Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE & SEPTIC CONTAMINANTS
SEWAGE BACKUP, WHAT TO DO
SEWAGE BACKUP TEST & CLEANUP
SEWAGE BACKUP PREVENTION
SEWAGE CONTAMINATION in buildings
SEWAGE CONTAMINANTS in FRUIT / VEGETABLES
SEWAGE EJECTOR / GRINDER PUMPS
SEWAGE LEVELS in SEPTIC TANKS
SEWAGE NITROGEN CONTAMINANTS
SEWAGE PATHOGENS in SEPTIC SLUDGE
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SMELL PATCH TEST to Track Down Odors
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
ALTERNATIVE & WATERLESS TOILETS
TOILETS, DON'T FLUSH LIST
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
This home buyers guide to septic systems article describes what goes wrong with septic tanks, drainfields, and other septic system components. Septic backups, failures, breakouts, odors are often traced to clogged sewer lines, failing drainfields or soakaway beds, or improper piping or septic component installation. This document provides advice for home buyers who are buying a home with a private septic system: homes using an on-site septic tank and drainfield or similar soil absorption system.
Chapter 4 in this article series outlines what goes wrong with septic systems and their various components. Chapter 5-recommends and describes septic inspection and test methods in more detail, explains how to be sure your septic inspection and septic test are conducted properly, tells you where to get more septic system information about a given property, and warns of unsanitary or dangerous site conditions.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Unless special provisions have been made such as protection of piping and septic tanks from damage, vehicle-rated septic tank covers, or similar steps, do not drive vehicles over the septic system.
Driving over septic tanks, septic piping, or drainfields risks costly damage to the septic system and may also be dangerous.
The bulldozer in our photo (left) was called to help remove a truck which drove over septic system components leading to a surprise collapse.
Home made or "site built" septic tanks, often using dry-stacked concrete blocks or even stone can collapse, a fatal hazard if someone falls in.
The septic tank shown in the photo at the top of this page had a concrete cover but when the cover was removed we found that the tank was under-sized, built of concrete blocks, and totally impacted with waste, as shown in this open septic tank photo. The system was inadequate, not working, and required replacement.
A proper loading and dye test would probably have detected this failure since the new owners had effluent in their yard within 24 hours of moving into the home.
Home made septic tanks which are way too small, such as the 100-gallon home made septic tank shown in the upper left of this photo of a too-small septic tank will simply not be functional for normal use.
Steel septic tank baffles rust off, sending solids into the leach field, shortening its life.
A steel tank baffle is visible in the lower left of this photo.
Watch out: Septic tank covers themselves can also collapse, especially if made of steel as shown in the same photo as mentioned above. Falling into a septic tank is very likely to be fatal.
Other septic tank covers may be made of wood which eventually rots and collapses.
Collapsing septic tanks, steel, home made, or any type, are very dangerous. Falling into a tank is likely to be fatal.
Concrete septic tanks such as shown here are pretty durable but they can crack and leak or may have an unsafe cover.
The distribution box has not been placed and is still sitting atop the septic tank. This is a great time to measure and record the exact location of the septic tank and its cleanout access covers.
Concrete tank baffles can deteriorate, crack, break, fall off. Baffles are checked when the septic tank is opened for cleaning.
Fiberglass or plastic septic tanks such as shown just below are also quite durable but may be cracked or damaged during installation or if driven-over later.
Septic Tanks which are not pumped often enough can become filled with sludge and scum, becoming totally impacted. Well before this condition is detected, such systems have sent solids into the leach field, shortening its life.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References