Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSPECTION
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WASHING MACHINES & SEPTIC SYSTEMS
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WASTEWATER TREATMENT BASICS
WATER, WELLS, WATER TANKS: TESTING GUIDE
WINTERIZE A BUILDING
Septic soakaway bed / drainfield shape & layout guidelines: This septic system design article discusses determination of a conventional drainfield shape or layout. This article is a section of our online book SEPTIC INSPECTION & TEST GUIDE whose chapters are shown at the left of this page. Citation of this article by reference to this website and brief quotation for the sole purpose of review are permitted. Use of this information at other websites, in books or pamphlets for sale is reserved to the author. Technical review by industry experts has been performed and comments from readers are welcomed. Contributors are listed at the end of each article.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Drainfields, also called leach fields, absorption beds, soil absorption systems, and leaching beds, perform the functions of septic effluent treatment and disposal in onsite wastewater treatment systems, conventionally called "septic systems".
We discuss several different conventional soil absorption systems: absorption fields: conventional trench, deep trench, shallow trench, cut-and-fill, and gravelless septic systems. Then we discuss septic absorption beds, and seepage pits. Basic septic system designs are discussed beginning at SEPTIC SYSTEM DESIGN BASICS. Advanced & alternative septic treatment methods are discussed beginning at SEPTIC SYSTEM DESIGN ALTERNATIVES.
Once we know the total area of effluent disposal system needed, such as length in feet of gravel-filled perorated pipe trenches (or galleys or gravelless or whatever) then the septic system installer will excavate to prepare the drainfield in a pattern or shape that divides that length into sub-lengths of parallel (or other) trenches or pits or whatever, and the location, routing, etc. of these will be determined by the lot size and shape so that the necessary septic system components fit AND are separated by the reacquired distances from one another and from site boundaries and other site features like the well or buildings, driveways, and the like.
The specific shape and dimensions for a specific property, soil characteristics, and septic system type can't really be specified precisely here since we know the detailed answers to the septic system drainfield design considerations listed above. But we have posted addition articles on septic system drainfield design that give the general septic system specifications that should be helpful.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Design Manuals for Septic Systems
Onsite Wastewater Disposal Books