Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER CONSERVATION MEASURES
WATER CONTAMINANT LEVELS
WATER FILTERS, HOME USE
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PUMP REPAIR GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMP SHORT CYCLING
WATER SOFTENERS & CONDITIONERS
WATER TANK REPAIR PROCEDURES
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WELL CHLORINATION & DISINFECTION
WELL FLOW RATE
WELL WATER PRESSURE DIAGNOSIS
WELL YIELD IMPROVEMENT
WINTERIZE A BUILDING
This article describes How to Repair a Water Pressure Control Switch that Sticks "ON" or "OFF" or is irregular in cycling on and off.
In the sketch above the water pump pressure control switch is item #4 - we show this switch in more details in photographs provided below.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
This article explains inspecting, cleaning, and possibly repairing a typical Water Pump Pressure Control Switch, normally found mounted on piping at the water pressure tank such as in this example where you see a small gray-covered box with electrical wires coming in (power) and out (to pump) of it.
The details of how to remove and replace a well pump pressure control are at PUMP PRESSURE CONTROL REPLACE for reinstalling the control.
The water pump pressure control switch either turns on the water pump directly, or (particularly when a submersible water pump is in use), this switch may operate a physically separate (usually wall-mounted) heavier-duty pump relay which turns on the water pump itself.
See WATER PUMP RELAY SWITCH for more details of that control.
If the water supply is high in sediment often sediment will clog the pressure sensing opening at the bottom of the pressure control. We've tried cleaning out this orifice but it's never proven to be a lasting repair. If your pump pressure switch stops responding to changes in water pressure it probably needs to be replaced.
How to Diagnose and Repair a Water Pump Pressure Control Switch that Sticks "on" or "off" or is misbehaving
If we’ve traced a pump control problem to the water tank or water pump pressure switch itself with some certainty, we will often just replace the switch. But beware, we once replaced a pump control switch when the problem was a clogged filter which was causing the pump to cycle on and off erratically. We felt pretty stupid.
How to Diagnose a Malfunctioning Water Pump Control Switch
We’ll need to do some water pump switch diagnosis – here are a few ideas that may help getting a recalcitrant pump control switch working again.
Watch Out: Safety warning - Shock Hazards: To remove a pump control/pressure switch remember to turn off electrical power, and using a neon tester or VOM double check to make SURE that electrical power is off, and taped-off so that on one turns it on and causes you to get shocked. Working around electricity and plumbing is particularly dangerous because of the increased chance of touching a live electrical wire while touching grounded plumbing piping.
A pump or water tank pressure control switch is designed and adjusted to turn the pump on at a "cut in" pressure, usually 20 psi or 30 psi, and to turn the water pump off at a "cut out" pressure, usually 40 psi or 50 psi. When you buy this control it is usually set at the proper cut-in and cut-out pressures - check the box.
If your pump control is properly adjusted (See WATER PUMP PRESSURE CONTROL ADJUSTMENT ) then it should be turning the pump on and off nicely at the pre-set pressures. If the switch is behaving erratically or not coming on or not shutting off at all, there could be various explanations, some of which have nothing to do with the switch itself.
These other problems are discussed at WATER PRESSURE LOSS DIAGNOSIS & REPAIR
and WATER TANK REPAIRS.
If your well pump won't stop running, you should probably turn it off to avoid burning up the pump motor. Causes of continued pump operation include lost water supply in the well, well piping leaks, well pump defects, or an improperly-adjusted pressure control switch that has called for higher water pressure than the pump can achieve.
If the water pump will not turn OFF, see WATER PUMP WONT STOP RUNNING
Look at the water pressure gauge reading.
When pressure is below the water pump control cut-in pressure:
So your gauge could be wrong. (You can purchase or make a water pressure test gauge that connects to a hose faucet anywhere in the system if you want to double check for this problem.)
When the water tank pressure gauge reading is above the water pump's "cut-in" pressure (say 32 psi as we show in the photo below), don't expect the pump to turn on.
