride (CPVC) pipe is not as flexible as PB or PEX and the fittings are solvent welded (glued) rather than press-on. This pipe is likely to split if freezing occurs. CPVC pipe is suitable for use on both hot and cold water lines.
Our photo (left) illustrates Royal brand PVC sewer piping being installed at a New York Home. Photo courtesy Galow Homes.
Watch out: PVC polyvinyl chloride pipe produced by JM Eagle Corp. is reported to be defective, leaking or breaking as early as in the first year after installation. Details are at PLASTIC PIPE LEAK CAUSES.
See WATER HEATER DEBRIS FLUSH for an example of a deteriorated plastic water heater dip tube debris that clogged the building water supply piping, faucets, fixtures.
Watch out: Using the wrong solvent adhesive, or not using it properly (including pre-cleaning the pipe joints) not only results in leaky plumbing, also the purple solvent cement makes permanent stains, as Oatey Plumbing points out:
Complete details are at PLASTIC vs COPPER Piping in buildings. Excerpts are below.
Many plumbers prefer to work with copper and, although plastic pipe is less expensive than copper, the fittings are expensive. Some areas do not allow plastic pipes based on environmental concerns. Some questions have been raised about the chemicals used in the adhesives used to join sections of piping, and the toxic gases given off from plastic piping during a fire.
Polyethylene (PE) and polyvinyl chloride (PVC) are only suitable for waste, underground water service pipes or cold water piping systems.
Our photographs of plastic water supply piping connections show a new water main (below left) and building supply pipe being connected to copper piping entering a building (below right) in San Miguel de Allende, Guanajuato, Mexico in 2010.
- Adapted with permission from The Home Reference Book
Frequently Asked Questions (FAQs) about plastic water supply piping & plastic drain piping used in buildings
Question: Do Rodents Attack Plastic Tubing or Piping? Does the tubing color make a difference in rodent resistance?
This might seem a strange question but we have blue plastic used for the connection from our gas tanks to our cooker. We have just had it serviced and have been advised that it should be yellow plastic. We have had the blue plastic for a lot of years and have been told it must be changed because the yellow tubing is not susceptible to vermin. Since we have never had a problem with vermin and the blue tubing – I was wondering how true this is and why do the vermin not like the yellow tubing. It would be good to get some advice before we start doing unnecessary work. Thank you for your help - D.M.
Reply: Yes, No, and maybe
We have indeed had reports of rodents chewing on plastic piping of various types, colors, brands, and application (water piping and gas piping for example). And rodents will gnaw on other plastic piping too, not just PEX.
You didn't say exactly what kind of plastic piping you are using nor its brand - that information would let us check with the manufacturer for recommendations about rodent proofing the piping. Certainly we don't want a rodent-chewed hole in any piping but in gas piping it would be particularly dangerous.
I am doubtful that changing from one color piping to another would make much difference in rodent resistance if the piping brand and material is the same; but if the color change includes a change of material, the new material might be more rodent resistance. In a New York installation I have seen yellow plastic-covered flexible copper tubing used for both gas piping (not through walls and ceilings or hidden locations) and heating oil piping. A mouse that chewed the outer plastic cover would most likely not get through the copper, but you'd lose the protective coating at that spot. At that same installation, we used threaded black pipe for gas piping where it runs through hidden locations such as ceilings and walls.
If your pipe damage is occurring indoors you need the services of a pest control expert - an "exterminator" too.
If you can send along details about the pipe type and brand we'll research further. See the CONTACT link on our pages.
Question: my daughter is doing extensive renovations on her house and the question has come up whether to use PEX or copper in the plumbing. I did a google search and the informations is conflicted; see below. Do you have knowledge of, and opinions about, this controversy? Any thoughts would be helpful. Thanks
I have worked with both PEX and Copper piping, though of course
Copper has been around a long time. We recently chose PEX for both water suppy and for a hot water heating line in an addition and so far have been happy with the results.
Our PEX tubing photo at left shows its use in new construction completed in a New York structure in 2012.
You can see the ease of bending radius in these piping runs of both hot (red) and cold (blue) water supply lines.
What follows is an OPINION based on field experience as a builder, renovator & inspector:
PEX water supply piping offers some advantages over copper sweat-fitting piping installation
Our PEX tubing photo at left illustrates an older PEX piping product installed in a Haddonfield New Jersey Home.
PEX Supply Piping Caveats
Copper Water Supply Piping
We discuss types of copper piping and their intended uses and copper fittings beginning at COPPER PIPING in buildings.
Copper Supply & Drain Piping Caveats
We discuss types of copper piping and their intended uses and copper fittings beginning at COPPER PIPING in buildings.
In sum, I don't believe there is a single "right" answer, and each material has some advantages and features that may make it fit a particular installation best. But when I ask my buddy Eric Galow, who is a full time builder, he's a PEX man all the way.
Is PEX the same as Kitec? How does one tell distinguish between Kitec and PEX? - Anon
Reply: Kitec was one brand of PEX piping or tubing.
PEX (cross-linked polyethylene piping) is a general term for a type of plastic piping used in water supply, heating, and other applications.
Kitec® is a specific brand of PEX tubing that was subject of a class action settlement with an end-date for filing claims of 31 March 2012.
There you'll see how to tell the difference between Kitec and other PEX piping brands by color and markings that may be on the tubing.
Detals about PEX piping are at PEX PIPING INFORMATIO
Questions & answers about plastic water supply piping & plastic drain piping used in buildings.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.