Water tank diagnostic FAQs:
this article provides answers to frequently-asked questions about how to diagnose problems with the water pump or tank supplying building water pressure & flow.
These questions help sort out the causes of water pressure problems and help determine if the problem appears to be at the water pump, water pressure tank, water piping, or water source such as a private well or water storage tank.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Well Tank Problems, Trouble With Water Pressure Following Water Pressure Tank Replacement or Relocation, etc.
[Click to enlarge any image]
Question: my water system has a pump but no pressure tank, now my pump is losing pressure ...
I don't have a tank so the water comes out by the pump so the pump runs the entire time I use my sprinkers. The pump runs but doesn't seem to run as high as it usually sounds so my water doesn't keep coming out. Do I need a new pump? I replaced it 4 years ago. - Debbie 4/16/12
Debbie, if you run a well pump with no pressure tank to make the pump's life easier, you have to expect a reduced pump life. Your pump may have a worn internal bushing, damaged impeller, or a similar mechanical part damaged. SPECULATING, I could imagine also that the rapid on-off cycling of the pump (that's what typically happens if you run a pump on a water system with no pressure tank) might have even burned electrical contacts on a switch. Normally I'd expect the switch to just top working, but maybe instead you're seeing increased resistance and/or low voltage in the system.
Question: We relocated our water pressure tank and now can't get any water - what's wrong?
We moved our fresh water tank at the cabin from our driveway above the cabin to under the cabin. The pump has always been located under the cabin. Now the tank sits a few feet below pump level and we cannot get water to the cabin. The tank water level is slightly below the pump. - Pat
Reply: Provided the water pressure tank is not too high above your jet pump the problem is not moving the tank it's more likely a plumbing mistake or pump/pump control problem.
Pat: even a one line jet pump can lift water about 25 feet. So I suspect your pump needs replacement. If that's not the problem then it's lost prime or there is another issue.
Question: Water pressure at shower drops and water temperature varies just after we replaced our bladderless steel water tank with an internal-bladder model
I just replaced my old style steel cold water tank with a pressurized tank. I have a 40-60 jet pump that worked fine with the old tank. Now, when the I turn on the water at the shower, when the pump gets to 40 psi, the pressure drops way off and the water temperature oscillates between hot and cold. The system did not do this before I put in the pressurized tank. - Mike Barber
Reply: Things to check when water pressure behavior is odd following water tank replacement
Mike, This is an tough water pressure diagnosis question for which I have to guess at some things that are worth investigating further, as I'm not sure exactly what's wrong.
Check the operating pressure cycle of the pump and tank system by running water while watching the pump, tank, and pressure gauge.
Note the gauge pressure at which the pump cuts in and out. Typically the range is 20/40 or 30/50 cut in and cut out.
Assuming your pump pressure control switch is set (factory) to 20/40, if the the pressure gauge reads 40 just when the pump cuts OFF then the pressure, switch, and system look normal - so far. (If you run water too fast at a nearby fixture the pump may never reach its cut-off pressure, in which case once the pump is running then turn off the water running in the house so we can see the cutoff pressure).
Watch out: debris or other problems can lead a water pressure gauge to give inaccurate water pressure readings. Try tapping gently on the gauge if it is not responding to the pump turning on and off, and see WATER PRESSURE GAUGE ACCURACY for details.
If the pump cuts off at 40 as above and the gauge reads 40, you should have a fully pressurized water pressure tank with a normal dose of water in the tank. You can confirm this in part by gently rocking the water tank - it should be heavy and not move easily. Don't push around so much as to move pipes and start a leak.
Now turn ono water at the shower. If you do NOT have good water pressure and flow, then I suspect that there is a blockage somewhere in the system. Check pressure and flow at other fixtures. If ALL plumbing fixtures have poor flow, then the blockage is at or close to the water pressure tank.
Some pressure tank bladders can sometimes stick or collapse or tear, interfering with water pressure leaving the tank. Under the conditions above, if the pressure in the house is poor at pump cut off I suspect that may be the problem and some tank diagnosis, a tank installation problem, or a tank bladder defect are worth pursuing. A Minnesota plumber told me they sometimes free up a stuck tank bladder by briefly holding the pressure switch down to force tank pressure 10-20 psi above normal
Watch out: excessive water tank pressure beyond its design pressure can burst the tank and injure someone. This is particularly true if no one installed the necessary pressure relief valve at the water pressure tank. See WATER TANK RELIEF VALVE
If the water pressure drop is just at the shower I suspect debris blocking at the shower head or piping.
The fluctuating "hot and cold" temperature is another important clue to consider.To me that suggests that cold water flow in the whole system has at that point become intermittent but not through the entire system.
By that I mean if pressure leavinvg the water tank were itnermittent then because cold water is flowing BOTH to the hot water tank (where it pushes hot water out to the plumbing fixture) AND to the cold water deliver lines in the home, THEN both hot and cold pressure would fluctuate together (I'd think), so the water pressure would vary at the shower but the temp would vary less as hot and cold are both flowing through the whole system at same rate.
