Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
Ask a Question or Search InspectAPedia
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
AGE of PLUMBING MATERIALS & FIXTURES
AGE of CHIMNEYS & FIREPLACES
AGE of AIR CONDITIONERS & HEAT PUMPS
AGE of HEATERS, BOILERS, FURNACES
AGE of PIPING
AGE of WATER HEATERS
AIR DISCHARGE at FAUCETS, FIXTURES
AIR INLET VALVE, WATER TANK
AIR VOLUME CONTROLS, WATER TANK
ANTI SCALD VALVES
ANODES & DIP TUBES on WATER HEATERS
APPLIANCE EFFICIENCY RATINGS
AQUASTAT CONTROL Functions
BACKDRAFTING HEATING EQUIPMENT
BACKFLOW PREVENTER VALVE, HEATING SYS
BACKFLOW PREVENTER, HEATER WATER FEEDER
BACKUP PREVENTION, SEPTIC
BACKUP PREVENTION, SEWER LINE
BACKWATER VALVES, SEWER LINE
BOD WASTEWATER TEST
BLOCKED DRAIN REPAIR METHODS
BUILDING SAFETY HAZARDS GUIDE
CARBON MONOXIDE - CO
CHECK VALVES, WATER SUPPLY
CHEMICAL CONTAMINANTS in WATER
CHIMNEY INSPECTION DIAGNOSIS REPAIR
CHINESE DRYWALL HAZARDS
CHLORINE IN DRINKING WATER
CHLORINE IN SEPTIC WASTEWATER
CLEANOUTS, PLUMBING DRAIN
CLOGGED DRAIN DIAGNOSIS & REPAIR
CLOGGED SUPPLY PIPES, DIAGNOSIS
CLOGGED SUPPLY PIPES, REPAIR
CLOGGED SUPPLY PIPES, HOT WATER
CONDENSATION or SWEATING PIPES, TANKS
CROSS CONNECTIONS, PLUMBING
DEBRIS in WATER SUPPLY, Water Heater
DEPTH of DRAIN & SEWER PIPES
DEPTH of SEPTIC TANK
DIAELECTRIC PIPE FITTINGS
DRAIN & SEWER PIPING
DRAIN LINE DEPTH
DRAIN a WATER HEATER TANK
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOODED HEATING EQUIPMENT REPAIR
FLOODED SEPTIC SYSTEMS, REPAIR
FLOODED WATER HEATER REPAIR
FLOOR DRAIN / TRAP ODORS
FLUSHOMETER VALVES for TOILETS URINALS
GAS DETECTION INSTRUMENTS
GAS FIRED WATER HEATERS
GAS LP & Natural Gas Safety Hazards
GAS LP & Natural Gas Pressures
GAS PIPING, VALVES, CONTROLS
GALVANIC SCALE & METAL CORROSION
GALVANIZED STEEL PIPING
HARD WATER - SOFTENERS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
LEAD POISONING HAZARDS GUIDE
LEAK TYPES, Water Supply/Drain Pipe
MANUALS & PARTS GUIDES - HVAC
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MIX VALVE SCALD PROTECTION, Best Practices
MUNICIPAL WATER PRESSURE IMPROVEMENTS
MOLD INFORMATION CENTER
MVOCs & MOLDY MUSTY ODORS
NOISE / SOUND DIAGNOSIS & CURE
NOISE CONTROL for HEATING SYSTEMS
NOISE CONTROL for PLUMBING
NOISE, PLUMBING DRAIN DIAGNOSIS
NOISE, PLUMBING DRAIN REPAIR
NOISE, PLUMBING CHECKLIST
NOISE, WATER HEATER
NOISES, WATER PUMP
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
ODORS, SEPTIC or SEWER
ODORS SEWER GAS in COLD WEATHER
ODORS, SULPHUR SMELL SOURCES
ODORS, URINE REMOVAL
OIL FIRED WATER HEATERS
OIL-FIRED BOILERS, HEATING
OIL FUEL TYPES & CHARACTERISTICS
OIL TANK PIPING & PIPING DEFECTS
OUTHOUSES & LATRINES
PIPING IN buildings, Clogs Leaks Types
PLASTIC PIPING ABS CPVC PB PEX PVC
PLASTIC PIPE INSTALLATION ERRORS
PLASTIC PIPE LEAK CAUSES
PLUMBING FIXTURES, KITCHEN, BATH
Plumbing Materials & Fixtures, Age, Types
PLUMBING NOISE CONTROL
PLUMBING VENT DEFINITIONS & CODES
PLUMBING VENT DEFECTS & NOISES
PUMPS, SEPTIC PUMPS
PUMPS, SEWAGE EJECTOR / GRINDER PUMPS
PUMPS, SUMP PUMPS
PUMPS, WATER PUMPS
PUMPS, WATER REPAIR
