Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Aerobic treatment unit final treatment stage details: here we explain the final treatment stage of aerobic septic systems or aerobic treatment units, and we suggest sources for designs and products for aerobic septic treatment units (ATUs) for onsite waste disposal, also called fine bubble aeration systems. We address aerobic septic system design, features, inspection, repair, and maintenance. Product sources are also listed.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Septic effluent, after having been processed through the aerobic treatment unit (ATU), may require further polishing, such as by a private wetland or greenhouse system, and may also require disinfection such as by chlorination or UV light. Other common final ATU effluent treatment systems include sand bed filters, raised bed septic fields, drip irrigation systems, evaporation/transpiration effluent disposal systems, or even a conventional septic drainfield.
When all of this processing has been completed, the effluent may be sufficiently sanitary to permit discharge into a nearby body of water or directly onto the ground surface. In other circumstances the effluent is discharged into a subsurface system such as a drainfield. In this last case, the drainfield or soil absorption system will not need to meet the same treatment requirements as a conventional septic drain field, because of the pre-processing and sanitizing that have already taken place.
Aerobic or aeration septic systems should have a second settlement chamber at or past the septic tank
Because the treatment tank is continually agitated the level of suspended solids remains high.
Therefore an aerobic treatment unit will also include a second settling chamber to make sure that solids are not being sent out to the soil absorption system. Some designs may include a filter at the tank outlet for added protection of the absorption system. Sludge from the settling chamber is returned to the primary tank for further treatment.
Chlorine or Calcium Hypochlorite Disinfection for Aerobic or Aeration Septic Systems
Disinfection methods for treated effluent include chlorination or UV light treatment. Where chlorine tablets are used it is essential that the proper type of tablets are placed into the system (see the two links below about chlorine tablets, swimming pool chlorine tablets, and calcium hypochlorite tablets (the proper stuff to use).
OPINION DF: Although they may be approved for this application, I have never been completely confident in UV-light disinfection systems for several reasons:
Continue reading at ATU MAINTENANCE PROCEDURES or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about aerobic septic system final stage treatment processes.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Septic SystemReferences & Books