Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
Ask a Question or Search InspectAPedia
InspectAPedia ® Home
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER CONTAMINANT LEVELS
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PUMP REPAIR GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMP SHORT CYCLING
WATER SOFTENERS & CONDITIONERS
WATER TANK REPAIR PROCEDURES
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WELL FLOW RATE
WELL WATER PRESSURE DIAGNOSIS
WELL YIELD IMPROVEMENT
WINTERIZE A BUILDING
This article explains how often to add air to a building water pressure tank, and how to detect and correct air and water leaks in a building water supply system where a private well is the water source.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
Frequency of Adding Air to Bladderless Steel or Fiberglass Water Tanks
When your water tank is a conventional older style that does NOT use a "captive-air" type bladder, unless there's a leak at the water tank you shouldn't have to add air again for months or maybe even a year.
The frequency with which you'll need to add air depends mostly on how much water is used.
Eventually air in this older type of tank gets absorbed into the water, losing the cushion effect and generating a need for more air.
Frequency of Adding Air to Captive-air Bladder-type Water Tanks of Steel, Plastic, or Fiberglass
Captive-air or bladder type tanks should never need air added. If you keep having to add air to a bladder-type tank something is wrong with the system, perhaps a torn or leaky water bladder in the tank or a leak in the steel tank body that is losing air.
The pressure tank's internal rubber bladder contains water, the steel tank body contains the air charge.
Key Water Tank Air Charge or Waterlogged Water Tank Diagnosis & Repair Articles
There are fancier methods than those described below but here are three simple methods, of which the second two work well for easy replacement of air lost from a bladderless or glass-lined steel water storage or pressure tank.
Bladder type or "captive air" water tanks do not normally need to have makeup air added but if you are finding short cycling on a bladder-type water tank system, if the problem is not in the pump control or water piping, the problem may be traced to a failure of the internal bladder itself - a component that may be replaceable. In that case adding air to the bladder type water tank won't correct the problem.
Readers of this document should also see Water pump and pressure tank repair diagnosis & cost an specific case which offers an example of diagnosis of loss of water pressure, loss of water, and analyzes the actual repair cost. The illustration at page top is courtesy of Carson Dunlop, Inc. in Toronto.
Frequently Asked Questions (FAQs)
Questions & answers on how often you should add air to a water pressure tank
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.