Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER CONSERVATION MEASURES
WATER CONTAMINANT LEVELS
WATER FILTERS, HOME USE
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PUMP REPAIR GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMP SHORT CYCLING
WATER SOFTENERS & CONDITIONERS
WATER TANK REPAIR PROCEDURES
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WELL CHLORINATION & DISINFECTION
WELL FLOW RATE
WELL WATER PRESSURE DIAGNOSIS
WELL YIELD IMPROVEMENT
WINTERIZE A BUILDING
Well yield, flow, well recovery rate & well water quantity:
Here we define and describe how to measure water well yield, safe well yield, the water delivery rate of a well, or well recovery rate, and we explain how to measure or calculate this critical number. We explain why a well flow rate is actually comprised of multiple flows at various depths, and we describe how those rates are found & tested.
We define the difference between well pumping rate and well recovery rate. We show how to calculate the actual flow rate of a water well, and we point out a critical difference between an instantaneous well flow rate and the well's 24-hour flow rate.
We also explain how & why a water well's flow rate will change over time, and we define the safe yield number for a water well.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
This article series describes how we measure the amount of water available and the water delivery rate ability of various types of drinking water sources like wells, cisterns, dug wells, drilled wells, artesian wells and well and water pump equipment. The sketch at page top, courtesy of Carson Dunlop Associates, outlines what happens during a well drawdown test or well flow test procedure.
To determine the well yield we need to know how much water flows into the well from surrounding rock or soil in a given amount of time. In a simple example given here, we start with a dry empty well (it was just pumped dry), we wait a known period of time, and then we measure the depth of water that appears in the well.
That's all we need to calculate the STATIC HEAD of Water in the Well and then the actual well yield (explained in this article).
In a companion article, WELL FLOW TEST PROCEDURE, we describe both valid and questionable ways people measure well yield, and we offer some simple steps any home owner or home buyer can take to check the adequacy of water pressure and water quantity at a building.
Well Recovery Rate is the rate at which water runs into the well from the rock fissures and openings into the lower portion of the well below the steel casing, while we're pumping water out of the well.
Some other terms for well recovery rate include well yield, well flow rate, and well water quantity.
Since the "recovery rate" of a well describes the rate at which water runs into the well, a well recovery rate also defines the rate at which water can be pumped out of a well without pumping the well down so far that the pump "runs dry".
Typical numbers for well recovery rates (if measured honestly over a 24-hour period) run from a fraction of a gallon per minute (a terribly poor well recovery or flow rate) to 3 gallons a minute of water flow (not great but useable) to 5 gallons per minute (just fine for residential use) to more than 10 gpm (a great well recovery rate for residential use).
Water flow rates into a well & inflowing water quality vary at different well depths: using Drill Stem Testing
A drilled well, especially a deep well, often passes through more than one aquifer level in the earth. As geological conditions and rock properties vary at these various depths, and as the properties of aquifers themselves will vary, the total flow rate of a water well is the sum of all of the individual flow rates through which the drilled well opening (below the bottom of the well casing) pass.
Drill Stem Testing (DST) described by AGE Developments in Australia describes well stimulation and well testing. 
Drill stem testing allows the well driller to identify and evaluate the multiple aquifers through which a well may have been drilled.
A submersible well pump (an electric submersible pump or an airlift submersible pump unit) and piping system that includes two inflatable seals is lowered into the well to a desired test depth. By inflating seals above and below the pump itself, when the pump is operated, it draws only water flowing into the well casing in the depth between the upper and lower well casing seal.
Drill stem testing is thus able to isolate and test the water flow rate within each different well segment (at different depths) of the well in order to diagnose and evaluate the overall well flow rate as well as to target areas for hydro-fracturing.
DST also permits identification of undesirable water flow into a well at certain depths. For example if one aquifer provides water high in contaminants (sulphur for example) that aquifer can be isolated and sealed, to exclude water from that aquifer when the water well is put into use.