Tap on the water pressure control switch
If the water pressure gauge stays low (below the pump; cut-in pressure, try tapping on the side of the pressure control switch housing itself. Don't bang it with a hammer, just tap it.
If the pressure control relay switch closes and turns on the pump after you tap on it but if it otherwise sometimes "sticks" in the "off" , there's probably a problem with the pressure control. It could be a dirty or burned electrical contact, a loose electrical connection, or debris clogging the diaphragm of the pressure sensor (or something else we haven't thought of).
Tap on the water pump itself
If the pump is accessible we might give it a smart rap with a small wrench. Don't bang it with a hammer. Just as a connection in a pressure switch may be loose or dirty or bad, the same could be true of a pump motor. If tapping on the water pump makes it start, it needs repair or replacement.
Some pressure control switches include a metal lever along one side of the switch. Lifting this lever from its horizontal (off) position upwards towards vertical (on) position, will "force" the pump switch to turn the water pump on.
In our pump control drawing (left) the red arrow points to a pump pressure control switch bypass lever. Most pump pressure control switches do NOT have this feature, however.
Provided that you also have electrical power at the switch, the well pump should turn on if you lift this lever. Some manufacturers such as Square-D call this the "Maintained Manual Cut-in Lever or Manual Cut Out Lever" (depending on the switch model and application). "Manual cut in" means that lifting the lever will turn on the pump.
Watch out: Do not leave the manual cut-in switch on (up). Turn the switch back off and proceed to diagnose why the switch was not turning the well pump on and off automatically.
If your well water is high in iron, sediment, or minerals, we find that sometimes the small diameter pipe that mounts the pressure control switch onto the water line, water pump, or water tank will clog with these materials. In the photo at left I'm pointing to the pressure control switch.
You can see the small diameter mounting pipe that connects the bottom of this pressure switch to the building water supply piping right at the bottom of the water tank. Other pressure control switches may be bolted right to the pump motor and may use a flexible plastic or copper tube to transmit water pressure to the switch.
If this pipe (usually ¼” or 1/8” IPT diameter) is clogged with debris, you might be successful in getting the pressure control switch working again by removing the control switch, confirming that the line is packed with debris, and replacing it.
In our experience often when there is enough debris to clog the pressure control switch mounting pipe then the same debris also clogs the still smaller opening in the bottom of the pressure switch itself. It’s this small opening that permits water to press against a diaphragm in the bottom of the pressure switch and thus allows the switch to sense the water pressure.
Debris can clog the tubing connecting (or mounting) the pressure control switch to the water tank or water piping, preventing the pressure switch from responding properly to changes in water pressure. The result may be intermittent failure of the switch to turn the pump on or off, or it may result in a hard failure to turn the pump on or off.
Our photo (left) shows a copper tube running from a two-line jet pump (photo center) to the bottom of a pressure control switch (the gray box at lower left). This is the tube that carries water pressure (pressurizing air in the tubing) to the bottom of the pressure control switch.
Pressure Control Switch Tubing Clogging
Clogging of the Water Pump Pressure Control Switch if your water has a high level of silt, debris, or minerals, it's possible
that the tubing or piping connecting the pump pressure switch to the pump or water piping, or the pump switch bottom orifice through which the pressure switch senses the water pressure in the system has become clogged.
The small diameter of this tubing and still smaller diameter of the pump switch orifice makes clogging easy if your well water is high in sediment or minerals.
On rare occasions we can tap on the well pump control switch and it will begin working again, but not for long, and not reliably. Another water pressure control switch failure is the rupture of a rubber disk or "bladder" inside the switch itself. If you detect or suspect a defective pressure control switch, try replacing it with a new one.
We see a similar problem affecting water pressure gauges on private water systems: debris or mineral deposits can clog the pressure sensing orifice on the water pressure gauge, causing it to fail to respond at all, or to respond inaccurately to changes in water pressure.
When we find a clogged water pump pressure switch or the tubing connected to it, or a clogged water pressure gauge, we replace those items. A well pump pressure gauge that does not respond to pressure changes is potentially unsafe as it could lead to excessive pressurization of the water tank and building piping.
