InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Water softener plumbing water supply & drainage troubleshooting FAQs.
This article series describes procedures for diagnosing and repairing water softener or water conditioner problems including water conditioner control settings and adjustment or repair, brine tank and brine tank float cleaning and repair, and the proper amount of water softening or conditioning that is needed.
Question: Where should I dispose of water softener drainage?
I am required to put a barrel filled with stone for my softener drain, I will only be 2' from my basement wall (concrete poured wall). Will I have problems with this? What should be a safe distance. The soil is sand. I have absolutely no other place to put it. Thanks for any information. - Joe 11/23/11
First, a solid barrel filled with stone won't work as a water softener drain destination; once the barrel has filled it'll just overflow. If you mean that you are trying to construct a drywell or seepage pit to accept water softener drainage, that might make sense. But you need to keep the drywell far enough from the foundation wall so that water from it doesn't leak back into the building, nor into the septic system.
While a concrete foundation wall is somewhat leak resistant, cracks, seams at the footing, and even direct moisture penetration mean that putting a drywell right next to your house is asking for an eventual water entry problem. With sandy soil it's an engraved invitation for water entry. If your foundation is a really tight one the water may not appear immediately, but eventually I expect it'll find its way inside. I'm sorry but I am doubtful that this will be a usable long term or even intermediate term solution. You'd be better off finding a more distant location (with sandy soils, 20 feet or more away) even if you have to use a pump to move the wastewater.
Question: water pressure now seems worse than before we installed a water softener
We recently installed a water softener in our home. Before we installed it, our water pressure was fine. Now that we have filled it with salt and recharged it, we have very little water pressure. Why is this? If I hit bypass, the water pressure goes back to normal. - Angela 10/16/12
If the water pressure problem has been present since the softener was installed, I suspect an installation error, such as a copper pipe joint partly blocked by solder.
If the problem is not since new but has just occurred, perhaps the bypass valve is not opening fully when in softener mode.
You DID put the salt in the right tank, yes?
Ps in links at page top see our article on the Bypass Valve for repair instructions.
Question: bubbles at toilet when water softener is operating
Commode and kitchen sink gurgles/bubbles and water drains from commode bowl while neutralizer/softener operates.
What is the problem, please? - Linda Kennedy 12/7/12
Reply: building drain waste vent DWV system problems
If a kitchen sink drain and toilet are bubbling that suggests that the plumbing vent system that should be serving those appliances is absent, blocked, clogged, missing, or improperly installed;
You may be noticing the noises when the water softener is in backwash/regeneration mode more than at other times because of the added water volume passing down the drain line or because of the point at which water softener drainage is being connected to your plumbing drain system.
The city recently came in and changed our water reader and once they did our water consumption went from 10,500 gallons to 55,500 gallons of water in a 28 day cycle. The only thing running when we were notified was the water softener BUT I do not know for sure if it was in its cycle for the day or if it was the problem. The thing is the city just replaced their head in our basement a day before we started wasting water. WHat gives, if anything? Is this normal or was it just our luck? Any ideas would be great. Thanks
(Feb 15, 2013) Shannon - in New Castle said:
I'm new to having a water softener.. I don't know how to use this thing, don't know how to adjust it, and can't get it to cycle. How often should it cycle for 2 people living in the house? There are NO stickers or labels on it anywhere to tell me what make/model/mnfctr it is either. I'm pretty sure the dern thing hasn't run in over a week now, the water is starting to smell really strong... HALP!
(Feb 8, 2014) kawika said:
Similar to the question "discolored water after water softener regen cycle". I cleaned the brine tank but I still get discolored water afar regeneration. We have only noticed the discoloration in the 2nd bath toilet and tub, nowhere else. it clears up after 3 flushes.
Kawika, I'm just guessing, but it seems to me that if water looks different colors at different fixtures in the building I'd think the root source is not the softner (that all water passes through) but perhaps the piping or some other contaminant, or iron, or debris source.
If you see it mostly at a toilet it could be worth cleaning debris out of the toilet tank too.
he discoloration is only present immediately after a regeneration cycle. Why only in the toilet/tub is unknown. If it were the piping or other source it should be present at all times.
I agree with your reasoning, more or less; sometimes a fixture that runs water faster (like a tub) will stir up and show debris that slower running fixtures don't. A toilet would offer the opposite explanation: debris often accumulates in the toilet tank - in part because the relatively slow fill rate doesn't stir it up enough to flush out when the toilet is flushed.
Start (because it's easy) by taking a look in the toilet tank; look for deposits on the tank walls or crud on the tank bottom; that may point to a water supply debris problem; if there are yellow stains but no deposits more often that points to iron in the water;
With that simple look out of the way and assuming we want to pursue the water softener, I'd check the softner brine tank - in these articles we describe cleaning and disinfecting the brine tank. It's tempting to also run a disinfectant cycle through the water softner itself but I would not do that without knowing the brand and model and then checking the manufacturer's cleaning instructions.
