Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE & SEPTIC CONTAMINANTS
SEWAGE BACKUP, WHAT TO DO
SEWAGE BACKUP TEST & CLEANUP
SEWAGE BACKUP PREVENTION
SEWAGE CONTAMINATION in BUILDINGS
SEWAGE CONTAMINANTS in FRUIT / VEGETABLES
SEWAGE EJECTOR / GRINDER PUMPS
SEWAGE LEVELS in SEPTIC TANKS
SEWAGE NITROGEN CONTAMINANTS
SEWAGE PATHOGENS in SEPTIC SLUDGE
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SMELL PATCH TEST to FIND ODOR SOURCE
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
ALTERNATIVE & WATERLESS TOILETS
TOILETS, DON'T FLUSH LIST
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Odors from the septic drainfield or soakaway bed: this article explains how to diagnose & correct sewer gas or septic odors (and other building smells and odors traced to a failed septic drainfield, leachfield or soakaway bed. Some of the diagnostic steps pertain to all seasons, others to cold weather conditions.
The photograph at page top shows green septic dye appearing in a septic system drainfield during a septic loading and dye test. Even before we performed this test to confirm that the liquid found on the surface of the drainfield area was indeed septic effluent (coming from the septic tank), sewage odors in the drainfield area outdoors told us that the septic field was in trouble. Also see our broad-scope article on diagnosis and cure of sewer gas and septic odors: Sewer Gas Odors diagnosing, finding, and curing septic tank and sewer line smells.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
[Click to enlarge any image]
Look for wet areas in or near the septic drainfield. Consider performing a septic loading and dye test to confirm that the wet areas found are septic effluent from the septic tank.
Even if wet areas around a septic leach field are local ground water or runoff, the added water load that those conditions place on the septic drainfield may themselves constitute a septic failure or may require site work to redirect those water sources away from the drainfield.
If the septic system drainfield is blocked or failed it may be possible to reroute effluent to an un-used or under-used section of the drainfield (if effluent was not being distributed uniformly in the first place) - check the distribution box (if any).
There will be additional evidence of septic field condition in the D-box; if the box is flooded either these lines are blocked (such as by poor, uneven installation, tree roots, or a collapse, something not too likely unless you drove a truck over the fields), or the field has stopped percolating and needs replacement.
If on opening the D-box or excavating a drainfield line you see standing water in the leachfield line, either the field is saturated - lost perc - or the line has collapsed nearby and is not flowing.
You can test this by running a hose into the leach line from the D-box or from your point where you've cut it open.
Sometimes you'll see that only one field line is saturated and failed - you can close it off in the D-box and just use the others to give the saturated one a rest, but at the end of the day, you probably need a new drainfield.
See SEPTIC D-BOX INSTALL REPAIR for help in finding and inspecting the septic system drainfield distribution box.
Septic Repair Shortcuts and Septic Treatment Products and "Magic bullet" septic repair products and procedures like chemicals, additives, root killers, or soil restorers are mostly ineffective, waste money, and in some cases are illegal as they contaminate the environment. If the septic system drainfield is blocked or failed, most often the property needs a new drain field.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References