How to install a Tankless Coil for Hot Water Heating
Tankless coil installation procedure
TANKLESS COIL INSTALLATION PROCEDURE - CONTENTS: typical steps in the installation or replacement of a tankless heater coil or "tankless coil" installed on a hot water or steam boiler to produce domestic hot water for washing & bathing: how is a tankless coil installed, warnings about leaks, breaking off bolts, and proper gasket handling.
At page top we include a sketch showing the typical installation of a tankless coil on a residential heating boiler. Notice in the page top sketch that a mixing valve or anti-scald valve has been installed between the cold inlet to the tankless coil and the hot outlet pipe from that device.
[Click to enlarge any image]
At left we've adapted a U.S. Energy.gov sketch from a confusing article that mixes up TANKLESS COILS (boiler-mounted devices that we discuss in this article),
As you can see, a tankless coil used for making hot water is a heat exchanger that is inserted into the heating boiler's very hot water. As cold water flows through the inside of the tankless coil it is heated up, leaving the coil hot.
On some heating boiler designs the tankless mounting plate is round (photo below). When I find a pile of tankless coils like this I know the building occupants have not been having a good time in the shower. On other tankless heater coil designs the coil mounting plate may be round as we illustrate in M.C.'s photo later in this article. And tankless coils may mount on any of the boiler sides or even on its top, depending on the boiler's design.
On steam boilers a tankless coil may also be mounted but will always be below the boiler's water level.
Step by Step Tankless Coil Installation Procedure
Watch out: when installing a tankless coil to follow the manufacturer's instructions about handling and sealing the boiler-to-coil gasket (some may specify no sealant is used), and about uniform torquing of the coil faceplate mounting bolts.
Start the installation of a tankless coil heater by doing the unusual: read the instructions from the boiler manufacturer.
We provide some example instructions just below, based on the Crown BDS Series oil fired hot water boilers. But installation details from your manufacturer may vary. The following is adapted and excerpted from the Crown Boiler advice here are typical steps in tankless coil installation:
Unpack the tankless coil and gasket. Be sure all parts are in good order. If there are tie wires holding coil sections together (see Reader Question - below), remove these.
Drain the boiler and heating system [and let the system cool down to a safe working temperature]
Remove the boiler jacket cover panels to give access to the tankless coil mount location
Sketch at left adapted from Crown Boiler's BDS boiler installation instructions. Contact information for the Crown Boiler Company is given below.
Remove the screws or nuts holding the coil mount location cover plate (red & gray rectangle in our sketch) in place, along with the gasket, and discard these. Typically you will see a round or rectangular plate where the tankless coil will mount.
Place the tankless coil gasket (orange in sketch) over the coil and up against the inside surface of the coil's mounting faceplate (green and gray in sketch). [Notice that the manufacturer does not mention any sealant, just the gasket; be sure all mounting surfaces and the gasket are clean.]
Watch out: if an arrow is present on the coil faceplate be sure it's pointing "up" (or as directed) and that the word "TOP" (if present) is indeed at the top of the coil.
Replace the cap screws or nuts (depending on the coil mounting hardware type), and tighten evenly and snug. (blue in sketch)
Watch out: do not over-torque the coil mounting bolts, screws or nuts. If you snap one off in the boiler there will be hell to pay getting out the broken-off piece.
Small leaks at the coil may show up only a an accumulation of mineral deposits, as boiler temperatures evaporate small leaks: you won't see water on the floor.
At left we illustrate the typical piping arrangement into and out of a tankless coil water heating system. Cold water is piped to an inlet marked "COLD" and building hot water supply piping is connected to the tankless coil outlet marked "HOT".
[Click to enlarge any image]
This tankless coil piping example from Crown Boilers indicates the use of a mixing valve or anti-scald valve right at the heating boiler. The company includes an interesting warning reading as follows [Quoting - Crown BDS Installation Manual]
WARNING: Thermostatic mixing valves are intended to increase the supply of hot water available from the coil. They are not intended to prevent a scald hazard.
Really? I speculate that the company's lawyers got a hold of this one - nobody wants to be named in a scald lawsuit. Some manufacturers may hold the view that anti-scald devices should be installed at each fixture, at the point of use.
Our photo shows a typical mixing valve produced by Watts Regulator Co. The mixing valve manufacturer's installation instructions for these devices include similar warnings.
Also be sure to follow the mixing valve manufacturer's installation instructions. For example Watts recommends:
To prolong the life of the Model LF1170-M2 or LFL1170-M2
valve [not shown here], it is recommended that it be trapped as shown ...:
i.e. the hot water inlet to the LF1170-M2 valve should be 8" –
12" (200 – 305mm) below the hot water supply feed. - "Instructions Series LF1170 and LFL1170 Hot Water Temperature Control Valves", Watts Regulator Co. (2013)
do I leave-on or remove tie wires found on the tankless coil before I install it on my heating boiler?
