Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
VENTILATION in BUILDINGS
AIR BYPASS LEAKS
AIR LEAK DETECTION TOOLS
AIR LEAK SEALING PROCEDURE
AIR POLLUTANTS, COMMON INDOOR
AIR SEALING STRATEGIES
BASEMENT CEILING VAPOR BARRIER
BASEMENT HEAT LOSS
BASEMENT LEAKS, INSPECT FOR
BLOWER DOORS & AIR INFILTRATION
BRICK WALL DRAINAGE WEEP HOLES
CATHEDRAL CEILING VENTILATION
CEILINGS, DROP or SUSPENDED PANEL
COMBUSTION AIR for TIGHT BUILDINGS
COOLING LOAD REDUCTION by ROOF VENTS
CONDENSATION on WINDOWS & SKYLIGHTS
DEW POINT CALCULATION for WALLS
FIREPLACES & HEARTHS
FLAT ROOF MOISTURE & CONDENSATION
GREEN BUILDING CONSTRUCTION
HEAT LOSS in BUILDINGS
HEAT LOSS DETECTION TOOLS
HEAT RECOVERY VENTILATORS
HOT ROOF DESIGNS: UN-VENTED ROOF SOLUTIONS
HOUSEWRAP AIR & VAPOR BARRIERS
HOUSE DOCTOR, how-to be
HUMIDITY LEVEL TARGET
ICE DAM LEAKS
INDOOR AIR HAZARDS TABLE
INDOOR AIR QUALITY & HOUSE TIGHTNESS
INDOOR AIR QUALITY IMPROVEMENT GUIDE
INSULATION AIR & HEAT LEAKS
INSULATION INSPECTION & IMPROVEMENT
INSULATION R-VALUES & PROPERTIES
LOG HOME GUIDE
MOISTURE CONTROL in BUILDINGS
ODORS GASES SMELLS, DIAGNOSIS & CURE
ROOF VENTILATION SPECIFICATIONS
ROOF ICE DAM LEAKS
SHEATHING, FOIL FACED - VENTS
STAIN DIAGNOSIS on BUILDING INTERIORS
STUCCO WALL METHODS & INSTALLATION
SWEATING (CONDENSATION) on PIPES, TANKS
THERMAL MASS in buildings
THERMAL TRACKING Indicates Heat Loss
VAPOR BARRIERS & AIR SEALING at BAND JOISTS
VAPOR BARRIERS & HOUSEWRAP
VAPOR CONDENSATION & BUILDING SHEATHING
VENTILATION in BUILDINGS
WIND WASHING INSULATION At EAVES
WINDOWS & DOORS
This roof ventilation and ice dam leak prevention article compares Two Identical Houses, With and Without Roof Ventilation and Insulation to Understand Attic Moisture Problems. Both homes, located in "the Bleachery" in Wappingers Falls, NY were built in the late 1800's overlooking Wappingers Lake.
This article is part of our roof ventilation & attic condensation article series. These articles describe inspection methods and clues to detect roof venting deficiencies, insulation defects, and attic condensation problems in buildings. It describes proper roof ventilation placement, amounts, and other details. The photograph at page top shows the author's introduction to roof ice dams at 25 King Drive in Poughkeepsie, NY in 1970.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Comparing Two Identical Houses, With and Without Roof Ventilation and Insulation to Understand Attic Moisture Problems
One of these pre-1900 homes (at below left) was renovated by the author (DJF) to include effective soffit intake and ridge exhaust under-roof venting along wtih insulation and air leak sealing throughout the structure. The second home (below right) had a drafty attic that had avoided attic condensation and moisture troubles but the design sucked so much heat out of the home in winter that combined with little attic insulation the house suffered from extensive ice dam formation.
On two identical 1860's Wappingers Falls NY "Bleachery" historic houses shown in these photos, the one with no melted snow was renovated to include continuous soffit and ridge venting and good attic insulation.
[Click to enlarge any image]
These homes, located on West Street in the village of Wappingers Falls, New York, were built to house workers at nearby mills powered by water from Wappingers Creek.
At left you can see the same two homes on a different winter day. The home on the left was the one to which we'd added attic insulation and under-roof venting. The home on the right has so much heat loss through the roof that it is completely free of snow.
When the homes were built they lacked central heating, storm windows, siding, caulking, and insulation. They were drafty. Interior moisture and condensation were less likely to damage the structure than today, nearly 130 years later, when the energy improvements listed have been added to the homes, making them tighter but also providing indoor moisture sources such as from bathing or cooking.
In renovating the left-hand home we removed solid blocking between rafters at the house eaves, allowing perforated soffit covering to send air in at the eaves.
Adding a ridge vent completed the air intake-outlet scheme. Insulation was placed in the attic floor and we used baffles to be sure that we kept an air path open at the house eaves.
It was important to contine the attic floor insulation out over the top plate to avoid a heat loss point that would have invited icing over that area.
Photos of of Ice-damaged Roofs & Leaks into Building Walls Indicate Where Roof Ice and Ice Dams are a Problem
This glass solarium suffers from ice build-up during most winters.
The ice action led to damage to the glass seals, resulting in leaks into the building.
If a roof shape prevents easy installation of under-roof venting, or if a home is located where building custom excludes under-roof venting, use of an ice-and-water shield product under the shingles at roof edges, or use of metal covering the lower roof slopes are other measures taken to prevent ice dam leaks into the building interior.
See UN-VENTED ROOF SOLUTIONS for a discussion of how we prevent leaks into roofs where venting is difficult to achieve.
In our next photo below you can see examples of leaks into building walls caused by roof ice dams and water back-ups behind the dams that leak into the building soffits and walls. It can be hard to spot this problem in warm weather, but freezing weather, by forming ice at wall leak points, adds actual ice to the clues.
In warmer weather when there is no snow or roof ice there are still clues indicating leaks into building walls. From outside look for stains or for water tracks down walls subject to water damage from roof leaks or roof ice dam backup leaks. Inside be alert for mold complaints and hidden mold reservoirs.
Loss of insulation R-value due to wet wall insulation also shows up on thermal scans if the insulation is still wet.
The house whose roof shows melted snow and bare roof slates (beware of nasty owner) has inadequate venting and inadequate insulation, giving rise to snow melt and ice damming, and almost certainly to attic condensation and moisture.
After these vents were added we also closed-off the gable end vents (not shown) to assure that airflow moved over the desired pathway.
The builders of this house had blocked the soffits with boards on edge between each rafter pair in an effort to "warm up" the cold attic. We removed these blocking boards to assure a proper airflow.
Global warming and building ice dam leaks? Venting of roof cavities helps reduce the effects of hot weather associated with global warming
In a 1996 version of this article in the Journal of Light Construction we paraphrased Stephen Jay Gould, a Harvard scholar who said "The world is currently enjoying a brief warm spell in the midst of a basically cool period.
Gould said that the glaciers that covered our region might return in another 10,000 years or so. We added that the sheets of ice we see creeping down buildings in freezing climates are not due to global freezing but due to poor building ventilation and insulation.
That conservative view of climate change has since proven to be mistaken, as very rapid global warming is, in 2008, a fact accepted by virtually every qualified scientist. But global warming does not mean that we can blithely ignore attic ventilation. Not only will the risk of ice dam leaks continue to occur on poorly-insulated and poorly-ventilated building roofs, but more, the benefits of proper under-roof ventilation are present in hot weather as well.
A properly ventilated building roof cavity or attic means that the roof surface as well as the attic will be cooler in hot weather, reducing indoor cooling costs and extending the life of the roof covering.
Continue reading at ROOF ICE DAM PREVENTION at SKYLIGHTS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References