The implication of the case you describe (temperature varies significantly at the shower) implies to me that cold water is being blocked somewhere else than right at the water tank - because you're seeing more cold flow blockage than hot flow blockage.
Another reader found a solution to this problem at a debris block in a piping elbow in a cold water line.
Finally, if your pump pressure control switch is not behaving properly, say not turning on the pump at the CUT IN when it should, I suspect that there may be debris blocking at the pressure control switch. Sometimes changing out a water pressure tank can stir up debris in the whole water supply system, exacerbating a problem with the pump pressure control switch or piping.
This problem is more likely if the water supply suffers from clay or silt or other debris or if the building piping includes rusty iron pipes. A solution is to check and perhaps replace both the pressure control switch and the small diameter pipe nipple that mounts the switch body to the building water piping or pressure tank.
Please look into these possibilities and let me know what you're finding - what you learn will help other readers. And I'll think about and research this question further and add what else I can come up with.
Reader Follow-up from Michael Barber
I finally have gotten the time to get back to my water pressure problem. I replaced the old style steel tank with a "bladder" tank.
My pump is a 40/60. I opened the drain line (I added this to the main cold water line going into the house so I could run the water from under the house where the pump and water tank are) and have set the pump pressure switch so that it shuts off at precisely 60 psi and starts at 40 psi.
With the water line open the pump turns on right at 40 psi, then the pressure drops rapidly to about 20 psi and then slowly drops to between 8 and 12 psi where it stays until I close the water line. I set the tank pressure at 38 psi with the pump off after having drained the line.
When I use the shower, or any other faucet for that mater, the pressure is great for the first 3 to 3.5 mins but then drops off significantly and only partially returns to full pressure (consistent with what I see on the gauge under the house).
The problem I am having is that the water pressure did not act like this prior to replacing the tank.
Is this normal for these types of tanks? If so, should I just have my old tank welded up a reinstall it? I posted this on the site a few days ago but haven't had a response. At least that I could find. Thanks, - mike barber
Thank you for the added details. Below I offer some diagnostic suggestions and comments:
Steady state water pressure at maximum flow rate:
It is normal for the water system pressure to remain at a much lower number (8-12 psi in your case) than the pump pressure control switch cut-off number (60 psi) when you are running a faucet and pipe wide open; The pressure you are seeing is the steady-state water pressure that the pump is capable of delivering continuously - a function of the pump horsepower, total lift, pipe lengths, diameter, bends, and other obstructions.
Steady state water pressure at single fixture flow rate:
When you do not have any other plumbing faucet wide open but are running a single fixture such as a shower or sink, and when you report good pressure for the first three minutes, most likely that pressure is being delivered by the water pressure tank that is starting at 60 psi and falls to 40 psi when the pump then turns on.
After that point we have exhausted the stored energy/pressure in the water pressure tank. Thence the water pressure we see in the system is strictly the pressure capability of the pump and piping properties I outlined just above.
Improving steady state water flow rate & pressure:
When the single fixture (or for that matter even multiple fixture) water flow rate is inadequate there are some things to check to fix the trouble. If the poor water system steady state flow rate/pressure has been present since installation or for a long time or developed slowly over months or years, we suspect limitations due to
see WATER PRESSURE PROBLEM DIAGNOSIS TABLE linked-to in the article above for a more complete list of diagnostic suggestions
When a poor water flow rate and pressure problem has developed suddenly we suspect:
Keep in touch - what you find will help other readers. - Daniel
Question: we have a driven point well with a pump that won't stop running until I turn off the water
I live in a mobile home with a point well system (2"). Today the pump kept running while I was sprinkling the garden. It did shut off when I turned the water off. Usually it cycles on & off while the water is running. Any suggestions? - Sharon 8/31/ 12
When the well pump stops running when you turn off the water, then the problem is not likely to be the pressure switch, and more likely is instead a problem with the ability of the pump to deliver water fast enough for your usage rate. Since the pump used to be able to "get ahead of" your water demand when the only thing you were doing was running a garden sprinkler, here are some things to check:
Question: Submersible well pump giving a big drop off in pressure, recovers only briefly, good pressure at the water filter cleanout valve
I have an in well pump, and what I'm getting is a big drop off of pressure in the house. It recovers after a while but does not last long ( bout a minute)then its just a trickle. I get good consistant pressure on the filter clean out valve but not in the house. When water is running in the house, the pump cuts on & off while water is running but never the pressure it should.. Any ideas would be appreciated - Rob 9/4/12
Rob it sounds as if your water filter may be clogged. Or the valve that temporarily bypasses or shuts off the water filter (to allow service) may be damaged, shut, improperly set. Also check for a waterlogged pressure tank - lost air charge.
Question: water pressure cycles between strong and weak; can it be the pressure tank?
i have a ground pump and of late i've noticed my toliets when flushed make a fill pause fill pause fill sound. Today i showered and could fill the water pressure strong and weak, then go strong again?