I am installing two DHW coils on a Crown Series 24 steam boiler (sectional, 6-sections). The coils came tied with bailing wire. The bailing wire is not copper, it does however seem to be in logical areas to keep the coils together and ridged. Is this done just for shipping? Should I remove the bailing wire, or does it stay on the coils helping hold them together?
This ... is of the DHW cools for my Crown boiler. This is just one of them, and shows the bailing wire in question. My gut says remove it, but ? - M.C. 2/24/2014
Before we saw the photo we were not sure of the right answer. But from the photo I'd certainly expect that was junk wire intended to be removed. These are "tie wires" intended to prevent the coil sections from damage due to flopping around during shipping. I'm also a little worried about tankless coils showing up exposed - it's the fins and tubing that transfer heat from boiler water to water in the coil - I wouldn't want the coils to be bent, dinged, or crushed. Is this new equipment?
Don't leave these wires t in place - you would risk unwanted corrosion on the coil itself once it's installed, as well as risking dropping junk into the boiler interior as the wire rusts and falls off.
But if on removal the coils seem to flop too loosely, I'd look carefully at how they'll be suspended in the boiler interior - and let me know if that looks odd and we'll pursue it with Crown.
For example if the coil tubing were so flexible that it fell inside the boiler ending in contact with a hot spot that'd not be very attractive.
Also take a look at MIXING / ANTI-SCALD VALVES - you may want to install a mixing valve if one is not already provided, both to avoid a scalding risk and to permit more efficient use of the coil.
Our photo (left) illustrates a heating boiler with two rectangular tankless coils installed. [Click to enlarge any image]
I would not leave a wire of a different metal wrapped around a coil to be inserted into the boiler - without first checking with the manufacturer. I can imagine two very different situations:
A different metal wire wrapped for stability during shipping might actually cause corrosion by galvanic action when the coil is inserted into the boiler - so should be removed
On the other hand
A manufacturer *might* have wrapped a different metal wire around the coil tubing as a sacrificial anode much as we see inserted into a domestic water heater tank.
So what we need is to know the manufacturer of the coil, or if there is none, we'd contact the boiler manufacturer - Crown - to find out what's up.
Are there any installation instructions with boiler? If not I'd download those as they may address this question. Here is contact information for your boiler manufacturer:
Crown Boiler Co.
P.O. Box 14818
3633 I Street
Philadelphia, PA 19134
You are correct this boiler has two coils. they are not wired to each other, they came shipped separately and with adequate protection. The inlet is standard pipe thread, and in the mounting plate the inlet spits off to three separate finned copper tubes that each go into the boiler and make a few passes then come back to a fitting that runs them all back to one tube.
On the three tubes that zigzag back and forth on their several passes they are tied together with bailing wire. Would the bailing wire just rust away eventually, meaning that it is there just for shipping, and should be removed?
I confirmed with [the boiler manufacturer] Crown that they should be removed.
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
"BDS Series Oil-Fired Hot Water Boilers, Installation Instructions, Models GS-080 -> Crown BDS-236", Crown Boiler Company, BDS 12-99, Crown Boiler Co.
P.O. Box 14818
3633 I Street
Philadelphia, PA 19134
Website: http://www.crownboiler.com, retrieved 2/26/2014, original source: http://www.crownboiler.com/manuals/content/ All_Models/BDS%20Series%20%28all%20models%29.pdf
The following link provides access to literature or manuals for previous Crown products:
 Bosch Tankless Water Heaters - http://www.boschhotwater.com/
[1a] Bosch, "Instrucciones de instalacion y manejo, Calentador de agua instantaneo, Confort / Confort S 6BP / 6BP n 10BP / 10BP N 13BP / 13BP N"
Robert Bosch, S. de R.L. de C.V., Calle Robert Bosch 405, Zona Industrial, Toluca, Edo de Mexico CP 50070, website: www.bosch.com.mx, Tel: 800-11-26724 (2010)
 Chromolite Tankless Water Heaters
 U.S. Department of Energy on Tankless Water Heaters - http://apps1.eere.energy.gov/consumer/your_home/water_heating/index.cfm/mytopic=12820
 "Tankless or Demand Type Water Heaters,"U.S. Department of Energy, retrieved 10/14/2012, original source: http://energy.gov/energysaver/articles/tankless-or-demand-type-water-heaters [Copy on file as Tankless_Water Heaters_DOE..pdf] retrived anew 2/25/2014
Home Inspection Education Home Study Courses - ASHI@Home Training 10-course program. Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference Book, a reference & inspection report product for building owners & inspectors. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference eBook, an electronic version for PCs, the iPad, iPhone, & Android smart phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter inspectaehrb in the order payment page "Promo/Redemption" space.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones
Wikipedia provided background information about some topics discussed at this website provided this citation is also found in the same article along with a " retrieved on" date. NOTE: because Wikipedia entries are fluid and can be amended in real time, we cite the retrieval date of Wikipedia citations and we do not assert that the information found there is necessarily authoritative.
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Or choose the The Home Reference eBook for PCs, Macs, Kindle, iPad, iPhone, or Android Smart Phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter INSPECTAEHRB in the order payment page "Promo/Redemption" space.