The well flow rate or recovery rate is not equal to the well pumping rate: that is, most water pumps can pump water out of a well faster than water runs in unless the well has a great recovery rate. For wells with modest recovery rates of say 2-3 gpm, some well installers or plumbers design the pump so that it cannot pump faster than this rate, thus avoiding pumping the well dry and possibly damaging the water pump itself.
The well pumping rate is limited by the horsepower of the well pump, pump type, pump location, and other factors. The maximum well pumping rate set by the pump is normally a number stamped on the data tag attached to the well pump itself. The well pumping rate defines how fast in gallons per minute (GPM) the pump can deliver water if it has an infinite quantity available.
The well flow rate, as we discuss in this article, is the rate that water flows into the well itself from the surrounding soils. The well flow rate is the true limit on a well's ability to deliver a sustained water flow to its users.
So you could pump water out of a well very fast pumping rate, say at 10 or even 15 gpm. But if the well recovery rate is less than the well pumping rate, you're going to run out of water. How soon you run out of water depends on how much water was in the well casing when you started pumping (the static head), and ultimately on the well recovery rate. We explain this in more detail at definition of the WELL QUANTITY TOTAL.
We offer a more detailed (and more confusing) equation used to calculate the details of a well recovery rate in our discussion at Drilled Wells - steel casings. But it's easier to simply pull water out of a well at a given rate and see how long we can do so. That's about what a well driller does to determine the effective well flow rate when a new well is drilled.
Pulling water out of the well (using a variable-rate pump running at a rate set by the well test professional) integrates all of the different rock fissure flow rates into a single quantity of water.
The following example of calculating a well flow rate uses well data from a dug well described in detail at Hand Dug Well Procedure.
Question: I'm digging a well, not yet in the driest part of our dry season. I'm at about 10 meters depth, well diameter about 1.4 meters. At 4 pm when the digger stops for the day (by hand hammering through rock with a mallet and chisel), he drains the water. At 9 am the next day the well has 1.6 meters of water in it. I intend to complete digging further into the dry season.
However, based on the above data, how many liters of water can the well produce in a 24 hour period? -- A. Starkman, Oaxaca, Mexico. [Note that this is a hand dug well - see Hand Dug Wells for more about that type of water source. But the calculations of well flow rate are the same for any round drilled well or hand dug well.]
Answer: We can calculate the well flow rate from the reader's example above, using the formula for the volume of a cylinder and a constant to convert between volume of well water in cubic meters and liters or gallons.
This well water flow rate calculation case provides exactly what we need to calculate the quantity of water in a well from direct measurements of the well diameter, depth, and water depth, presuming that the well, a dug well in this case, is round. We just need the depth of water and the diameter of the cylinder formed by the well.
Then we use the formula for volume of a cylinder - which in turn means we calculate the area of the circle formed by the bottom of the well (or the well's cross-sectional area) and we just multiply that area by the height (or depth) of the water.
WELL FLOW TEST PROCEDURE describes how we test well flow rate and quantity when the well is already built, is covered or sealed, and we can't conveniently make well diameter and water depth measurements.
So for this real-life example of a dug well for which we want to calculate the well water volume and the well flow rate:
Well Diameter D = 1.4 Meters
The formula to calculate the volume of water in a cylinder is
Volumecylinder = pi x r2 x h
where pi = 3.1416,
Area of a circle = pi x radius squared (radius = 1/2 of the diameter)
For our dug well example under discussion, our diameter is 1.4m so the radius is .7m.
Volumecylinder = 3.1416 x .72 x 1.6
Volumecylinder = 2.46 cubic meters - that's the volume of water found in the well after the overnight waiting period.
Notice that we're being sure to use the same units of measurement for both diameter (or radius) and depth - in this case, we are working in meters.
How to Convert Cubic Meters to Liters or Gallons - Other Common Measures of Water Volume
Convert Cubic Meters of Water in the Well to Liters
Liters: one cubic meter contains 1000 liters.
