Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Septic tank effluent retention time & net free area: this document answers the question: what is septic tank retention time, or "effluent retention time" and explains the importance of this concept. Septic tank maintenance requires that the tank be pumped at the appropriate interval (given in our table of septic tank pumping frequency).
If the effluent retention time is too brief in the septic tank, solid waste is pushed into the drainfield where that important component is clogged, leading to failure. We explain how we calculate or estimate the required septic tank retention time and we describe a related concept: net free area in the septic tank.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Septic Tank Effluent Retention time and Effective Septic Tank Volume - Why pump a septic tank before it is full of solids and grease?
In short: retention time is the time that septic effluent spends in the septic tank before flowing out to the drainfield. If a septic tank is not pumped frequently enough retention time becomes short and the drain field will have a much shorter life. Solids moving into the drain field will clog it.
A septic tank with too little net free area or free volume for liquid effluent will not permit solids to settle out of the sewage.
The result is that the waste in the tank remains agitated during system use, forcing solids into the absorption system - a condition which can spell the quick and costly ruination of a septic leach field or other absorption system.
Longer retention time in the septic tank permits effluent to separate into floating scum, settled sludge, and clarified effluent. It's clarified effluent not sewage that we want to discharge into the absorption system. Use of this information at other websites, in books or pamphlets for sale is reserved to the author.
Definition of Septic Tank Retention time
Septic tank retention time is the length of time that effluent remains in the septic tank before moving out to the absorption system or leach field. In order for a septic tank to function properly, adequate liquid volume must be maintained to allow for sufficient "settling time" or "retention time" which permits solids to either settle out as sludge or join the floating-scum layer at the top of the tank.
Baffles in the tank prevent the floating scum from leaving the tank, an event which would lead to rapid failure of the soil absorption system or leach field. When pumping is too infrequent, even if the tank is not totally clogged with solids, the reduced liquid volume in the tank (the "net free area") reduces settlement or "retention time" and grease coagulation time.
Definition of net free area or septic tank working volume
Net free area or effective septic tank working volume: The "net free area" (my term) or "effective septic tank volume" is the actual tank interior volume minus the space occupied by settled sludge and floating scum. In addition to the requirements that the sludge level be sufficiently below the baffle and tank outlet, a sludge level which has reached more than 20% of the septic tank volume is unacceptable and such a tank needs to be cleaned.
What is the Required Septic Tank Effluent Retention Time Period?
Retention time requirement: the retention time necessary for a septic tank to function properly depends on the size of the septic tank and the daily wastewater volume or flow. The necessary days of retention time = the effective tank volume divided by the daily wastewater volume in gallons.
This means that if the wastewater flow exceeds 600 gallons a day or if the sludge and scum levels increase to reduce the tank volume below 600 gallons, then we're pushing floating debris into the leach field.
This condition means that the septic tank contents remain agitated when the system is used, forcing small floating solids and grease out of the tank and into the absorption system, shortening the life of that component. If a property owner waits until a system or septic tank is blocked before having the tank pumped, it is quite likely that the leach fields have already been damaged.
This is why various authorities set guidelines on tank pumping/cleaning based on scum layer thickness and sludge thickness, and this is why those figures require cleaning of the septic tank well before it is "full" or nearly full of solids and floating scum.
Continue reading at MEASURE SCUM & SLUDGE or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about septic tank retention time and net free area or effective volume inside the septic tank.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References