How to Interpret & Act On Drinking Water Test Results
How to remove water contaminants indicated by a water test
WATER TEST INTERPRETATION - CONTENTS: How to interpret water test results - types of water quality & purity tests & what they mean; What to do if your water fails a water test, when to re-test, detecting cheating on water tests; When and how to shock or chlorinate or sterilize a water well; How to get rid of odors in drinking water; How to treat water for hardness, minerals, odors; How to treat water that is contaminated: choices of types of water treatment equipment
POST a QUESTION or READ FAQs about how to understand the meaning of water potability test reports & what actions to take based on water test results
Common Water Contamination Tests for Bacteria Levels - Identifying Unsanitary Drinking Water
This series of articles explains many common water contamination tests for bacteria and other contaminants in water samples. We describe what to do about contaminated water, listing common corrective measures when water test results are
We include water testing and water correction measures warnings for home owners and especially for home buyers when certain conditions are encountered, with advice about what to do when these circumstances are encountered.
Various treatment methods for contaminated water are reviewed and the pros and cons of each are discussed.
Emergency drinking water needed? Basic water purification procedures that can be used in an emergency such as after a hurricane, flood, or earthquake are described
at DRINKING WATER - EMERGENCY PURIFICATION and
If community or private wells are back in operating and providing water, do not assume that the water is sanitary and ok to drink until responsible authorities have said so. Even then, local water pipes in a building may be unsanitary and additional cleaning or disinfection may be needed.
This document combines information from various sources including from the Dutchess County NY health department, from Smith
Laboratory in Hyde Park NY (914-229-6536), water test developer/suppliers, and other independent sources. Pending review corrections by these sources, the author is responsible for the content which includes
opinion and advice based on more than 40 years experience in the field.
Because water quality can have major effect on personal health, home owners and home buyers, & ASHI home inspectors should consult with their local health department before performing tests or taking corrective actions regarding water quality.
PA - Coliform Bacteria Test for Contamination in Water: Presence/Absence Test
This standard water test required by many banks, involves pouring use of a chemical Defined Substrate Technology (DST) reagent which produces a color change (or another signal, i.e. fluorescence), both indicating
and confirming the presence of total coliform and E. Coli in a sample of drinking water. The test indicates either the presence or absence of this bacteria.
This test, used by most water test companies for real estate transactions does not produce a bacteria colony count. We order this procedure, or the lab will elect this procedure when the water sample is turbid (contains sediment or
other material which precludes alternative test procedures).
The test is sensitive and specific for the detection of total coliform and E. coli at 1
CFU/100mL of sample in water samples with as many as 20,000 heterotrophic bacteria present per ml. This means that this test for coliform bacteria is not obscured by the presence of other bacteria in the water.
P/A Test results: if the test did not find an indication of a coliform bacteria problem the result will say "Less than 1" or if the lab reports carelessly, "Zero".
Accurate lab test reporting would be to say "below the limits of detection" of a given test, and then to specify the
limits of detection used. The acceptable level of bacteria in water varies by jurisdiction. For example in some Canadian provinces a higher level of 10 CFU/100mL is permitted. These very slightly higher numbers are allowed because the opinion of health experts is that there is no measurable risk at those levels.
M.F.T. - Coliform Bacteria Test for Contamination in Water: Membrane Filter Technique
This standard water "test" required by many banks, involves pouring 100 ml of water through a membrane filter. The bacteria present in the water are trapped on the surface of the filter. After an incubation period of 24
hours the coliform colonies present are counted. The count may not exceed 0 per 100 ml according to recently updated New York State Drinking Water Regulations. (MFT=Multiple tube Fermentation Test.)
MFT Test results: If the lab finds apparent unacceptable results with this general test for the presence of any bacteria, the revised NY State procedure requires the lab to measure for E-coli, by performing the MPN procedure as follow up.
This is because the presence of non-coliform bacteria present in the water can obscure the test and prevent counting E-coli. The NY State Sanitary Code has no
standard for total bacteria count in water supply. The need to go to an MPN test often explains additional delay of up to a week beyond usual time for obtaining water test results.
