Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
AGE of PLUMBING MATERIALS & FIXTURES
AIR DISCHARGE at FAUCETS, FIXTURES
ANTI SCALD VALVES
ANODES & DIP TUBES on WATER HEATERS
BACKUP PREVENTION, SEPTIC
BACKUP PREVENTION, SEWER LINE
BACKWATER VALVES, SEWER LINE
BATH & KITCHEN DESIGN GUIDE
CHEMICAL CONTAMINANTS in WATER
CHEMICAL ODOR SOURCES
CHLORINE IN DRINKING WATER
CLOGGED DRAIN DIAGNOSIS & REPAIR
DEBRIS in WATER SUPPLY, Water Heater
DEPTH of SEPTIC TANK
DRAIN & SEWER PIPING
FAUCETS & CONTROLS, KITCHEN & BATH
FAUCETS, OUTDOOR HOSE BIBBS
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOOR DRAIN / TRAP ODORS
FLUSHOMETER VALVES for TOILETS URINALS
GAS PIPING, VALVES, CONTROLS
GALVANIC SCALE & METAL CORROSION
HARD WATER - SOFTENERS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
LEAD POISONING HAZARDS GUIDE
LEAD IN DRINKING WATER, HOW to REDUCE
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MUNICIPAL WATER PRESSURE IMPROVEMENTS
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
ODORS, SEPTIC or SEWER
ODORS SEWER GAS in COLD WEATHER
ODORS, SULPHUR SMELL SOURCES
ANIMAL or URINE ODOR SOURCE DETECTION
PIPING IN BUILDINGS, Clogs Leaks Types
PLUMBING FIXTURES, KITCHEN, BATH
PLUMBING NOISE TRANSMISSION CONTROL
PLUMBING VENT DEFINITIONS & CODES
PLUMBING VENT DEFECTS & NOISES
PUMPS USED in BUILDINGS
PUMPS, WATER REPAIR
RELIEF VALVE LEAKS
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
REPAIR BURST LEAKY PIPES
METHANE GAS HAZARDS
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SHUTOFF VALVE LOCATION, USE
SULPHUR & SEWER GAS SMELL SOURCES
SWEATING (CONDENSATION) on PIPES, TANKS
TOILETS, INSPECT, INSTALL, REPAIR
WATER, WELLS, WATER TANKS: TESTING GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMPS & TANKS
WATER SOFTENERS & CONDITIONERS
WATER SOURCE ALTERNATIVES
WATER SUPPLY & DRAIN PIPING
WATER SHUTOFF VALVE LOCATION, USE
WATER SHUTOFF VALVE, WELL PUMP
WATER TESTS, CONTAMINANTS, TREATMENT
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
Water softener alternatives that do not use salt or other chlorides: this article describes alternatives to conventional salt-based water softeners or water conditioners. Some of these alternatives work quite well at treating hard water (high in mineral content) but we warn that some other "water softener devices" often sold to homeowners are in fact ineffective.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Other Water Softeners or Methods for Removing Hardness & Minerals from Water: Real vs. Fake Water Treatment Equipment
Effective Alternatives to Salt Based Water Treatment for Hard high-mineral content water
Other methods of water softening may have different potential effects on the septic system, as we discuss here.
Chelating agents & chelating additives, treatments, or chelating systems for treating water high in minerals use chelating agents. Dow Chemical explains how chelating agents work to address minerals in water, various products, industrial processes, etc.
Reader Question: who can install a chelating cartridge to handle hard water?
I finally decided to do something about the hard well water and have ordered a chelating cartridge to be slipped into the stream after the particulate filter and before the big, blue reservoir water pressure tank. ... Do you know of someone whom you would trust to look at the present arrangement and use their noggin when planning how to get the flow diverted out to a new cartridge holder and then back into the present line, providing a bypass and possibly even a takeoff to get water for the outside spigot out before it goes through the chelator? I'd hate to see the job botched; it's such a neat piece of work as it stands.
I sure hope that you've heard good things about the chelation approach -- this uses citric acid to bind Ca++ and apparently (which makes sense) also can reverse calcium carbonate deposits already in place. It seemed to be a lot kinder to the septic tanks than a salt-based system. (Those have never made much sense to me, I'm afraid.). - E.O., New York
Reply: Discussion of chelating agents for home water softener treatment as an alternative to salt-based water softeners
Any licensed experienced plumber can recommend the installation location for your water treatment equipment and can handle the plumbing tasks themselves.
Chelating agents to bind various metals (iron, copper, manganese, calcium, and other metals occur naturally) that occur in water supply and in other raw materials that affect a wide variety of products, processes, and in mechanical systems have been in use for some time. Much of the literature discusses food processing, personal care products, industrial applications, pharmaceuticals, and stabilization of other products affected by minerals in water, and treatment of boilers and similar equipment to clean or remove mineral deposits.