RELIEF VALVE LEAKS
REPAIR BURST LEAKY PIPES
SEWER GAS ODORS
SEWER LINE LEAKS & ODORS
SEWAGE BACKUP, WHAT TO DO
SEWER BACKUP PREVENTION
SEWAGE & SEPTIC CONTAMINANTS
SEWAGE CONTAMINATION in buildings
SEWAGE EJECTOR / GRINDER PUMPS
SEWAGE PATHOGENS in SEPTIC SLUDGE
SEWAGE PUMP CLOG DAMAGE
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SHUTOFF VALVE LOCATION, USE
SOUND CONTROL for PLUMBING
SULPHUR & SEWER GAS SMELL SOURCES
SUMP PUMPS GUIDE
SWEATING (CONDENSATION) on PIPES, TANKS
TANK TYPES: WATER, OIL, EXPANSION, ALL
TANKLESS WATER HEATERS
Temperature Pressure Relief Valves - Water Heaters
TOILETS, INSPECT, INSTALL, REPAIR
TOILET FLUSHOMETER VALVES
TOILET INSTALLATION PROCEDURE
TOILET OVERFLOW EMERGENCY
TOILET PLUGS, SEWER BACKUP
TOILET REPAIR GUIDE
TOILET TISSUE CHOICES
Toilet Types, Flush Methods
TOILETS, DON'T FLUSH LIST
TRANSITE Pipe Water Supply Piping
TRAPS on PLUMBING FIXTURES
WATER CONTAMINANT LEVELS
WATER HAMMER NOISE DIAGNOSE & CURE
WATER HEATER SCALE - De-Liming Procedure
WATER ODORS, CAUSE CURE
WATER PIPES, Clogs Leaks Types
WATER PRESSURE & FLOW MEASUREMENT
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PRESSURE PROBLEM DIAGNOSIS TABLE
WATER PRESSURE PUMP REPAIR GUIDE
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER PUMP REPAIR GUIDE
WATER QUALITY TESTS, CONTAMINANTS, TREATMENT
WATER QUANTITY IMPROVEMENT
WATER SHUTOFF VALVE LOCATION, USE
WATER SOFTENERS & CONDITIONERS
WATER SOURCE ALTERNATIVES
WATER SUPPLY & DRAIN PIPING
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TESTING ADVICE
WATER TEST CHOICES & WATER TEST FEES
WATER TEST INTERPRETATION
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
LP or Propane Gas Tank Installation: here we provide descriptions and photographs of unsafe gas piping, indications of unsafe or improperly operating gas appliances, gas meters, and other gas installation defects are provided. The photo above shows two 24-gallon LP gas tanks installed outdoors on a wobbly unstable base. This document also provides free sample draft home inspection report language for reporting defects in oil and gas piping at residential properties. Also see How to Report Defects in Oil Piping. DO not copy contents from InspectApedia to other websites.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
If you smell gas you should leave the building immediately and should do so without doing anything that could create a spark such as operating a light switch or telephone.
From a safe location, call your gas company's emergency line and/or your fire department.
Immediate LP or natural gas safety hazards: if there is evidence of an LP or natural gas leak at a building, gas odors, for example, you should:
Specifications for Installing & Inspecting Above-ground LP Gas Storage Tanks - gas cylinders not filled on site
These LP Gas tank location clearances for above-ground gas tanks are given as measured from the tank's relief valve in any direction away from any potential source of ignition (of a gas leak) or where leaking gas could be drawn into a building window or other vent opening.