Can you tell me if it is the pressure tank under my house or the under ground water pump, which i replaced the wiring to the pump with the pipes. We do not know how old the pump or pressure tanke are. This house is at least 18 years old. any comments or suggestions would be greatly appreciated. How do i know when i need a new pump? It is a 3 ft wide, 80 ft. deep well? Please any comment would be greatly appreciated. Thank you so much a concerned mother of 2 youngions :) sk - Suzette Kerr 9/13/12
Suzette, it sounds like a waterlogged water pressure tank.
The pressure sensor on my water pump has a rubber cap. There is a little drip from the small tip which accumulates in the rubber cap. Now I am loosing water pressure to 10 instead of the usual 30-50. I removed the rubber cap and re-seated it with return of the pressure but I am sure this is not a permanent fix as the leak is still there. What do I do now?? - Sandra 9/25/12
Tell me the brand and model of switch so that we can review the manufacturers specs, and send me a photo of the drip problem el that I better understand where water is coming from.
Question: Issues with well water system: noisy pump, humming, pump keeps running;
Over the last few days I have had a few issues with our well after system.
Contacts looked loose so I replaced the switch and checked the pressures again. Noise at the at switch and gauge area where the pump line comes in is still there but not through the whole house. Pressure is 40 cut in 55out. I wanted to adjust the out up to 60psi but noticed the spring had no pressure on it. I drained the system and checked the tank static charge pressure and it was very low. Went and bought a little air pump and charged to about 38psi. Checked operation and it functions well but noticed the pressure cut out is still 55, (played with cut out and still 55) and pressure drops off fast.
At this point I am still suspecting the check valve but I don't see it by the switch, I thought I would see an obvious fitting that has a direction arrow or something to denote a check valve.... Maybe on pump? So either pump or check valve with pump running all the time and not reaching 60 psi?
Maybe I could lower the cut in pressure and that would lower the cut out min pressure too?
Question: water pump kicks on immediately every time we turn on the water
pump kicks on every time you turn water on? - Debra 10/2/2012
We have replaced the pump switch recently, and the problem is getting worse if two things are running at the same time (i.e. toilet flush and washing machine) the pump(?) won't catch (when it hits the certain spot it's supposed to) and we have to manually go downstairs and reset it to get the water going again. What is the problem?? Please help before this problem gets worse!!!
Question: Water pressure stopped for 20 seconds at a time - problem traced to iron-clogged pressure switch; is this a water quality issue or a wear and tear issue?
We had an issue with water pressure ( water would stop flowing for 20 sec at a time) in a house we are renting. The owner called the local well drilling co. They replaced the pressure switch which was clogged with iron. Is this a wear and tear issue or a water quality issue or something else. - Sue Sue460@ptd.net - 9/7/2012
Sue, thanks for the important question - it gives us a chance to clarify the problem with debris clogging at well pump pressure control switches and pressure gauges.
Continue reading at WATER TANK REPAIRS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: loss of water pressure after a power failure
(June 20, 2014) Bill said:
Oover the last two weeks we have noticed it the washing machine, dish washer, is running or if a toilet is filling, there is very little pressure any where else in the house, until the pump kicks on. In the last two weeks I have replaced the pressure switch and the pressure tank with no improvement....T well seems to be operating as it should...watching the guage it kicks on right at 40lbs and kicks off at 62lbs, just as it should..then you can watck the pressure gauge slowly decline and the pump kicks on st 40...It takes less than a minute for the pump to fill the tank...yet we still have the same pressure loss in the house...I have removed all th piping from where the plastic pipe from the well to the tank cleaned and replaced it all...there was less sediment in the piping than expected....I don't know what to do next?
Bill do you thins there could be a probled with debris clogging of a filter ?
Following that check for loss of prime.
Following that check for lightning damage to the well pump, wiring, casing, piping.
Question: pressure tank fails to fill
(Aug 30, 2014) pressure tank fails to fill said:
Check for a collapsed or damaged tank bladder or debris at the tank inlet.
(Sept 8, 2014) Brian said:
(Oct 6, 2014) Elizabeth said:
Most likely there is a leaky foot valve or check valve that allows loss of water in the pump and piping. Before you shut off the pump when the leak dropped water pressure in your system the pump came on and restored it.
After you shut off the pump the leak was able to lose so much water (and pressure) from your system that the pump lost its prime.
DO NOT keep running the pump in these conditions as it can be damaged or ruined if run dry.
See WATER PUMP PRIMING PROCEDURE in the More Reading links above on how to prime the pump to get water back.
But a proper repair will be to find and fix the leaky foot valve, check valve, piping or other leak that causes the trouble.
Question: small black specs in the water supply
(Nov 12, 2014) Susan said:
Susan one would think that since the pressure tank feeds both hot and cold building water piping systems the black specks would show up in both hot and cold water. Perhaps you've got corroding piping?
Question: Century jet pump not working, burning electric smell
(Nov 28, 2014) William said:
William it sounds as if the pump motor is not able to start - could be a failed motor, jammed impeller, or bad start-run capacitor.
At More Reading above you'll see more pump diagnostic articles beginning with WATER PUMP REPAIR GUIDE - home
Question: waterlogged pressure tank, now debris in the water
(Dec 20, 2014) u1024274 said:
(Dec 21, 2014) DanJoeFriedman (mod) said:
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References