Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Septic alarms / septic or sewage pump alarm systems:
This article describes alarm systems used on septic pumps, grinder pumps, and septic tank pumping stations and pumping systems.
This article series explains the differences between Sump Pumps, Sewage Ejector Pumps, Septic Grinder Pumps, Sewage Pumping Stations, & Septic Pump Alarms.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Our video at right demonstrates the operation of a septic tank pump system alarm.
Septic alarms indicate when the septic tank pump is not operating. Repair is needed promptly.
Advice is given for septic tank effluent or sewage pump selection and use.
Septic pumps used for pumping air in aeration systems and septic pumps used to move effluent in a drip dispersion system are discussed under the appropriate septic system type which are outlined at SEPTIC SYSTEM DESIGN ALTERNATIVES.
Citation of this article by reference to this website and brief quotation for the sole purpose of review are permitted. Use of this information at other websites, in books or pamphlets for sale is reserved to the author.
Use & Operation of Single septic pump alarm system details
It is important to be able to distinguish between blocked building drains, failing septic systems, and lost function of a septic pump.
Otherwise you will soon be unable to run plumbing fixtures and you may not know why.
In a single-pump septic system (shown in the photograph at left and at page top) if you hear the septic alarm buzzer or bell it means that you have very little septic capacity before repairs are made, since there is no working pump.
Use & Operation of Duplex septic pump alarm system details
In a duplex septic tank pump system, (shown in photo at left) sounding of the septic alarm indicates that you're running on the backup pump.
You need to repair the failed septic pump but you can continue to use the building's plumbing fixtures as the backup pump should be working.
There are two different philosophies for designing duplex backup systems - alternating septic pump cycles and reserve septic pump installations.
We discuss simplex and duplex septic pump installations and the different methods of designing a duplex septic pump system in more detail at SEWAGE EJECTOR / GRINDER PUMPS
See the septic alarm test demonstration video at the top of this page for an example of testing the septic tank pump alarm system.
The control panel for a sewage grinder pump system includes pump power switches, alarm, and alarm reset switch or button. The Environment One Corporation grinder pump control panel shown here should be part of any sewage grinder pump system.
Reader Question: what are the common causes for a pump alarm to go off
What are the most common causes a pump tank alarm would go off? My grinder pump is only 4 yrs old and we are still building, so it does not get that much use. C.S. 8/5/12
A competent onsite inspection by an expert usually finds additional clues that help accurately diagnose a problem with a sewage pump such as a defective check valve or a running toilet that keeps filling the reservoir tank. That said, the alarm sounds when the level in the reservoir reaches a level that means that the primary pump is not working, or in a single pump system, that no pump is working.
Continue reading ar SEPTIC PUMP BUYERS GUIDE or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: why is the septic alarm going off in our new home?
What happens with a new home less then 6 months old and the alarm keeps going off? - Carol 8/18/11
Carol, septic pump alarm systems operate on a sensor or float control that monitors wastewater level in the septic tank or pumping chamber. The idea is that if the level rises above some point, the alarm warns the homeowners that the single pump has failed to start, or if it's a duplex pump system (two pumps) that the first pump didn't work and the second pump has started (the backup pump is doing all the work).
Question: Our septic alarm gose off if the system loses power.
Checked all the floats, everything working fine. Pump ok, high level alarm ok, Q: the alarm goes off if the power goes off to the system. It has never done this before. If I turn off the breaker, and back on, the alarm sounds until I silence and reset. - Mike 10/13/11
Mike in the past when we heard about alarm sounding problems the problem was usually traced to a float that had slipped out of position. As you've checked the floats and wastewater levels I'm afraid it sounds as if there may be as shorted wire. The float is basically a switch that closes to sound the alarm. So I'd check the float switch or the actual wiring. If you use an ohmmeter and see zero resistance across the wires that are supposed to trigger the alarm, the wires are probably shorted or the switch is stuck.
Also check for a battery-backup alarm system that is intended to warn of loss of power - basically we can't keep using a septic grinder pump very long if there is no electrical power. The usage time buffer depends on the size of the holding tank.
Thanks. I will disc. the float wires and troubleshoot from there.
Sounds right, Mike. In fact if you can disconnect the wires at both ends that's another way to check for a short between them enroute.
Question: why does a grinder pump alarm go off on a seldom used system?
What are the most common causes a pump tank alarm would go off? My grinder pump is only 4 yrs old and we are still building, so it does not get that much use,. C.S. 8/5/12
A competent onsite inspection by an expert usually finds additional clues that help accurately diagnose a problem with a sewage pump such as a defective check valve or a running toilet that keeps filling the reservoir tank.
That said, the grinder pump alarm sounds when the level in the reservoir reaches a level that in turn signifies that the primary pump is not working, or in a single-pump system, that the pump is working and the level of wastewater has reached the level at which the alarm will sound.
So check your plumbing system for:
Questions & answers or comments about warning alarms on septic tanks and septic pump systems
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References