1. checking and cleaning the brine tank
2. running the softener through an extra regen cycle
Toilet tank is clean. Cleaned brine tank, manually ran two regenerations…next scheduled regeneration had no water discoloration…latest regeneration (Today) had the discoloration back in toilet (cleared after 4 flushes).
are we certain that the incoming water from the source is not the origin of the discoloration you're seeing? Have you tested that water - ahead of any treatment equipment?
Question: white residue in dishwasher
(Feb 16, 2014) stanley costello said:
i get a light powder like residue on my dishes after a dishwashing cycle
I've seen this deposit in more than one circumstance: using too much dishwasher detergent, very hard water supply, and on occasion, debris that needs to be cleaned from the dishwasher bottom.
(June 7, 2014) Ann said:
Just set up new digital water softener. finished settings and run regeneration cycle. It carried out regeneration adn then started cycle all over again ? what is wrong pleaase - what should I do?
Question: replace algae-contaminated water softener?
(June 9, 2014) David Williams said:
have well water system. had a bad algae bloom. water co. said softener had to be replaced. could it have been cleaned, repaired instead?
I'm unclear why a dirty water softener would need replacement; someone is giving expensive advice that's safe for them and costly for you. Instead I would follow the water softener cleaning and disinfection procedure in your water softener's instruction manual or see our water softener cleaning procedure article at
I cleaned my water softner tank and now I can't get the prime back. Please help!
If you mean your well pump has lost prime just search inspectApedia for "LOST WELL PRIME" or "HOW TO PRIME THE PUMP" to see procedural details.
If you mean the water softener is not filling the brine tank you will want to check for disconnected tubing, a clogged check valve, or a clogged or improperly set (e.g. on bypass) control valve.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
USA GE Water Softener Warranty Service: All warranty service provided by our SmartWater
Servicer Network. To schedule service, on-line, 24 hours a day, visit
us at GEAppliances.com, or call 800.GE.CARES (800.432.2737) (U.S),
or 866.777.7627 (Canada),
Canada GE Water Softener Warranty Service: provided by GE Canada Factory Service Centers or an authorized technician. CAMCO Inc.,
Todos los servicios de garantía son proporcionados por nuestra red de
proveedores de servicios autorizados SmartWater.
Para programar un
servicio, por Internet, las 24 horas al día, visítenos en GEAppliances.com
o llame al 800.GE.CARES (800.432.2737).
 North Dakota Standards for Water Softeners, North Dakota General Authority Law, Chapter 62-04-08, Water Softener Units http://www.legis.nd.gov/information/acdata/pdf/62-04-08.pdf. "The objective of this chapter is to provide a standard of quality, capacity,
and performance for water softener units. Water softener performance
is to be based upon referee tests procedures described in section
 Culligan Mark 10 Water Softener 1994-1998 Installation and Operating Instructions (covering models manufactured after 1995) (1-96) 01881948.pdf available from www.culligan.com
 Water Softeners, CMHC, Canadian Mortgage and Housing Corporation, cmhc-schl.gc.ca/en/co/maho/wawa/wawa_005.cfm - October 2008. Canada Mortgage and Housing Corporation acknowledges the contribution of Health Canada to the development of this document. For further questions regarding water treatment and water quality, contact Health Canada at email@example.com or call 613-957-2991 or 1-866-225-0709.
 "Commercial Water Softener Installation and Operating Instructions", IBC Filtration & Water Treatment Products (Australia) for commercial, industrial and residential application www.ibcwater.com.au (07) 3219 2233
 "Non electric water softener,
Installation and Operating Instructions", IBC Filtration & Water Treatment Products (Australia), op.cit.
 "Water Softener Twin Tank Installation and Operating Instructions", IBC Filtration & Water Treatment Products (Australia), op.cit.
 Our Water Hardness Table used at originated with but was edited and added to from http://www.bestfish.com/tips/110598.html and also from http://www.water-research.net/hardness.htm
 Thanks to reader Gail Sanchez for discussing water softener backups and floods after an electrical outage - August 2010
 Water Right, 1900 Prospect Court
Appleton, Wisconsin 54914, Tel: 920-739-9401, Website: http://www.water-right.com/ and their water softener manuals are available online at http://www.water-right.com/library/literature/literature_manuals.html
 General Electric Corporation, Operation Manual, 740/760 [Water Conditioner or Water Softener] Control, 255 and Performa Series Valves, (268, 268 FA), General Electric Corp. 2007
Home Inspection Education Home Study Courses - ASHI@Home Training 10-course program. Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference Book, a reference & inspection report product for building owners & inspectors. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference eBook, an electronic version for PCs, the iPad, iPhone, & Android smart phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter inspectaehrb in the order payment page "Promo/Redemption" space.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones
Wikipedia provided background information about some topics discussed at this website provided this citation is also found in the same article along with a " retrieved on" date. NOTE: because Wikipedia entries are fluid and can be amended in real time, we cite the retrieval date of Wikipedia citations and we do not assert that the information found there is necessarily authoritative.
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Or choose the The Home Reference eBook for PCs, Macs, Kindle, iPad, iPhone, or Android Smart Phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter INSPECTAEHRB in the order payment page "Promo/Redemption" space.