Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Septic media filter system operation: this document explains the how septic media filter systems work. When using a septic media filter system, effluent treatment is by both actual filtration and ultimately by a biochemical process as the filter "matures" and includes its own biomass. Both natural media filter septic systems (such as sand, gravel, or peat) and synthetic media filter septic systems (foam cubes, glass, slag) are used, and both single-pass and effluent recycling systems may be employed.
Citation of this article by reference to this website and brief quotation for the sole purpose of review are permitted. Use of this information at other websites, in books or pamphlets for sale is reserved to the author. Technical review by industry experts has been performed and is ongoing - reviewers welcomed and are listed at References.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Media filters are not a new idea, and have been in use in various forms for more than 100 years. An early form of media filtration used simple sand to filter drinking water, though the process used pressure and worked a bit differently from media filters used to treat septic effluent.
For septic effluent treatment purposes, the filter strains the effluent, trapping small solids and debris.The principal septic effluent treatment performed by the filter is biochemical, as a biomass or film of microbes attaches to the filter surface. (I discuss biomats in the context of a conventional drainfield at Biomat Formation.) In contrast with the relatively thick biomass of a drainfield (.5cm to 10cm), a thin biomass film forms on the entire surface area of the media filter.
So it's apparent that the term "media filter septic system" fails to make clear by its name that it's not just "filtering" septic effluent. Very important is the septic effluent and suspended solids treatment that takes place by microbes which form as a biomat on the surface of the filter media.
Effluent passing through the media filter comes into contact with the biomass where the biomat's microorganisms further process and sanitize the liquid effluent by removing pathogens, nitrogen, and viruses. (Treatment that occurs in a septic tank does not remove any appreciable portion of nitrogen from the effluent.)
The septic media filter, because of its porous nature, also supplies air (oxygen) to this process to assist the microbes in digestion of pathogens and organics in the wastewater effluent. The actual treatment process (slightly simplified) is a complex of filtering, adsorption, and oxidation by microbes in the biomat.
For the media filtration system to work, effluent has to be provided from the settlement tank to the media filter at a slow rate, perhaps 5 gallons per day per square foot of media surface. Septic effluent may be passed through the media filter only once - a single pass septic media filter system - or it may be recirculated through the media filter - a recirculating septic media filter system.
Septic media filters (discussed here) are an effluent treatment method. Other types of septic filters, such as greywater filters, washing machine filters, and filters at the effluent outlet of a conventional septic tank are all designed to protect the septic effluent absorption field or leach field. These other septic filters are discussed at Septic & Graywater Filters or select a topic from the More Reading links shown below.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Design Manuals for Septic Systems
Onsite Wastewater Disposal Books