Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
STRUCTURAL INSPECTIONS & DEFECTS
AGE of a BUILDING - how to determine
BRICK FOUNDATIONS & WALLS
CHIMNEY INSPECTION DIAGNOSIS REPAIR
COLD POUR JOINTS, CONCRETE
COLUMNS & POSTS, DEFECTS
DISASTER BUILDING INSPECTION & REPAIR
EARTHQUAKE DAMAGED FOUNDATIONS
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOOD DAMAGE TO FOUNDATIONS
FOOTING & FOUNDATION DRAINS
FOOTINGS EXPOSED, Repair Methods
FOUNDATION BULGE or LEAN MEASUREMENTS
FOUNDATION CONSTRUCTION TYPES
FOUNDATION CONTRACTORS, ENGINEERS
FOUNDATION CRACKS & DAMAGE GUIDE
FRAMING DAMAGE, INSPECTION, REPAIR
GRADING, DRAINAGE & SITE WORK
GUTTERS & DOWNSPOUTS
INSECT INFESTATION / DAMAGE
MOBILE HOMES, DOUBLEWIDES, TRAILERS
MODULAR HOME CONSTRUCTION
MOISTURE CONTROL in BUILDINGS
RETAINING WALL DESIGNS, TYPES, DAMAGE
RETAINING WALL GUARD RAILINGS
STRAW BALE CONSTRUCTION
STRUCTURAL DAMAGE PROBING
STRUCTURAL WOOD ASSESSMENT
THERMAL EXPANSION of MATERIALS
TIMBER FRAMING, ROT
WATER BARRIERS, EXTERIOR BUILDING
WATER ENTRY in BUILDINGS
WINTERIZE A BUILDING
This article explains how to notice defective, damaged, improperly supported, or missing structural columns, and other structural column & pier mistakes. Our page top photo shows a telepost used as a "permanent" supporting column. Most models of teleposts or "jackposts" are thin-walled steel and are not designed for permanent use. And all columns require proper bearing support at both the column top and bottom. This leaning, cockeyed jackpost is a structural collapse waiting to happen.
Detecting omissions, such as leaving out a column or it's pier or footing is an important step in learning how to recognize and diagnose various types of foundation failure or damage, such as foundation cracks, masonry foundation crack patterns, and moving, leaning, bulging, or bowing building foundation walls. Also see FOUNDATION DEFECTS OF OMISSION - MISSING
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Some of these are dangerous and risk collapse. But do not fail to pay careful attention to the structural connections themselves: connections between posts and beams, posts and piers, beams and the floors or ceilings they support.
Connection failure is often the weak link in residential structural movement and collapse. See DECK COLLAPSE Case Study for an example. FYI we call a 6-inch concrete filled steel column a Lally column after its inventor.
Some folks call these just steel columns, or lolly columns or steel posts.
Our photos below show a proper use of a temporary column, telepost, or jackpost - that gray screw-jack to the right of the white-painted steel column I am touching. The second photo at right shows why the temporary column was put in place: the hollow steel column supporting this beam had rusted through at its base, risking collapse. The collapse of a structural steel column is increased if the column is hollow, rather than concrete-filled.
Thin-walled Steel Teleposts - Maybe Not the Best Choice for Permanent Repairs
Some Teleposts May be Permitted for Permanent Installation
Shown below, some adjustable screw jacks or teleposts such as some Read-I-Post columns are constructed of a heavier-gauge steel and in some jurisdictions they may be approved for permanent use in structures. Often where an adjustable column is permitted for permanent structural use, once it has been properly adjusted in height, its adjusting rod is removed and the screw is tack-welded in place.
Notice that the installer took care to bolt the Red-I-Post top plate to the beam underside. Let's hope that the beam itself is secured to the floor joists overhead and is protected against lateral movement.
See our page top photo for an example of a horrible installation of a jackpost that is likely to collapse. Below are more examples of improper telepost installations. At below left we have inadequate bearing surface and no connection between the steel bearing plate and the joist underside. It looks as if the post may also be out of plumb. Boing!
Which End Goes Up When Installing Screw Jacks & Teleposts?
