Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
This article discusses problems that occur in aerobic septic systems, also known as aeration septic systems or fine-bubble septic aerators. We identify things that cause problems with or harm aerobic septic systems.
At this website are designs and products for aerobic septic treatment units (ATUs) for onsite waste disposal, also called fine bubble aeration systems. We address aerobic septic system design, features, inspection, repair, and maintenance. Product sources are also listed.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Drugs: Systems serving homes (or nursing facilities) where occupants are consuming large quantities of medications, particularly antibiotics or possibly chemotherapy drugs, can be rendered inoperative if the antibiotic or drug level concentration is sufficient to kill the microbes in the ATU.
Disinfectants: Use of improper septic effluent disinfectant in aerobic systems: be sure to use the proper disinfectant in order to avoid both environmental contamination and violation of federal law.
Filter clogging: I have received complaints of frequent outlet filter clogging on some aerobic septic systems. I speculate that the cause may have been a fault in the upstream solid-holding tank(s) such as a broken or missing baffle, use of the system beyond its design load, or perhaps improper use of a septic additive or chemical which may have increased the level of suspended solids.
Salt: Systems serving homes with hard water and which use a water softener can be rendered inoperative if high levels of brine are discharged into the ATU. Water softener backwash and brine will need to be discharged to a separate drywell.
Overloading: A residential ATU is at risk of being overloaded and failing to adequately treat its effluent if it has not been properly sized during its design phase.
Continue reading at ATU TANK SIZES or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about problems with the operation of aerobic septic systems
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Septic SystemReferences & Books