Pressure Control Switch Tubing Leaks
Thanks to reader Bob Hartman-Berrier for explaining a more subtle problem with pressure control switch tubing - wrong (too-small) diameter, causing a leaky fitting, preventing the pressure control switch from properly responding to changes in water pressure.
The tubing connecting a pressure switch may be steel (a rigid small-diameter mounting pipe), flexible copper (connected with flare fittings), or flexible plastic (connected using special brass connectors. Changing the tubing, especially plastic tubing, can get cause trouble.
Mr. Hartman-Berrier diagnosed this problem by observing that the pressure control switch would turn the water pump on if the override lever on the pressure switch were moved to the "on" position, but otherwise the switch did not work. The pressure switch was not turning on the water pump even though the water pressure was below the "cut-in" pressure setting. Because the pressure control switch was a new one, investigation eventually turned to a possible problem with the plastic tubing connecting the switch to the water tank.
Watch out: your water pump might have two tubes running from the pump body: one tube carrying pressure to the pressure control switch, and a second, similar-diameter tube that is connected between the pump body and an air volume control. AVCs are discussed at WATER TANK AIR VOLUME CONTROLS.
How to Check the Bottom of the Pump Control Switch for Clogging
If as long as we’re taking the switch off to check these things I’d check out that opening on the switch bottom as well. We do this by unscrewing the connecting pipe from the bottom of the pressure switch, and looking inside of the opening into which that pipe was connected.
In a pinch it’s good to know that you may be able to clean the water pump control switch right up and get it working again.
Be careful about poking anything into the threaded opening which connects the pressure switch to the water pump or water tank. It's tempting to just jam a paper clip into the little sensor hole and wiggle it around. But if you puncture the switch diaphragm you'll certainly need a new switch. (You probably need one anyway if you see a lot of crud in there.)
It's possible to remove all of the phillips-head screws you see in this photo of the underside of a pump pressure control switch, to expose the diaphragm, and to clean out the whole mechanism. Don't tear the diaphragm
Since a new pressure switch is not very costly, and since we have to take the switch off to diagnose it anyway, if on removing and inspecting the pump pressure switch we think it was clogged, I’ll often just replace it.
Check the water pump pressure control switch for dirty, burned contact points:
If the pump pressure control switch contacts are burned we can sometimes get it working again for a while by first, turning off electrical power as we described above, and then using a file, carefully cleaning all touching-surfaces the switch contacts.
A file may produce less grit and debris in the switch than sandpaper.
We sometimes use fine sandpaper anyway, but in either case be careful not to leave grit and debris in the switch or it’ll fail again that much sooner.
If after inspecting the pump pressure control switch or its mounting fittings you decide that you've repaired it or that you need to replace it, follow the instructions at PUMP PRESSURE CONTROL REPLACE for reinstalling the control.
Watch out: do NOT try working on a pump control switch without first removing electrical power - you could be killed by electrical shock.
Causes of burned pump pressure control switch contact point surfaces include:
If the pressure control contact point surfaces are burned, it may interfere with the pump turning on. While it is possible to clean or even file these surfaces to get the switch working again as an emergency temporary fix, the switch needs to be replaced. While we have heard a report of the pump pressure control switch failing to turn "off" blamed on burned contact points, we think that when a pump won't turn off other causes are more likely.
A Guide to Building Water Pressure by Adjusting or Repairing the Water Pump Pressure Control Switch
Continue reading at WATER PUMP PRESSURE CONTROL REPLACE
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: well pump tank makes a noise after tank begins to fill
(June 28, 2011) elmer said:
Is a good article but i still with my question because i did not find the answer . My well pump tank make a noise after the tank begins to fill again?..The pressure control works fine.
It might be normal to hear a noise at the pressure tank when the pump is running, as water is flowing into the tank. If you hear air gurgling then there may be a leak in your well line causing the pump to also send air into the tank.