For example, Dow Chemical discusses the effectiveness of chelating agents, the varied uses of chelating agents and how chelating agents work in the company's product literature their VERSENE, VERSENEX, and VERSENOL Chelating Agents that Dow indicates are generically referred to as EDTA, HEDTA, DTPA and NTA..
We don't have experience with the use of citric acid for those purposes. However some authorities that citric acid, a weak organic acid, is effective in binding minerals in water.  Just how effective the filter system you are installing will be in handling the hardness of your water supply surely depends on the rated capacity of the filter (in gallons per day), your daily water usage, and the hardness of your water supply. In your immediate area of Dutchess County, NY, the well water is very high in mineral content and also in iron.  
We agree that avoiding dumping excessive salt into a septic system (a concern you expressed) is smart thinking. A properly adjusted water softener should not be sending excessive salt to the septic drainfield, though indeed Gayman and others have reported on that concern. More septic system drainfield damage may be caused by flooding from excessive regeneration cycling or even a "stuck control" on a conventional water softener. Details are at SALT OR WATER INTO SEPTIC.
But before buying and installing a specific water treatment device, we recommend that you test your water to determine the degree of hardness and that you compare your anticipated daily water usage rates with the treatment capacity rating of the chelating filter you are considering.
Precipitating water softeners using additives such as borax precipitate out minerals as a white sludge but I wouldn't recommend this equipment for residential use where clogging pipes and increased water alkalinity may be a problem.
Reverse osmosis (RO) water purifiers (see sketch at page top) will also remove minerals from water leaving it soft. These systems do not discharge salt into the drain system, though they do discharge water.
We don't know (yet) which uses more discharge water - a water salt-based water softener or an RO system - I'll report that data here.
Culligan™ reports in their Water Softener Installation/Maintenance Guide that "The backwash interval is preset at the factory for 10 minutes which is adequate for most water supplies. It is adjustable, however, for 5 to 30 minutes. It is recommended that backwash last just long enough so that the effluent from the drain line is clear. Backwash too long and water is wasted, not long enough and the tank becomes fouled with sediment."
Details about reverse osmosis are at REVERSE OSMOSIS WATER TREATMENT
See REVERSE OSMOSIS CONCENTRATE WASTE DISPOSAL for a discussion of the possible impact of reverse osmosis water treatment equipment's wastewater concentrate when it is disposed into a septic system.
Iron contaminants and high manganese contamination are often found along with water that is high in calcium and other mineral content. These treatment methods that focus on iron removal from well water: 
Polyphosphate treatment can remove 0-3 ppm of soluble iron in water supplies.
Greensand Filters (using glauconite, a green clay mineral as ion exchange media glauconite, a media that is backwashed periodically using potassium permanganate) can remove 0-10 ppm of iron from water (and are great at removing sulphur odors as well). "Greensand" filters absorb soluble iron and manganese. But check the pH of your water before using potassium permanganate. If your well water pH is less than 6.8 this approach doesn't work well.
Chlorination + charcoal filtration: for higher levels of iron in water (not your case if your test was accurate) a chlorinator combined with charcoal filter can remove higher levels of iron and manganese dissolved in well water, and are also typically rated as 0-10 ppm.
The charcoal filter removes the residual [and potentially harmful carcinogenic thrhalomethanes (THM) produced by use of chlorine, residual chlorine, and thus and chlorine odors.
Because chlorine acts as a disinfectant, this design keeps the charcoal filter working longer by retarding bacterial growth. Periodically, however, the charcoal filter portion of the system has to be replaced.
Details are at CHLORINATORS & CHARCOAL FILTERS
Ion Exchangers (a water softener) can remove 0-10 ppm of soluble iron, but frankly water softeners are not designed primarily for that purpose. So often in high iron-content water homes I've examined, the professionals usually have installed one of the other iron removal methods upstream (ahead of) the water softener.
That also means you won't need to set the softener to use more salt than necessary to deal with hardness just because you're trying to remove iron from your water
Some magic water softener equipment is sold such as magnets or other magic "catalytic" devices which claim to remove hardness (mineral ions) from the water by surrounding a water pipe with a magnet or other exciting ideas are simple junk science. The only "hardness" they remove is money from your wallet.
Epsom Salts and Septic Systems: Epsom salt is not sodium chloride. People who use Epsom salt baths, such as for a sore foot, are unlikely to discharge enough Epsom salts into a septic system for it to be measurable. Household use of Epsom salts should not be a concern for the septic system.
Continue reading at SCALE PREVENTION, WATER HEATER or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Greywater System Books