So for our example well, the well cylinder of water contains (2.46 x 1000) = 2460 liters of water
Convert Liters of Water to Gallons of Water
Gallons: 1 gallon contains 3.7854 Liters
So we can divide the liters, above, by 3.7854 to convert water volume in liters to water volume in gallons.
The example well water volume contains (2460 / 3.7854) = 650 gallons of water.
How to Compute Well Flow Rate in Gallons per Hour
Now we can also obtain the well flow rate - the rate at which water is flowing in to the well - though this will change seasonally as well as change if the well is dug further or other steps are taken that affect well yield.
At the time of our reader's observations, from 4PM on a given day to 9AM the next day (that's a total of 17 hours on the clock) the new well collected 650 gallons of water.
Well Flow Rate = gph
The Well Flow Rate for a water well of any type is normally expressed in gallons per hour or gph that water enters the well from surrounding soils. We calculate a well's flow rate measured in gph by dividing the quantity of water in the well (we calculated that just above, right?) by the number of hours it took for that water to enter the well.
Well Flow Rate = Gallons / Hours - or gph, gallons per hour or water flow rate into the well, provided that no one is taking water out of the well during this same interval.
Our reader made it easy by telling us that the well was pumped dry at 4PM. He measured the water depth and well diameter and kept track of how much time had passed (17 hours).
From our well volume formulas above we know that starting with zero water, after 17 hours the well contained 650 gallons of water.
For this example, 650gallons / 17hours = 38 gallons per hour - this is the well flow rate for a 17 hour period for this particular well.
The most common measure of a well's ability to deliver water, that is the answer to "how much water can we get out of a well" is the measurement or calculation of the well flow rate per minute - the water flow rate into the well expressed in gallons of inflow per minute. gpm.
In our example above, 38 gallons an hour might look like a huge flow rate, by the way, but it's not when we convert the flow rate in gallons per hour into flow rate in gallons per minute - the standard unit of measure of well yield.
The well flow rate in gpm defines the maximum rate at which water can be drawn out of the well over a sustained period. Actually we can temporarily draw water out of a well faster than the gpm flow rate, because the well pump has available to it the reservoir of water already in the well when it starts pumping - the well's "static head". But once that static head of water has been exhausted, gpm is the absolute limit of further water delivery rate possible.
For our well flow rate calculation example above, we found that this well had a water in-flow rate of 38 gph or 38 gallons per hour.
Gallons per hour (gph) divided by 60 (the number of minutes in an hour) = well flow rate per minute in gpm.
Well Flow Rategpm = Well Flow Rategph / 60
For our dug well example, 38 gph / 60 = 0.63 gpm - this is the measured well flow rate in gallons per minute.
In this case that's a weak, marginal well flow rate - just over half a gallon per minute. In the U.S. most building or health departments who must approve a private well water supply when issuing a final certificate of occupancy for new construction want to see 3 to 5 gallons per minute or 3-5 gpm.
Watch out: if you install a pump whose pumping rate exceeds the well yield or flow rate (see WELL YIELD DEFINITION), the pump may run dry and be damaged. The risk of pump damage is greater in a well that has a small static head (see Static Head of Water in the Well) or in conditions under which the pump is left running for long periods so that the static head is likely to be exhausted. If you have this risk or this problem on a well, see the advice on protecting pumps given
Is This Really the 24-hour Well Flow Rate?
Is 38 gph or 0.63 gpm really the true well flow rate? Maybe. Maybe not.
The property owner's observation was that from "an empty well" at 4 PM on a given day, the well water level rises to 1.6 meters of depth by 9AM the following day.
So what was observed was a flow rate of 38 gallons per hour over a 17 hour period. Not a 24-hour period. Will the well water level continue to rise past the 17 hour period. Maybe, maybe not.