Question: pump control relay clicks clicks clicks at end of cycle
(July 19, 2011) carter said:
i have a question,,i have a new installed jet pump...6 months,,when i flush my toilet my pump will run for maybe 20/30 seconds,,,it runs fine,,but when its right at the end,,the pressure points will snap on and off right fast 3/4 times,,i adjusted the screw and it worked good for a day now its doing the same thing,,,,runs smooth until right the end,,,then click,,click,click,,
Pump pressure control switch contact bouncing?
It sounds as if the contact switch points may be burned; take a look, or try replacing the switch. I am guessing in that direction because at the end of a pump cycle even if the pressure sensor of the switch is not working properly I wouldn't expect pressure sense to drop so far as to fall below the cut-in right at the END of the pump cycle.
Question: pressure drops to zero and pump stops unless manually re-set
(Aug 30, 2011) Janice said:
I have a question. We have a pressure control switch lever (as shown above) that we need to re-gauge if we run two faucets (or demand too much water) at one time. The pressure will drop to zero and we need to engage it in order to get the water working again. Any suggestions on what would be causing this? This also happens if we run the faucet in the tub or the washer. Thanks!
Janice if your water pressure is dropping to zero, the problem sounds like more than just adjusting the pressure control switch. It sounds as if the well pump is not keeping up with the water flow rate demand in the building. Or your well itself cannot keep up.
Before trying to adjust the pressure control switch I'd check out the well flow rate itself.
Question: pressure drops below the pump cut-in set pressure before the pump comes on
(Sept 5, 2011) Jim said:
I've adjusted cut on and off pressures, etc. My problem is that when the pressure drops through the cut in point, the switch "tries" to trip. The contacts close briefly, pump just starts to turn, then everything stops and pressure falls. I can start it with the manual switch and it will run fine . Pressure tank is brand new, and adjusted to about two pounds below cut in pressure. Any ideas?
(Oct 18, 2011) Kerry said:
Pressure control switch isn’t turning on the pump - when using the manual cut in switch the pump isn’t turning on either, however, if you manually use a screwdriver and push the contacts down you can get the pump to engage. hold the contacts down and you can get the tank up to pressure, however as soon you run out of pressure you have to go down with your screwdrivers and get the pressure back up
Reply: check for a debris clogged pump pressure switch or sensor port or tubing
it's possible that the pressure sensing port on the bottom of your pressure control switch is clogged and not properly sensing water pressure. If the switch thinks that you are above the cut-off pressure it won't turn on the pump. Another possibility is that the switch contacts are burned.
I'd try replacing the switch and making sure the little tube on which it mounts is also unblocked by rust or debris.
Question: pump came on for just 10 seconds
(Oct 21, 2011) Andrew said:
I have a relatively new Gould. Today I noticed the pressure was not right then it finally had no pressure. While in the pump house I re-booted the power. The pump came on for about 10 seconds and then shut off again. Again, I said it is about 3 1/2 years old and all the contacts I looked at look like the day it was put in. What is the most likely problem ? Pressure control switch - capacitor etc... Thanks for your help
(Jan 12, 2012) warren said:
my presure switch is tapping on/off on/off when i turn my tap on. what could be the cause?
Andrew check the actual pressure in your system, then run water. Watch to see the pressure at which the pump cuts on. Then turn off water and watch to see the pressure at which the pump cuts off.
If the pump cuts off very quickly I suspect the water tank is water-logged - it's lost its air charge.
(Feb 13, 2012) Rob said:
@Warren - two things come to mind that can cause that (as I just had the same problem). A bad pressure tank can cause your pump to kick in and out repeatedly while running water. The other potential problem is the setting on the pressure switch itself. If the in and out are too close it would cause this. If you haven't adjusted your pressure switch I would check the air pressure in your tank. If you press the valve down and get water, then you've most likely got a ruptured bladder in your tank.
