Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSPECTION
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
This document discusses the design and use of Foam Cube Septic Media Filter systems in alternative wastewater treatment systems. Foam cube and other special septic effluent treatment media (discussed at this website) can permit wastewater treatment on very small lots or even completely above ground where space or soil conditions do not permit a conventional tank and drainfield system.
Media filter septic systems use a conventional septic tank followed by any of several methods to further filter and treat septic effluent before it is discharged to the soil, soil surface, or waterway. Citation of this article by reference to this website and brief quotation for the sole purpose of review are permitted. Use of this information at other websites, in books or pamphlets for sale is reserved to the author. Technical review by industry experts has been performed and is ongoing - reviewers welcomed and are listed at References.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Two-inch open-celled polyurethane cubes are placed into a container to form a packaged or "pre-fab" septic media filter system which is used in either single pass or recirculating effluent mode.
Packaged foam cube septic effluent (wastewater) treatment systems may be placed entirely above ground (but of course will not work in an area of hard freezing climate).
Septic effluent is passed into the foam filter in small doses (1/10 gallon to 1 gallon per cubic foot per dose) using spray nozzles which dose the system from its top.
An advantage of the foam cube septic media system for wastewater treatment is its easy maintenance as the (clog prone) top few inches of foam cubes are easily removed and replaced.
A typical media filter system is designed using a flow of 50 to 65 gallons per day per occupant of the building served by the system. This number, cited by several authors including Jantrania, Minnis, and Kahn, Allen, and Jones, is less than other total wastewater load estimates but is considered by these authors to be realistic and is consistent with a number of studies performed on typical wastewater flow rates and quantities.
The system design maintenance required of the media filter system as well as its operating characteristics vary considerably depending on the media selected, with open cell foam and textiles providing higher gallons per day loading ability than peat and other media.
"Maintenance" in this case will refer to inspection of the media bed to determine when the media needs to be cleaned or replaced. Some systems, such as sand filter beds, are raked or agitated rather than replaced, but ultimately all filter systems will become clogged and face media replacement.
Septic filter media maintenance and replacement cost should be factored into estimates of alterative septic system costs when comparing alternative septic system designs.
Please scroll down for more text, or use the links listed at Related Topics . Green links show where you are in this document.
Product Source List for Filters, Septic Filters & Wastewater Treatment Systems Using Filtration Methods
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Design Manuals for Septic Systems
Onsite Wastewater Disposal Books