Sample gas tank inspection report language: Safety: Install secure and level support for the LP gas tank at ... - if a tank tips over and breaks gas line it could be dangerous. This is an inexpensive item. This item should be handled promptly on establishing gas service for the house, preferably before tanks are filled.
Below we provide Installation specifications for Buried LP gas tanks.
How to Find a Buried LP Gas Tank
Finding a buried LP gas tank should not be difficult at a property, since the top of the tank has to be accessible for filling and inspection. Look for the access cover, usually white steel on older LP gas cylinders or black plastic covering an access well on new buried LP gas tanks, as we mention next.
At some new properties you may first have to see and recognize the plastic access well and cover such as the buried LP gas tank cover shown in these photographs.
When the buried LP gas tank access cover is opened, the buried LP gas tank fill valve and regulator are plainly visible as should be a gauge indicating the remaining amount of LP gas in the tank.
The LP tank gauge is installed at a fitting either on the tank top itself or on a combination fitting at the tank top where the gas valves and connections are also installed. This Liquid Petroleum Gas Tank Gauge - LP tank gauge or bottled gas tank gauge shows us that it is intended for installation on a 200 Lb. LP gas cylinder, and that the tank is at about 40% full.
LP Gas tanks are normally filled before the tank is totally empty. The liquid petroleum gas delivery truck driver can assure that no contaminants have leaked into the tank if it is still under pressure. LP tanks are usually not filled to 100% of tank capacity, since doing so would risk sending liquefied LP gas out of the gas tank and into the regulator where it could cause damage or be unsafe.
The curved graph at the upper end of the LP gas gauge dial shows the effects of temperature on the LP gas stored in the tank and thus on the effective remaining amount of fuel in the tank.
Some smaller LP gas cylinders may lack a gauge. When a gas cylinder has no percentage-full gauge and we want to know if the tank is empty or nearly so, we gently rock the tank (be careful not to cause a gas leak). If the tank is heavy and hard to move it's probably nearly full. A bit of experience with pushing slightly on the tank just before and just after it has been filled by your LP gas delivery company can make it easy to have a general idea of the level of fuel in the tank.
Be sure that LP gas cylinders are not so loose or poorly supported that they can tip over - risking injury or even a gas leak and explosion!
Above we provide additional installation specifications for above ground LP gas tanks and cylinders.
Here are some LP gas safety recommendations and home inspection report examples:
LP Gas Cylinder that is Incompletely Buried
Propane Gas Tank Safety Recommendations: The liquid propane gas tank at ... is partially buried - this may not be a recommended building practice; accelerated rust may lead to failure of the container. Please review this question with the gas supply company.
Propane Gas Tank Safety Recommendations:Be sure that the safety relief valve and controls atop the LP gas tanks outside are protected from icing (for example from exposure to rain or gutter overflow). Iced controls can prevent proper operation of safety devices.
Frequently Asked Questions (FAQs) About Installing, Filling, & Inspecting LP Gas Tanks
My gas company is making me pay to move the tank because of the air conditioner...They put it there, not me - Stephen 6/2/11
Seems doubtful that the gas company installed the A/C unit. But even if that unit was installed previously and the LP tank has just now been recognized as a hazard, I'd be grateful that someone recognized and warned you about a safety hazard.
i would like to ask if there is a provision that requires a minimum distance of LP-gas pipe line away from any source of heat? - Randy 5/1/12
Randy, "any source of heat" is not well defined. So no, not at that level of definition. After all, an LP tank is installed outside exposed to heat from the sun. But you can read some LP gas tank location and piping routing safety specifications at GAS PIPING DEFECTS as well as in the article above.
My lp tanks outside my mobile home are just a foot away from where my dryer vents outside at. I just bought this home and it was already like that. Is it safe? I have electric dryer. - Robin 1/10/2013
The heat of a clothes dryer won't be a risk to an LP gas tank; but if the dryer is blowing lots of lint around I'd double check that the LP gas regulator vent is not exposed to lint-clogging from blowing debris - that would be, in my view, unsafe.
Questions & answers or comments about LP tanks or propane tanks at residential installations.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.