Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
How to close the septic tank - restoring a save access cover to septic tank cleanouts & inspection ports. This septic tank pumpout article series provides a step by step, photo-illustrated guide to opening, pumping, and inspecting septic tanks, how a conventional septic tank is located, opened, pumped out, cleaned, and inspected.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
When inspection of the septic tank is complete, the cover is replaced and the operator should make sure that the cover is sound and secure against falling-in.
The first photo above shows that this septic tank cover is in good condition and ready for re-use.
Septic Tank Cover Replacement Safety Warnings
But when replacing the septic tank cover, be sure that your tank cover is un-damaged, that it seals against any significant surface or ground water entering the septic tank, and most important, be sure that the septic tank cover is securely set in place so that it cannot be tipped, moved, or opened by a child. Loose septic tank covers risk a fatal septic-tank fall-in.
The second photo shows the operator replacing the septic tank cover. Notice that he has placed his feet carefully and securely so as to avoid slipping while replacing the cover.
This article series is intended for septic pumping tank truck operators and as general information for homeowners or septic service companies concerned with septic system care. Citation of this article by reference to this website and brief quotation for the sole purpose of review are permitted.
Use of this information at other websites, in books or pamphlets for sale is reserved to the author. Technical reviewers are welcome and are listed at References. This is a chapter of Inspecting, Testing, & Maintaining Residential Septic Systems an online book on septic systems.
When the septic tank has been located and its cleanout port found, if one does not already exist, make a drawing
showing just where the tank is located to assist the owner/septic service company in the future.
We measured at a right angle to the garage wall the distance from the wall to the center of the cleanout cover.
We recorded that distance (in this case, 78 inches).
Then we measured from the garage rear corner to the point along the wall from which we measured out from wall to tank (in this case, 90 inches.) Since the garage is a fixed site feature, we can easily locate the septic tank cleanout cover again with just these two numbers.
We also buried a square of yellow plastic right at the tank cover so that when excavating it in the future
we'll readily see that we've found the right location.
Finally, having recorded the septic tank cleanout cover location, we covered the septic tank cleanout access port with several inches of top soil and re-seeded with grass seed.
"Septic Tank Location - How to Find the Septic Tank" provides additional explanation and illustration of recording the location of septic system components.
Provide the results of what was learned during septic tank pumpout and issue any appropriate Safety Warnings to Owners
Continue reading at : RECORD SEPTIC TANK LOCATION
Below at in the form of individual detailed articles are the Steps in Septic Tank Cleaning Procedure in the order that they should be performed
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Design Manuals for Septic Systems
Onsite Wastewater Disposal Books