Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Septic tank cleanout timing based on objective data:
Determining septic tank cleanout frequency based on physical inspection of the septic tank scum & sludge layers. This article explains when to pump the septic tank and sludge and scum layer thicknesses.
We explain that making these basic observations when a septic tank is pumped, and knowing how long it has been since the previous pumpout can tell us more accurately when the septic tank is going to next need cleanout. This approach can save you money in pumping costs or it may save you money by properly protecting the life of the septic system drainfield.
We discuss the floating scum and sludge layer thicknesses and their measurement for evaluating the septic tank net free area and overall condition.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
A Photographic Guide to Pumping a Septic Tank
This article series provides a step by step, photo-illustrated guide to opening, pumping, and inspecting septic tanks, how a conventional septic tank is located, opened, pumped out, cleaned, and inspected. This guideline is intended for septic pumping tank truck operators and as general information for homeowners or septic service companies concerned with septic system care.
Readers should see Septic Tank Pumping Frequency Guide for a table explaining when to schedule a septic cleanout. Citation of this article by reference to this website and brief quotation for the sole purpose of review are permitted. Use of this information at other websites, in books or pamphlets for sale is reserved to the author. Technical reviewers are welcome and are listed at REFERENCES.
Standard Method 1: Pump the septic tank based on usage level - using the septic tank pumping tables
The most common method used to determine when a septic tank should be pumped is to use a tank pumping frequency table which suggests the tank cleanout interval as a function of tank size and the level of usage of the system, such as the number of occupants in the building.
We provide a table to give a septic pumping schedule at SEPTIC TANK PUMPING SCHEDULE. Refer to the table to see the recommended pumping frequency for the particular septic system being considered. For example, (from the septic tank pumping table), a 1000 gallon septic tank serving a home with five occupants should be cleaned out about every two years. If the tank has only a 500 gallon capacity, it needs to be cleaned about every six months!
Why a septic tank pumping table may be wrong - other septic tank pumping schedules
Septic tank shape affects its pumping needs.
What septic tank pumping tables may not recognize is the effect of tank shape on the need to pump it out. Most septic tanks are 4ft. to 6ft. deep. But if the tank in question is a "low boy" or shallow septic tank (used in areas where there is not enough soil depth to bury a conventional septic tank) it may need to be pumped more often.
Septic tank usage affects its pumping schedule.
Septic tank pumping tables presume a number of occupants based usually on the number of bedrooms in a home. If your home has more occupants or other reasons for heavier septic system use the tank needs to be pumped more often.
Alternative Method 2: Use actual septic tank conditions to decide its next pump out time
By inspecting the conditions in the tank at pumping time you can decide if your septic tank should be pumped more or less often than called for in the pumping schedules. The thickness of the floating scum layer and bottom sludge layer determine how much net free area remains in the septic tank. The size of the net free area in the septic tank in turn determines the EFFLUENT RETENTION TIME - which means that we want effluent to stay in the tank long enough for new solids and greases to separate out before effluent leaves the septic tank.
Pump the tank based on sludge/scum thickness
It is in fact quite possible to MEASURE SCUM & SLUDGE thicknesses in the septic tank.
The exact point at which a septic tank needs to be pumped could be determined by opening the septic tank and measuring the sludge and scum levels in the tank. As long as the sludge and scum layers are minimal (just a few inches of thickness) or in other words, as long a the "net free area" in the tank (see below) is adequate, the tank does not need to be pumped.
See "EFFLUENT RETENTION TIME"
and MEASURE SCUM & SLUDGE for details of these procedures.
Depending on the size of the tank and its dimensions, as the sludge and scum layers become thick the net free area remaining in the tank becomes so small that there is inadequate time for solids to separate into sludge and scum layers. At this point, even though the septic system appears to be "working" its remaining life is in jeopardy because suspended solid waste is being pushed into the drain field.
The volume of net free area in a septic tank determines the time available for this solid and grease separation. That time is referred to as "septic effluent retention time." Short effluent retention time means that the tank sewage remains agitated which in turn means floating and suspended solids are being pushed into and thus are clogging the drain field.
Method 3: there are other reasons people pump septic tanks
There are other reasons besides time or sludge/scum layer thickness that lead people to pump septic tanks out, such as diagnosing septic system problems, odors, backups, or inspecting / repairing septic tank baffles.
We list and discuss these in detail at REASONS FOR PUMPING THE SEPTIC TANK.
Continue reading at SEPTIC TEST FINAL OVERVIEW or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References