Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER CONSERVATION MEASURES
WATER CONTAMINANT LEVELS
WATER FILTERS, HOME USE
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PUMP REPAIR GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMP SHORT CYCLING
WATER SOFTENERS & CONDITIONERS
WATER TANK REPAIR PROCEDURES
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WELL CHLORINATION & DISINFECTION
WELL FLOW RATE
WELL WATER PRESSURE DIAGNOSIS
WELL YIELD IMPROVEMENT
WINTERIZE A BUILDING
This article explains how to Diagnose and Cure Bad Water Pressure Due to Clogged Water Supply Pipes - how to diagnose the loss of water pressure and the need for a replacement water pressure tank and water pump. The process of diagnosis and the costs of the repair are explained. Consumer advice on saving money on well repair costs includes a review of the parts and labor costs of a typical well pump and pressure tank replacement case.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Clogged water supply piping can cause poor water flow in a building. This can occur suddenly from debris clogging a delivery pipe, often at a turn or "elbow" in the piping, but that's not common.
[Click to enlarge any image]
If the building water supply piping is blocked usually this is a long-standing problem.
Examples of causes of poor water pressure due to blocked pipes include
The sketch (above left), courtesy of Carson Dunlop Associates shows how galvanized steel water supply piping becomes clogged from rusting or mineral deposits.
Also see WATER PRESSURE LOSS DIAGNOSIS & REPAIR in a building
If only hot water pressure and flow are poor, also see CLOGGED SUPPLY PIPES, HOT WATER.
There are two useful diagnostic tricks to determine if building water piping is clogged:
A main water supply pipe failure between the municipal water main in the street (or from a private well) and water supply pipes in the building the building, can occur, perhaps by leaking or by becoming clogged with rust or minerals so that water is not being delivered to the home at good pressure or not at all (if the water line has burst).
In cold climates, the water supply line may have frozen outside or even in the building at an un-heated location.
Next see Water pipe clog repair guide. or select a topic from the More Reading links shown below.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: could repairs by our plumber have caused a considerable water pressure decrease
(May 22, 2012) Anonymous said: Had a leak under the kitchen sink...under the subfloor from the sink. had a plumber replace a section of pipe. There was an additional leak from the outside spout that tied into the plumbing that the plumber fix so he cut that line he couldnt get access to the leak, so he added another outside spout and tied it into where the kitchen sink plumbing was located. a few weeks later, we noticed if you turn on the outside water, the water prressure in the house drops to where the water is barely running. What could this be? Could the plumber tied into the wrong pipe that would cause a considerable pressure decrease?
It's not uncommon for water pressure in a building to be weaker at a second or third fixture if one or more others are running. If we run water from a spigot that is close to the water supply source - say the pressure tank - it may cause a larger perceived pressure drop at more remote fixtures in the home - it's as if the pressure finds a close easy relief point. I'm not sure what "wrong pipe" might be or how that would make a difference.
However a plumbing repair indeed can cause reduced water flow rate (which people refer to as water "pressure") downstream from the repair work if the plumber pushed too much solder into a joint, blocking the pipe interior.
Question: no water pressure to certain fixtures
(June 23, 2012) Valiangel said:
I have no water pressure to my outdoor hose and my washing machine which are both located in the rear of the house. I'm thinking it's the iron piping there, but not sure. My outdoor hose has only a trickle of water, and my washing machine has slightly more water pressure....Is there any way to determine if I'm correct?
Valiangel I think you might do better by reviewing WATER PRESSURE PROBLEM DIAGNOSIS TABLE - article linked to near the end of this page.
Question: poor water pressure if I run more than one fixture at a time
(July 29, 2012) annonymous said:
Please help, for years now my water has been terrible, if i use 2 or more fixtures at one time i lose water from all fixtures say if i flush the toilet and i am running the bath taps the bath will have a trickle of water or if the washer is on and i turn on another tap i will only get a trickle of water but just lately i have noticed that even running one tap will run normal then almost stop or stop completely. Is this due to neighbours sharing water? I live in a mid-terraced house.
Anon there are more water pressure improvement suggestions at WATER PRESSURE LOSS DIAGNOSIS & REPAIR
You want to determine if the problem is piping (see the article starting at the top of this page) or if it is a system pressure problem, or a water supply problem from a well or municipal supply. That first step will help direct the choices you can make to improve things.
Question: company comment on using VacuFlow™ vacuum sewage systems
(Sept 7, 2012) rickyyd12 said:
Vacuflow is the trade name for a method for the continuous piped disposal of sewage, utilizing the energy of atmospheric pressure by creating a vacuum in the piping system (a vacuum sewage system)
For rural or seaside areas with circumstances as hilly or flat terrain (high water table) it means that the natural fall on which gravity systems depend must be created artificially, the Vacuflow system is the alternative.
Why you posted this at our article on poor water pressure remains a mystery.
Question: waste water line is blocked, how do I clear it?
(Nov 8, 2012) unika said:
i am getting problem with waste water supply pipe, i dont know where it is block so i need help how to clear the waste pipe....due to this my washing machine is not working properly and when i used washing machine the water flow out in sink.....can you please suggest me what liquid does work in such a problem?