While a hand dug (or drilled) water well fills as water flows into it, the well water in-flow rate will slow down and eventually stop. This is true except for artesian wells. That's because eventually the pressure exerted on the well sides by water in the well equals the pressure of water in rock fissures or passages from which water is trying to enter the well.
When the water pressure exerted on the well sides and bottom by water inside the well itself equals the water pressure exerted by water trying to enter the well, at that point water flow into the well will stop. The well water level won't change much until someone draws water out of the well, thus lowering its in-well water level back down and allowing more water to flow in.
Well flow rates will vary by season, weather conditions, and other factors such as well age and history of usage. The well flow rate may also be affected by the chemistry of the water itself - if water is high in minerals, over time the rock fissures through which water flows into the well become mineral clogged and the well flow rate may diminish.
How to Determine the True 24-hour Well Flow Rate
So the owner will want to either measure the well depth again after 24 hours, repeating our calculation from above with the well depth measured at the end of 24 hours, with water only flowing into the well, that is, no one draws any water out of the well during that period.
We prefer to simply measure the water in the well at the end of 24 hours and calculate the 24-hour flow rate. When the well is a drilled well rather than a hand-dug well, the well driller may measure the well flow rate by use of a well pump whose output is adjustable.
The well driller measures the well draw down rate in the well opening while the well pump is running, and compares that to the rate at which the pump is removing water from the well. But a true well flow rate, whether obtained by simple observation or by use of a calibrated pump, should be measured over a 24 hour period, not a shorter interval.
Measure Well Flow Rate After You Determine the Well's Static Head?
Alternatively the owner might want to watch the well water level increase until the water level has stopped rising in the well. It might take longer than 24 hours for the water in flow to stop.
When the water level has stopped rising on its own in the well, the depth of water in the well is measured and is referred to as the static head - the amount of water in the well when the well is fully recovered and at rest.
The flow rate of a drilled well, driven point well, or dug well can certainly change dramatically over time. But other water wells continue to produce water at the same rate for decades. A 27 foot deep well at our office has delivered the same flow rate without change from 1920 to 2010.
When the flow rate of a well varies the underlying causes might include the following:
We define safe well yield as the combination of total water quantity that can be drawn out of a well without dropping the water level in the well low enough to introduce air into the system or damage the well pump.
A well with a large static head and/or a well with a very good flow rate may have a high safe yield while a well with a small static head and the bad luck to also have developed a low well flow rate will have a very small safe yield - in some cases less than 50 gallons of water.
If a poor safe yield is likely to be permanent, solutions include increased water storage capacity in the building, steps to increase the well yield, or installation of a drawdown cutoff device that prevents the pump from dropping water in the well to a level that risks air entry into the piping or damage to the pump.
Watch out: if you install a pump whose pumping rate exceeds the well yield or flow rate , the pump may run dry and be damaged.
The risk of pump damage is greater in a well that has a small static heador in conditions under which the pump is left running for long periods so that the static head is likely to be exhausted.
If you have this risk or this problem on a well, see the advice on protecting pumps given at WELL PIPING TAIL PIECE.
Watch out: Measurements like the well depth (WELL DEPTH, HOW TO MEASURE), well flow rate (WELL FLOW RATE), well recovery rate are all useful, but taken by themselves some of these numbers can give a false reading about the basic question of how much water is in the well? What we really need to know is the total quantity of water that can be drawn from the well and the quality of that water: is it potable, hard (mineral laden), smelly, dirty, requiring treatment for any aesthetic or health-concern contaminant?
At WELL QUANTITY TOTALwe translate these numbers into a more realistic picture of how much water you really can expect to get out of a well.
Reader Question: My well seems to run out of water; the well contractor thinks it's the pressure tank and we don't need to hydro frak the well.