Question: testing my pump switch I saw a spark, then everything went dead - how do I select a new pump switch
(Jan 11, 2012) Steve said:
Square D 9013FSG 2 pressure control switch. While testing with a VOM probe, I got a small spark and everything went from dead to working normally (I think...at least the water is back on). If I eventually need to replace this switch, are there several varieties of the 9013FSG 2? How do I know what version to get? The tank is a red AMTROL H20W-TO WATERWORKER 9015-585 in a residential installation.
Steve, just match the new switch to the original one by
brand and model or part number
equivalent brand and model chosen by the factory pre-set cut-im and cut out pressure
Question: new pressure switch not working
(Jan 12, 2012) Archie said:
just repaced breaker, wire, pressure regulator switch on home well pump and still nothing works. I checked the gauge tube for clogs and it was clear, when I open the contact points, there is no spark, but there is power going to them, what am I missing
Archie, you need to run water until pressure in the pressure tank drops below the cut-in pressure set in the control.
Question: pump runs, cuts off normally, then pressure suddenly drops from 30 to zero
(Jan 23, 2012) kevin said:
hello, i just replaced my guage, my 30/50 switch, got my air pressure in my tank to 28psi. my pump runs and then cuts out at 50psi. I turn my water on and watch my guage. When the pressure get to 30psi, it hovers a second then plummets to 0. I never here my pressure switch click on at 30. Please help, any ideas?
(Apr 30, 2012) John said:
Hello, I just moved into a new house and my water will be running fine then all of a sudden I will have none. I checked the pressure tank and found that if I move the Maintained Manual Cut-in Lever or Manual Cut Out Lever I will get my pressure and water back. This seems to happen at random and I was wondering if this was likely to be caused by a bad pressure control switch?
(May 28, 2012) Jon: said:
I have my well set at 60/40 .. Turns off at 60 I turn on water when it gets to 40 elec. turns on but after a few seconds it drops to 0 . Water trickles out. Can you help me with this problem
John and Kevin: the sensor port on the bottom of your pressure control switch may be clogged - try replacing the switch and the mounting tube as well.
Try first checking system water pressure at an independent location using a test gauge at a nearby hose bib. Tell us what you see.
Question: well pump would not stop - problem traced to clogged well screen
(May 2, 2012) Denis(satisfaction) said:
I had a pump that would not shut down...this site allowed me to go through each possible potential cause and after a few visits to the site and about 2 hours I pulled the 1/2"stone out of the internal injector screen and we have water. Thanks a million. Happy Wife Happy Life!:)
Nice going Denis.
Indeed without a more sophisticated well pump controller that monitors current draw, we can't tell the difference betweeen a well that has run out of water and a well whose foot valve screen has become debris clogged, not allowing water to enter the pump.
Question: pump cycles on and off right at the cut-out point
(June 12, 2012) matt said:
what would make the needle on the pressure gauge bounce badly enough to turn the pump off then on 2 or 3 times at the shut off point
A clogged sensor port on the bottom of the pressure control switch can cause the problem you describe.
Also check for burned contact points on the pump relay. If you see burned relay contacts replace the switch.
Question: do I pre-pressurize the empty water tank air charge or add water then air pressure?
(June 12, 2012) Anonymous said:
ihave a 30/50 switch so i need 28 psi in the water tank. do i put the air in at 28psi on an empty tank of water or add the water then try to add air up to 28psi?
if you are setting air pressure in a water pressure tank in the range you describe, the assumption is that the tank has been emptied of water.
On most pump and tank systems if the water tank is a bladderless system and if the air charge is too low, you can add air after water is in the tank as well. Just watch the gauge. If you add too much air typically the excess air will flow out at the nearest faucet when you next run water.
Question: well pump won't get above 10 psi
(June 17, 2012) Jamie McGehee said:
my new pump worked fine for about a week. Then all at once,my pump is running but pressure wont go above 10psi
Jamie, double check that the gauge 10 psi is really correct - that is, that house pressure is indeed abnormally low - or use a separate external water pressure gauge to check.
Lost air charge in the water tank won't lower the pressure the pump delivers - but it will cause the pump to short cycle on and off too often.
