Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSPECTION
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WASHING MACHINES & SEPTIC SYSTEMS
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WASTEWATER TREATMENT BASICS
WATER, WELLS, WATER TANKS: TESTING GUIDE
WINTERIZE A BUILDING
Sand filter septic design details: this document discusses design and use of septic media filters using sand. When using a septic media filter system, effluent treatment is by both actual filtration and ultimately by a biochemical process as the filter "matures" and includes its own biomass. This is particularly true of sand-bed filter septic systems which also often use a recirculating sand bed design to move septic effluent multiple passes through the sand filter system.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Various texts cite the critical importance of selecting the proper sand for a septic media filter. New York's standard specifies a sand grain size of 0.25 to 1.0 mm; if nitrification is required (which may be specified by the local health department), the grain size is larger, 0.5mm to 1.0 mm., and all sand is passed through a 1/4" sieve and must be uniform to a coefficient of 4.0.
The effluent collector pipes below the sand bed discharge the treated effluent to an absorption system such as a drain field placed below the original ground level or possibly into a raised bed or mound system. The raised bed or mound receiving the treated effluent may itself be constructed of sand or other fill material with a percolation rate of not faster than 5 minutes per inch.
Typical sand filter construction (NY State Wastewater Standards) involves an excavated bed area which is filled in layers of material as follows (bottom up):
Sand filter problems: keep deep rooting plants, surface runoff, and heavy traffic (that could compact the media) off of the system. Don't block air movement over the surface of the system with buildings or plantings.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about sand filter septic system designs, maintenance, repair: sand media filter and recirculating sand filters.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
More Reading on Sand Filter Systems
Using a Sand Bed Effluent Disposal System as a Component of Alternative Septic Systems for Difficult Sites. This document includes the NYS Appendix 75-A section on sand filter beds (next citation) as well as sand filter bed design comments and advice from other experts
Sand Septic Filters - New York State Appendix 75-A Design Details for Intermittent Sand Bed Filter Septic Systems
References for this Septic Media Filters Discussion
Design Manuals for Septic Systems
Onsite Wastewater Disposal Books