Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSPECTION
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WASHING MACHINES & SEPTIC SYSTEMS
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WASTEWATER TREATMENT BASICS
WATER, WELLS, WATER TANKS: TESTING GUIDE
WINTERIZE A BUILDING
Exactly where should you look to find the septic drainfield or soakaway bed? This article helps you find a septic tank, D-box, soakaway bed or drainfield and other components by identifying locations at a building site where those components could fit and should have been placed.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Where should we expect to find a septic system drainfield or leachfield when we're exploring an existing homesite?
This article series and our accompanying septic system location videos explains how to find the leach field or drainfield portion of a septic system.
We include sketches and photos that help you learn what to look for, and we describe several methods useful for finding buried drainfield components. (Septic drain fields are also called soil absorption systems or seepage beds.) Also see How to Find the Septic Tank.
The septic system video#3 at right describes walking an 18 year old homesite by a lake to find the septic system components. We observe one area that by its space and absence of trees and rocks is almost certainly the drainfield location - a fact later confirmed by the owner.
This particular drainfield is uphill from the septic tank and the home which it serves. A septic pumping system will be needed. More videos on septic system location & maintenance are at SEPTIC VIDEOS.More videos on septic system location & maintenance are at SEPTIC VIDEOS.
Suppose we have no documentation and no idea where the drainfield is located. You can walk the building site looking for where a septic field could possibly be placed based on space, soil, and terrain conditions as well as distances from property boundaries and from a well if one is present. Our video at the top of this page gives a site walkthrough example of that procedure.
If you cannot find any candidate locations for a drainfield, go back to "square one" and start with our Septic Tank Location article. Once we can find the septic tank itself, the septic tank outlet defines the location of the effluent drain line that leads to the leach field.
But remember that a drainfield may not be installed at all. There could be a seepage pit, or nothing, yet the septic system may appear to be working, depending on the level of its usage and soil characteristics.
An experienced contractor or inspector can often tell where the leach field is by a simple visual check of the property since s/he knows the typical size, elevation, and soil requirements - in other words, we look to see where a leach field could possibly be fit at a property.
In the photo our client is pointing to a filled-area at the front of his home - which we determined was the probable drainfield area. Unfortunately the installer put his fill right across a creek bed (look in the upper photo at the natural lay of the land). So the drain field did not have much of a life before its effluent leaked into groundwater, appearing in our test as pink-dyed effluent in a nearby stream.
Our article Absorption Field Design discusses how to locate the septic field and how to determine septic field size for a conventional drain field. Knowing these most basic design considerations can tell you where to look for septic fields at a building site by knowing where a working field might be expected to be installed.
If a property has an alternative design system such as a mound or raised bed or other special absorption field designs, those will be more obvious as a terrain feature. You'll see a rather large, rather flat area of raised soil or filled soil on the property.
Sizes can vary widely but a small constructed drainfield made of fill might be 30' wide x 50' long. In the photo a two-level or "tiered" septic mound was installed perhaps 20 years ago; the lower mound is visible in the foreground.
The shrubs are a bit close to the septic field, which we found was in failure - dyed septic effluent appeared in the driveway in the close foreground, and could be seen quickly in this drain basin intended we were told to remove water from the driveway. Actually it was removing septic effluent from the drive.
There may be good visual clues that indicate the drainfield location, especially if you know what to look for.
Areas Cleared of Rocks and Major Trees Often Marks the Location of an Older Drainfield
This older and mature lawn is free of large trees and rocks though those items are found at other areas of this building site. This is where we expected to find the septic tank and drainfield.
Often it is possible to see long parallel depressions which mark leach field trenches. You cannot see them in this photo (a tank and seepage pit were found later) but you can see them in the next section of this article. These depressions are caused by earth fill settlement over the drainfield trenches.
be visible in systems of almost any age. Long parallel depressions, perhaps 24 to 30" wide and
many feet long, perhaps 20' to 40' and spaced perhaps 4' to 6' apart are suggestive of
drain field trenches.
In northern climates when there is light snow cover, the drain field depressions may be easier to see for a couple of reasons:
Wet Areas may Show a (failing) Drainfield Location
It's too bad, but sometimes the leaching bed or drainfield location becomes obvious because it is in failure mode.
If a drainfield is failing by pushing effluent to the surface that is a rather obvious clue of the field location.
The effluent breakout most-often occurs at the low-end of the failing drainfield line(s), but it can occur anywhere that a pipe is clogged, damaged, or leaking. In this photo, which we discuss in more detail below, the septic system failure and thus the septic field location was visually evident even under deep snow cover.
Often it is possible to see an area of raised-fill which was built to house the leach field.
VISUAL CLUES LOCATE the DRAINFIELD contains additional clues that telltale where you can expect to find the septic drainfield.
Citation of this article by reference to this website and brief quotation for the sole purpose of review are permitted. Use of this information at other websites, in books or pamphlets for sale is reserved to the author. Technical reviewers and content suggestions are welcome and are credited at "References."
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about problems with the operation of aerobic septic systems
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.