If pressure really is low and the pump is running (probably constantly if power is on to it) then I'd look for a damaged pump, low voltage to the pump, or a well piping leak, or low water in the well that is simply not returning water to the building.
If you shut off the system for a few hours or longer and then the pump is able to develop pressure I suspect the problem is the well flow rate.
(July 4, 2012) Ron said:
My pump waters the yard and sometimes the pump will kick off when a circuit tries to start. I suspect the pressure switch. If I restart the pump the circuit works fine. I have recently replaced the surge tank
Question: no water - help me?
(July 29, 2012) kmj said:
just installed a new system pump water tank and no water help
The best approach I can suggest to your "no water" question is to start with the diagnostics found at
Question: pump won't kick on and breakers trip
(Aug 23, 2012) CSW said:
I have a 2HP Franklin Electric Control Box. The pump works and fills my tank to 40+psi, but will not kick on when the pressure drops. Both the main and overload protectors are tripped, I reset them, and the pump kicks on. Is it the Square D Pressure Switch, something in the control box, or both?
(Oct 1, 2012) Anonymous said:
I have replaced my pressure switch 4 tmes in the last 30 days. This just started happening. So, I replaced my pump. But again, the switch just blew out again. Something is burning up the contacts in my switch, causing it to quit working. What is the problem
Sounds like a seized pump motor or wiring short that's tripping the breaker. This can also occur if the well has run out of water or the well screen is clogged, causing the motor to overheat or causing damage to the pump impeller or bearings.
(Sept 7, 2012) Jay said:
I have a private well with pump in the ground about 180'. Recently, the pressure switch will shut off when we use two or more water sources ( hose, sink, shower etc ) and I have to reset it by lifting the manual over ride lever on the side of the pressure switch slightly until pump kicks back on. If we only use sink or shower, we are good. We have normal pressure when it is working and do not have low pressure at any time. It just shuts down completely. Circuit breaker does not trip. We replaced the grey control box on the wall next to the pressure tank and have also pulled the pump to make sure it was working properly. Tapping on the pressure tank gives me hollow sound at top half and solid near bottom which leads me to believe it is not logged. Tank pressure is about 29 lbs.
My question is why the pressure switch keeps shutting down and needs to be manually turned back on. It was replaced with a new one but problem continues.
We have always had good water pressure in the past and were able to use several faucets or hoses at one time. Not sure what happened. Now if we use outside hose and kitchen sink, it will shut down within a minute or so, sometimes almost immediately.
Any help would be appreciated.
(Feb 12, 2014) Janee said:
Ours is pretty much the same as Jay's question below! We have a Square D 9013FSG2M4 20/40 Switch to replace the previous which was bouncing (burned contacts), to accommodate about a 32gal. water tank. Now the VERY new replacement will never Cut In (engage) on like it's supposed to after dropping in pressure. We even replaced the gauge itself just today with new one, and tried adjusting the deferential small/large pressure nuts in back. Still the switch will not Cut In (engage) unless we turn the Override Lever up.
However, at times even then it wants to kick almost immediately into Cut Off. So again, we made some adjustments. Where at first it kept shutting off at like 38psi, then lowered after some fiddling, to about 43psi. We are still trying to figure out how to get the thing to Cut In after the pressure gets to a certain point, say like when taking a shower, so the water doesn't keep cutting off.
Do you have any suggestions as to what we are doing wrong, how to adjust to stop this from happening? We appreciate this greatly! Thank you
thought I typed 33psi. Didn't mean to have 43psi typed in!
Is it possible that the switch is mounted on a small 1/8" pipe nipple or that it's sensor receives water pressure through a small diameter tube?
If the sensor port on the switch doesn't feel the water pressure correctly that can cause the trouble you describe. Or, of course it may be another issue
The way it's set right now (this new switch), it shouldn't run because it's settings (the Large spring adjustment) and the differential are completely different on the old switch compared to this new one! The differential on the old switch seems set lower (nut-wise), and a little more-so lower on the large spring, all compared to the new switch we recently bought to replace.