Our second dangerous telepost photo at above right you can see that the post top screw has bent the steel plate as it pushed into the beam, and the whole assembly is slipping off of the beam and moving to the right. Some installers place screw jacks or teleposts with the screw down against the concrete floor or pier top.
That allows the larger-diameter post "bottom" to be placed up against a steel plate and against the underside of the beam. This "upside down" installation reduces the chances of bending the steel supporting plate and it also places the thick steel screw down on the (often wet) basement or crawl space floor. The thicker steel screw is slower to rust through to the point of collapse than is the thin-walled hollow steel pipe that forms the body of most teleposts.
As we also discuss at Earthquake Damage to Foundations, defective supporting columns failed at Northridge Meadows during that 1994 earthquake. It appears that hollow 6" pipes were substituted for concrete filled steel Lally columns under part of the building. Once the fireproofing wrap was installed it was not possible to spot this shortcut by visual inspection. The hollow columns failed, permitting the upper floors of the structure to collapse. There were fatalities.
Here are examples of types of omission that contributed to a structural collapse. During our work at the Northridge Earthquake site in California in 1994 we noticed that some of the supporting Lally columns were hollow rather than concrete filled.
"Missing" column footings may or may not be a defect depending on design and soil conditions. In some jurisdictions, a poured concrete floor slab may be considered of sufficient thickness and strength to support the column.
How can we take a photo of a missing structural post or column?
Failure to compact the soil under a column pier or footing or under a poured concrete slab which has been placed on backfill can result in column settlement.
Our client is pointing to a supporting column in a location where we suspect that crack pattern around the column, combined with a slight but observable depression at the column base area suggests its pier may be settling.
When we see a column whose base penetrates the concrete floor slab we know the floor was poured around the column - the column was put in place first. We can't see if a proper pier was installed to support the column base - as is usually the case. Perhaps in the installation we show here, the builder set a 4-inch solid concrete block on (poorly-compacted) fill inside the building foundation, set his post on that, and jacked away. When the fill settles the block settles too, and the column may move downwards, cracking the concrete floor around its base in the pattern we show here.
As we also discussed at BASEMENT LEAKS, INSPECT FOR, even a concrete filled steel Lally column can deteriorate enough to lead to building movement or instability. But hollow steel columns such as teleposts and even steel pipes people sometimes think will support a building, heavy exfoliating rust on the columns can lead to crushing or splitting and a structural collapse.
When evaluating the history of water entry in a building we like to look at structural components that have been in place since the building was completed - those are parts that will have been exposed to flooding or recurrent wet floors if water entry has been a problem.
Light superficial rust on a Lally column base is not structurally significant, though it might indicate a history of wet floors in the area. The rust shown at the Lally column base at below left is just a chip, it is insignificant, and we concluded that there was no evidence of a history of wet floors in this basement area. The steel column at below right penetrates the floor slab - we think it may sit on a hidden pier (there was no sign of settling).
But the column surface rust at be;pw right suggests the floor has been wet in this area. We did not think this column had suffered damage that risks it's structural integrity. Click this link to see another photo of rust on the base of a steel column in a basement that we verified over a 12 year life had been subjected to recurrent wet floors but never flooding.
Comparing Surface Rust to Significant Exfoliating Rust on a Structural Column
But when we see exfoliating rust, some careful poking around to see just how much damage has occurred can help us decide the urgency of replacing the column - and of course fixing the water entry problem . WATER ENTRY in BUILDINGS will help with the latter.
Example of Structural Steel Column Collapse Due to Rust
At below left we show serious exfoliating rust at the base of a steel column. It's reasonable to infer that this home has been subject to recurrent flooding to a depth of several inches.
Our second structural rust photo (above right) was very exciting. We were inspecting a house on Long Island when the owner mentioned that she had pumps running 24/7 in the basement to keep Long Island Sound at bay. There was a forest of steel supporting columns (some were just hollow pipes not real Lallys) in this home's basement - all were badly rusted.
As the owner, who was a big person, walked across the floor, the kitchen floor suddenly collapsed and fell down about a foot. We wondered if an earthquake had suddenly struck Long Island.
Trembling we both took another look in the basement. The Lally column shown above and supporting part of the kitchen floor had picked that moment to crush. It was rusted through from repeated flooding.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.