Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
Ask a Question or Search InspectAPedia
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSPECTION
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE & SEPTIC CONTAMINANTS
SEWAGE BACKUP, WHAT TO DO
SEWAGE BACKUP TEST & CLEANUP
SEWAGE BACKUP PREVENTION
SEWAGE CONTAMINATION in buildings
SEWAGE CONTAMINANTS in FRUIT / VEGETABLES
SEWAGE EJECTOR / GRINDER PUMPS
SEWAGE LEVELS in SEPTIC TANKS
SEWAGE NITROGEN CONTAMINANTS
SEWAGE PATHOGENS in SEPTIC SLUDGE
SEWER BACKUP PREVENTION
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SMELL PATCH TEST to Track Down Odors
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TOILETS, DON'T FLUSH LIST
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WASHING MACHINES & SEPTIC SYSTEMS
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WASTEWATER TREATMENT BASICS
WATER, WELLS, WATER TANKS: TESTING GUIDE
WINTERIZE A BUILDING
Steel septic tank warnings: this document describes how to inspect the condition of a septic tank, providing special considerations for inspecting steel septic tanks. Inspecting steel septic tanks is a key component in onsite wastewater disposal systems. We describe steels septic tank defects, life expectancy, special problems, and repair methods. The page top photo shows an area where the author walked just before stepping through a rusted-out steel septic tank cover (shown below).
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
STEEL SEPTIC TANKS - Life Expectancy, What Breaks, What to Look For, How to Fix a Damaged or Leaky Steel Septic Tank or Tank Cover or Baffle
Guide to Steel Septic Tank Maintenance and Repair
Special Hazard Warning for Steel Septic Tank Covers
Watch out: Rusting steel tank covers can cause death! Rusted covers can collapse. We have reports of children and adults who have died from this hazard, as recently as December 1997. In 2000 the author consulted in a fatality involving an adult falling into a cesspool.
At a building inspection the author, even though walking carefully, stepped through a hidden, rusted-through steel septic tank cover (shown in the photos above on this page).
At left we're not sure what the heck we've got. This may be a steel septic tank that has collapsed, or a steel access riser to a home-made (out of stones) cesspool. This system was located less than 15 feet from a lake and cannot be working acceptably. And there was no safe cover.
Falling into a septic tank, drywell, or cesspool is quickly fatal, either from being buried by falling soils and debris, or by asphyxiation. Septic gases are highly toxic and can kill in just minutes of exposure. Even leaning over an empty (just pumped) tank has led to collapse and fatality of a septic pumper.
Special Problem with Rusted Off Baffles in Steel Septic Tanks - repair may be possible
The baffle in this septic tank (photo at left) is on the right side of the manhole.
This damage permits solids to enter the soil absorption system. In the photo shown above on this page the steel septic tank baffle has rusted away at its top - visible in the lower left of the tank top opening.
Should we repair a steel septic tank that has lost its baffles?
If a steel septic tank is otherwise in good condition but its baffles have become damaged or have been lost entirely, try inserting a plastic tee in the inlet and outlet waste lines.
Septic tank baffles, or septic tank tees prevent solids from flowing out of the tank into the drainfield, or from blocking waste flow into the tank from the building it serves. But if you see that the steel septic tank baffles have been missing for some unknown time, perhaps a long time, especially at the tank outlet end, you can assume that this condition has reduced the future life of the drainfield by permitting solid waste to flow into that area of the septic system.
See Septic Tank Tees for more details about this septic system component.
Steel Septic Tank Bottom Rust-Out, Leaks, Abnormal Sewage Levels
Steel tank bottoms rust out permitting effluent to leak into soils around the tank, possibly giving a large void in tank at time of testing, thus subverting a loading or dye test. Since steel tank tops can be replaced while leaving the old tank in place, the condition of the top itself is not a reliable indicator of tank condition.
You may spot a leaky steel septic tank whose bottom or lower sides are gone by noticing that for a septic tank that is in use and has not just been pumped out, the level of sewage in the septic tank is lower than the outlet baffle or pipe. Details are at SEPTIC TANK LEVELS of SEWAGE.
Frequently Asked Questions (FAQs) about steel septic tanks
Questions & answers or comments about steel septic tanks: special problems, inspection, troubleshooting, repairs, age, durability.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Onsite Wastewater Disposal Books