Not to mention this place we live in, we may as well live in another dimension since whoever built it, did so bassackwards, lol!
(Feb 12, 2014) Janee said:
Also, regarding what you said about clogging, would it be possible for ice in the pipes to cause this? It has been really cold outside, and a few times we had to use a Torpedo Heater to thaw some of them out.
P.P.S. Even if water still seems to be flowing through the faucets, and the small pipe beneath the switch, could the possible presence of ice cause this as if it were a clog? We checked to make sure there wasn't any debris and what not. As far as we could tell, everything was clear.
Question: we run out of water
(Oct 8, 2012) Pierre said:
Replaces old water tank from 20 gallons to 30 keeping the same 1/2 HP jet pump and cut/ in cut out pressure. Pressure is higher but now we run out of water when showering or flushing the toilet and doing the dishes. How can we fix this HELP!!!
(Mar 19, 2014) Anonymous said:
Not getting no pressure on gauge to keep pressure switch running
Pierre your well may be one with limited flow rate. See
Anon I'd like to help but don't understand the question. If you mean that the pressure switch is not responding to changes in water pressure then perhaps the switch mounting tube or bottom sensor port are debris clogged. If that's the case replace those parts.
Question: ok to re-use old wiring when installing a new well pump control?
(Feb 4, 2014) ardena said:
this female thanks you for all the info you have give everyone. I bought a new pressure switch and gauge .Is it safe to use the same wiring from the old one? I enjoy doing things that challenge me. Thanks again
WATCH OUT for getting electrocuted working on electrical wiring - make sure and confirm by test that power is off before you touch anything. A mistake can shock you, kill you, or burn the house down. I'd make that warning to anybody.
That scary message out of the way, if electrical wiring to a water pump control switch is not damaged say by overheating, nicks, cuts in insulation, etc. then normally it is re-used to power the new switch.
Read the instructions that come with the switch, including warnings about wiring safety; also, regardless of whether or not a person is competent or knows how to make electrical wiring connections, note that in some jurisdictions that work is by local code something required to be done by a licensed electrician, and inspected by the electrical inspector. This is being a bit fussy I know, but the consequences of a mistake are serious.
Question: addinga pressure tank to lawn sprinkler system
(Mar 21, 2014) Jim said:
Adding a pressure tank and switch to my lawn sprinkler system. The tank and switch will be next to house under the eve. Just a little concern that the switch will be exposed to the rain when it is blowing from that direction. will this be a problem?
Jim, unless all of the wiring, junction boxes, and electrical controls planned for your hook-up are rated for outdoor use and weather exposure your installation will be unsave and risks electrocuting someone. So in my opinion, yes this will be a problem.
Question: water in the well but not in the house
(May 4, 2014) Anonymous said:
I have water at my well but not at my house ant he pressure gage will not rise? Any help out there? Walter
Anon, please see the diagnostic suggestions at NO WATER PRESSURE and let me know if questions remain.
Walter if you've checked the
article in the More Reading Links above and are still stuck, try replacing the pressure switch. That is, if your pump is working and has power the switch could be debris clogged.
Question: buy separate contact points to replace in well pressure control switch
(18 hours ago) Jeff said:
Greetings, is the Well Pump Switch Contacts sold separately?
Jeff, the standard repair is to replace the pressure control switch. I wouldn't try replacing just the contacts, nor does the manufacturer recommend sanding or filing burned contact points. The loss of plating means the ground off surface won't last long.
Question: water pump cycles on and off at cut-out pressure
(June 23, 2014) Normand said:
Jet pump works fine but when I started it up this year is does something that it did not do previously.
When [the water pump] reaches the max pressure and shuts off, it starts again for 4-5 seconds the shuts off. Why does it go on and then off a second time once it reaches the max pressure?
Possibly burned contacts, debris clogging a sensor port on the switch, water running in the building, or something else I've not thought-of.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Water Supply & Drain Piping, Wells, Pumps, Water Supply Equipment