MPN - Coliform Bacteria Test for Contamination in Water: MPN testing
This test is used when the water cannot be filtered due to turbidity, high iron, large amounts of sediment, or high non-coliform bacteria count. This test involves incubation of measured volumes of sample in liquid nutrients which favor the growth of any coliform bacteria present. This is a statistical method
of testing based on the number of positive tubes of media after 48 hours of incubation and 48 additional hours of confirmation.
MPN Test results: As of modified NY State procedures starting in 1991 a count of 0 indicates no coliform and water of satisfactory quality. (MPN=MilliPore Nutrient test.)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Questions & answers or comments about how to understand the meaning of water potability test reports & what actions to take based on water test results.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Smart Tank, Installation Instructions [ copy on file as /water/Smart_Tank_Flexcon.pdf ] - , Flexcon Industries, 300 Pond St., Randolph MA 02368, www.flexconind.com, Tel: 800-527-0030 - web search 07/24/2010, original source: http://www.flexconind.com/pdf/st_install.pdf
Typical Shallow Well One Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect_Jet_Pumps_1.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Typical Deep Well Two Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Water Fact Sheet #3, Using Low-Yielding Wells [ copy on file as /water/Low_Yield_Wells_Penn_State.pdf ] - , Penn State College of Agricultural Sciences, Cooperative Extension, School of Forest Resources, web search 07/24/2010, original source: http://pubs.cas.psu.edu/FreePubs/pdfs/XH0002.pdf
Water Tests & Fees this water test fee schedule applies when testing is combined with other onsite building inspection services. Inspectors may charge differently if hired just to perform water testing.
Handbook of Disinfectants and Antiseptics, Joseph M. Ascenzi (Editor), CRC, 1995, ISBN-10: 0824795245 ISBN-13: 978-0824795245 "The evaluation of chemical germicides predates the golden age of microbiology..." -
This well-focused, up-to-date reference details the current medical uses of antiseptics and disinfectants -- particularly in the control of hospital-acquired infections -- presenting methods for evaluating products to obtain regulatory approval and examining chemical, physical, and microbiological properties as well as the toxicology of the most widely used commercial chemicals.
Principles and Practice of Disinfection, Preservation and Sterilization (Hardcover)
by A. D. Russell (Editor), W. B. Hugo (Editor), G. A. J. Ayliffe (Editor), Blackwell Science, 2004. ISBN-10: 1405101997, ISBN-13: 978-1405101998.
"This superb book is the best of its kind available and one that will undoubtedly be useful, if not essential, to workers in a variety of industries. Thirty-one distinguished specialists deal comprehensively with the subject matter indicated by the title ... The book is produced with care, is very readable with useful selected references at the end of each chapter and an excellent index. It is an essential source book for everyone interested in this field. For pharmacy undergraduates, it will complement the excellent text on pharmaceutical microbiology by two of the present editors."
The Pharmaceutical Journal: "This is an excellent book. It deals comprehensively and authoritatively with its subject with contributions from 31 distinguished specialists. There is a great deal to interest all those involved in hospital infection ... This book is exceptionally well laid out. There are well chosen references for each chapter and an excellent index. It is highly recommended." The Journal of Hospital Infection.: "The editors and authors must be congratulated for this excellent treatise on nonantibiotic antimicrobial measures in hospitals and industry ... The publication is highly recommended to hospital and research personnel, especially to clinical microbiologists, infection-control and environmental-safety specialists, pharmacists, and dieticians."
New England Journal of Medicine: City Hospital, Birmingham, UK. Covers the many methods of the elimination or prevention of microbial growth. Provides an historical overview, descriptions of the types of antimicrobial agents, factors affecting efficacy, evaluation methods, and types of resistance. Features sterilization methods, and more. Previous edition: c1999. DNLM: Sterilization--methods.
When Technology Fails, Matthew Stein, Chelsea Green Publisher, 2008,493 pages. ISBN-10: 1933392452 ISBN-13: 978-1933392455, "... how to find and sterilize water in the face of utility failure, as well as practical information for dealing with water-quality issues even when the public tap water is still flowing". Mr. Stein's website is www.whentechfails.com/