I have a interesting scenario. We have lived in our single family house for a little over 3 years now, we came from municipal water so please bear with my descriptions as we can't seem to wrap our heads around this issue. My first sign of water issue was when I had hooked up a simple garden water hose to a lawn sprinkler (I have no auto irrigation system). I was able to run the sprinkler for about 45mins before I had NO water whatsoever. Long story short, when I had to have my well chlorinated, the well contractor said that should not be the case.
Poor well flow rate, poor recovery rate, poor well yield: while an equipment problem can be involved, you're describing a well with a poor flow rate, poor recovery rate, small static head, small onsite water storage. Hydro-Fracturing is a process that can work to improve well yield, and is sometimes provided with a guarantee of results. (See How to Get More Water From a Well)
Larger water storage tank: If you combine a flow restrictor with a large enough storage tank you can probably defer attempts to improve well yield and live with the low-yield well for some time.
Continue reading at WELL YIELD IMPROVEMENT or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: bore well suffered drastic decrease in water supply
(Mar 6, 2014) mohd iqbal said:
Mohd I think you might want to take a look at our "water pressure loss diagnostics" beginning with the article
as you describe now "hard to see the water" I suspect your well water level has dropped significantly. That can happen for a variety of reasons including nearby drilling, geological changes, blasting, or simply clogging of rock fissures by mineral salts. Or of course the water table may have dropped for other more basic reasons. But usually if the well water level drops dramatically and suddenly, I suspect either nearby drilling, blasting, or water shifts in an area of Karst formations such as Florida in the U.S. where sinkholes open or close overnight. IN other areas of the world (you don't say where you are) we have reported similar geological concerns.
(Mar 15, 2014) Mohd iqbal said:
Mr. Iqbal, the text of the article above discusses how to increase well yield - which can be necessary for a myriad of reasons. You might want to read the related WELL FLOW RATE articles in the list above - which will be more helpful than a speculative guess about a system for which we have no data.
Question: water just stopped running - during a "flow test" conducted by the home inspector.
(May 2, 2014) Anonymous said:
At the top of this article is a link to WELL FLOW TEST PROCEDURE where we describe how well capacity is measured.
But you should start by finding out how much water the inspector ran. Let me know.
Question: relationship between well flow rate and the level of water in the well bore
(July 9, 2014) William said:
Yes the well flow rate into a well does vary in relation to the level of water that is already inside the well bore (or dug well).
We explain the concept of well flow rate in detail at
In sum, water flow into at least deeper wells and even some shallow wells from a variety of water passages, typically rock fissures, that occur at various depths in relation to the well bore. The total well flow rate is the sum of all of these smaller individual flows.
Even more complex, not all of the individual flows into a well flow at the same rate, nor do they necessarily flow continuously at a fixed rate over time. For example
Fissue A may flow at 7 gpm for 20 minutes then diminsh to 2 gpm for a longer or even indefinite interval, while fissure B may flow at 3 gpm foir 12 minutes, then fall to 0.5 gpm for a longer interval.
When the well bore is "full" - that is up to its normal static head top level, water stops flowing into the well bore because the pressure of the water in the bore is sufficient to stop inflow at the various water entry points along its height (I'm using the term "fissures" or water flow passages as usually there is more than one).
An exception are artesian wells whose aquifer feeds into the well bore at sufficient pressure to actually push water out at the well top and even to higher levels.
Question: cleaning the bore screen
(Sept 4, 2014) john blades said:
Pressurized hydrojetting or pull and replace it.
Question: hand dug well went dry
(Nov 10, 2014) Nancy said:
Sometimes deepening a hand dug well increases yield as do probes into the well sides. Watch out for well collapse and finding yourself buried - we don't know how your well is constructed. Check with neighbors or local well diggers or drillers about current position of the water table in general in your area.
Question: troubleshooting shut down pump on a high-yield drilled well
24 Feb 2015 delroy said:
I can't say from just the information in your note. But there are some helpful diagnostics that can get this figured out.
In the More Reading article links just above, please see
WATER PRESSURE DIAGNOSIS, PRIVATE WELL
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References