Please see CLOGGED DRAIN DIAGNOSIS & REPAIR -
to see how to diagnose and fix the waste pipe problem you described
Question: lost water pressure, just rickling, what product should I use to fix it
(Nov 22, 2012) Anonymous said:
The fresh water pipes into our property seem to have lost pressure and the water is just trickling. What can be done about this and what products should be uses.
Anon, before using an y "product' to improve water pressure we need to figure out why pressure is poor - lack of water, clogged pipes, bad pump, failing well, bad pressure regulator, etc. See WATER PRESSURE PROBLEM DIAGNOSIS TABLE
Question: son broke outdoor pipe, now poor indoor pressure
(Nov 24, 2012) Michael l. said:
My son stepped on a water sprout in the backyard and I had to just cap it.now we have low water pressure in the house and one restroom there's no running water from the sink or shower. What causes this and what do I do?
I think the next think I'd check is for a broken and leaking water pipe underground where your son stepped on the outside line.
Question: broken water main was repaired, but now we have low in house water pressure - why?
(Nov 26, 2012) krisstime said:
our watermain broke in our driveway, which blew our water meter apart. sand and debri was flowing towards the broken water meter. Now we extremely low water pressure in the house. Pressure seems fine to the house, but nearly none inside the house. city refuses to take blame so we are attempting to fix ourself. found sand in our toilet. where should we start looking for the blockage? was told there is a screen suppose to be buried by the front hydrant, but cannot seem to locate that
Perhaps sand and debris have clogged house piping; certainly if you found sand in the toilet that's strong evidence that a LOT of sand and debris has entered your water piping.
The fix, which will be troublesome, is going to involve lots of draining & flushing, including
- water heater tank
Perhaps you can get the city to agree to excuse the charge for water waste necessary to flush out the whole system.
Question: bad water pressure just in the kitchen
(Feb 8, 2013) Susan said:
all my water pressure is great in my house,except for my kitchen. for the past few yrs. my faucet will start out shakin a bit,before water flows,then the flow decreased,over a period of several moths,until it finally stops completely,i replace the faucet,and the process repeats itself all over again, and it is only in my kitchen. does anyone know what this can be,and how i can fix it permanently?
Susan most likely a valve, supply pipe elbow, piping itself, or perhaps a faucet strainer are clogged and need to be cleaned, repaired, or replaced.
Question: good pressure outside, bad water pressure inside after well pump replacement
(Mar 3, 2013) Anonymous said:
I had to replace a well pump. I'm getting good pressure at the pump and the water on the outside spicket runs good. But the cold water inside the house runs really slow (no pressure)Hot water runs good. checked all screens they are clean. I did have some black sand come out of the Faucet but screens are clean. I'm thinking some sand or dirt is blocking the water flow in the pipes somewhere in the line. How would I clean or clear this out. I was thinking cut the pump off, open the outside spicket hook up an air supply to the faucet on the inside and blow the water, dirt and thin the air out of the outside spicket. If anyone has a better idea, PLEASE HELP THANKS
Anon, look for debris clogging at the indoor plumbing system, starting at a water filter or at the pressure tank.
Question: why doesn't water already in the water heater tank come out to fixtures even if the main water supply is off?
(Feb 3, 2014) Anonymous said:
Why doesn't the water that is already in the hot water heater come out to the fixtures (after main water supply line is not supplying any water at all due to: busted underground or completely clogged/blocked)?
Anon: in normal residential hot and cold water piping systems, if there is no water pressure on the cold water input line to a water heater, no hot water will flow out of it into the building when hot water is turned on at a fixture. Incoming cold water pressure is what pushes hot water pressure out of the heater and on to building plumbing fixtures.
Question: why can't I clean clogged water supply pipes with a drain auger?
(Feb 3, 2014) Anonymous said:
Why wouldn't 1/4" augur fit into 3/4" piping?
Anon: given the length and turns in building piping, I'm doubtful that using an augur will be effective in removing clogging due to mineral deposits or corrosion throughout the system. Even if you could gouge out corrosion the resulting thin pipes probably have a very short remaining life.
Question: how do I improve water pressure at a higher building location?
I have a wr60 pressure tank near lake being fed by submersible pump. Settings are 40/60 and tank pressure is 38 psi. There is a second pressure tank approx 600 feet away up a hill in the house.
The air pressure in this tank is set at 38 psi. There is never any water entering this tank .the water pressure reading at this tank is 34 psi which I believe is the line loss from the 60 psi reading down at lake. Can the cause of no water in this tank because the air pressure is higher than water pressure . Can I lower air pressure to 32 psi.
Eddie you give horizontal distance but not vertical distance between the two tanks - that height is a factor to consider
. But if absolutely no water is entering the upper tank, other explanations include that water pressure is not high enough to lift water the height distance between the tanks or the tank is an internal bladder type and the bladder has stuck to itself.
Our illustration shown here and discussed in our article WATER PRESSURE BOOSTER PUMP shows that if incoming water pressure at ground level were at 60 psi, at a building plumbing fixture that is 30 feet higher the effective pressure would be around 47 psi.
Quoting from that article
Questions & answers or comments about clogged water pipes and their effect on water pressure
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Water Supply & Drain Piping, Wells, Pumps, Water Supply Equipment